Description: "Package with generic performance curves"

- Home > Modelica

## Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic

Package with generic performance curves

### Information

This package contains performance curves for the cooling capacity and the EIR of DX cooling coils. For performance data of specific DX cooling coils, see the packages Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed and Buildings.Fluid.HeatExchangers.DXCoils.Data.DoubleSpeed.

The data are described in Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.DXCoil.

Extends from Modelica.Icons.MaterialPropertiesPackage (Icon for package containing property classes).

### Package Content

Name | Description
--- | ---
DXCoil | Performance record for a DX Cooling Coil with one or multiple stages
BaseClasses | Package with base classes for performance data

## Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.DXCoil

Performance record for a DX Cooling Coil with one or multiple stages

### Information

This record declares the performance data for the DX cooling coil model. The performance data are structured as follows:

      nSta      - Number of stages. Set to 1 for single speed coil,
                  2 for dual-speed (or dual stage coils), etc.
      minSpeRat - Minimum speed ratio, used only for variable speed coils.
      sta       - Array of records with one performance curve for each stage,
                  as described below.

Each element of the array `per` has the following data.

      spe       - Rotational speed for the respective stage.
                  (This is only used for variable speed coils to interpolate for
                  intermediate speeds).
      nomVal    - Nominal performance values for the respective stage. Data of the
                  nomVal record are
         Q_flow_nominal - Total rate of cooling at nominal conditions.
         COP_nominal    - Coefficient of performance at nominal conditions.
         SHR_nominal    - Sensible heat ratio at nominal conditions.

         m_flow_nominal - Evaporator air mass flow rate at nominal conditions.
         TEvaIn_nominal    - Evaporator air inlet temperature at nominal conditions.
         TConIn_nominal    - Condenser air inlet temperature at nominal conditions
                             (for evaporative coils, use wet bulb, otherwise use dry bulb
                             temperature).
         phiIn_nominal  - Relative humidity at evaporator inlet at nominal conditions.
         p_nominal      - Atmospheric pressure at nominal conditions.

         tWet           - Time until moisture drips from coil when coil is switched on
         gamma          - Ratio of evaporation heat transfer divided by latent
                          heat transfer at nominal condition.

      per       - Array of records with one performance curve for the respective
                  stage of the coil. That is, the performance curves will be used
                  in conjunction with the nominal values defined in the record spe.
         capFunT  - Coefficients of biquadratic polynomial for cooling capacity
                    as a function of temperature.
         capFunFF - Polynomial coefficients for cooling capacity
                    as a function of the mass flow fraction.
         EIRFunT  - Coefficients of biquadratic polynomial for EIR as a function of temperature.
         EIRFunFF - Polynomial coefficients for EIR
                    as a function of the mass flow fraction.
         TConInRan - Minimum and maximum condenser air inlet temperatures
                     for which the performance curves are valid.
                     Outside this range, they will be linearly extrapolated.
         TEvaInRan - Minimum and maximum evaporator air inlet temperatures
                     for which the performance curves are valid.
                     Outside this range, they will be linearly extrapolated.
         ffRan     - Minimum and maximum air mass flow fraction (relative to m_flow_nominal)
                     for which the performance curves are valid.
                     Outside this range, they will be linearly extrapolated.

The data used to develop the performance curves `capFunT` and `EIRFunT` should represent performance when the cooling coil is wet, i.e., the coil providing sensible cooling and at least some dehumidification. Performance data when the cooling coil is dry (i.e., not providing any dehumidification) should not be included when developing these modifier curves. The DX coil model automatically detects and adjusts for dry coil conditions by evaluating the performance curves for the wet bulb and dry bulb temperatures at the evaporator inlet, and then selecting the corresponding performance. The selection of the corresponding performance is described and implemented in Buildings.Fluid.HeatExchangers.DXCoils.BaseClasses.DryWetSelector.

The parameters `tWet` and `gamma` characterize the amount of moisture that evaporates from the coil surface into the air stream when the coil is wet and switched off. For an examplanation of the parameters, see Buildings.Fluid.HeatExchangers.DXCoils.BaseClasses.Evaporation.

There can be an arbitrary number of polynomial coefficients for the record `capFunFF` and `EIRFunFF`. However, if a coil has multiple stages, then each stage must declare the same amount of polynomial coefficients. For example, if a quadratic function is used for stage one, then stage two must also use a quadratic function.

Extends from Modelica.Icons.Record (Icon for records).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Integer | nSta |  | Number of stages
Real | minSpeRat | 0.2 | Minimum speed ratio
Stage | sta[nSta] |  | Data record for coil performance at each stage
Minimum conditions
MassFlowRate | m_flow_small | 0.0001*sta[1].nomVal.m_flow_... | Small mass flow rate for regularization near zero flow [kg/s]

### Modelica definition

record DXCoil "Performance record for a DX Cooling Coil with one or multiple stages" extends Modelica.Icons.Record; parameter Integer nSta(min=1) "Number of stages"; parameter Real minSpeRat( min=0,max=1)=0.2 "Minimum speed ratio"; final parameter Boolean sinStaOpe = nSta == 1 "The data record is used for single speed operation"; parameter Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.Stage sta[nSta] "Data record for coil performance at each stage"; parameter Modelica.SIunits.MassFlowRate m_flow_small = 0.0001*sta[1].nomVal.m_flow_nominal "Small mass flow rate for regularization near zero flow"; end DXCoil;