Description: "User's Guide"

- Home > Modelica

## Buildings.Fluid.Sensors.UsersGuide

User's Guide

### Information

This package contains models of sensors. There are models with one and with two fluid ports.

#### Selection and parameterization of sensor models

When selecting a sensor model, a distinction needs to be made whether the measured quantity depends on the direction of the flow or not, and whether the sensor output signal is the product of the mass flow rate and a medium property.

Output signals that depend on the flow direction and are not multiplied by the mass flow rate are temperature, relative humidity, water vapor concentration X, trace substances C and density. For such quantities, sensors with two fluid ports need to be used. An exception is if the quantity is measured directly in a fluid volume, such as modeled in models of the package Buildings.Fluid.MixingVolumes. Therefore, to measure for example the outlet temperature of a heat exchanger, the configuration on the left in the figure below should be used, and not the configuration on the right. For an explanation, see Modelica.Fluid.Examples.Explanatory.MeasuringTemperature.

Correct use |
Not recommended |

Except for the mass flow rate sensor, all sensors with two ports can be configured as dynamic sensors or as steady-state sensor. For numerical reasons, if the sensor output signal is not multiplied by the mass flow rate, then it is strongly suggested to configure these sensors as a dynamic sensor, which the default setting. Configuring a sensor as a dynamic sensor is done by setting the time constant to a non-zero value. Typically, setting `tau=10` seconds yields good results. For `tau=0`, numerical problems may occur if mass flow rates are close to zero.

If the sensor output signal is the product of mass flow rate times a measured fluid property, such as sensors for volumentric flow rate or enthalpy flow rate, then the sensor is by default configured as steady-state sensor. These sensors may be configured by the user as a dynamic sensor by setting `tau > 0`, but there is typically little benefit as these sensors typically do not cause numerical problems. The reason is that these sensors multiply the quantity that is carried by the flow, such as specific enthalpy h by the mass flow rate ṁ to output the measured signal Ḣ=ṁ h. Hence, as the mass flow rate goes to zero, the sensor output signal also goes to zero, which seems to avoid numerical problems.

For static pressure measurements, sensors with one or with two ports can be used for all connection topologies.

The table below summarizes the recommendations for the use of sensors.

Measured quantity | One port sensor | Two port sensor
--- | --- | ---
steady-state (`tau=0`) | dynamic (`tau > 0`)
temperature relative humidity mass fraction trace substances specific enthalpy | use only if connected to a volume | avoid | recommended
volume flow rate enthalpy flow rate | - | recommended | recommended
pressure | recommended | recommended | recommended

#### Sensor Dynamics

If a sensor is configured as a dynamic sensor by setting `tau > 0`, then the measured quantity, say the temperature T, is computed as

τ dT ⁄ dt = |ṁ| ⁄ ṁ0 (θ-T),

where τ is a user-defined time constant of the sensor (a suggested value is around 10 seconds, which is the default setting for the components), dT ⁄ dt is the time derivative of the sensor output signal, |ṁ| is the absolute value of the mass flow rate, ṁ0 is the user-specified nominal value of the mass flow rate and θ is the temperature of the medium inside the sensor. An equivalent physical model of such a sensor would be a perfectly mixed volume with a sensor that outputs the temperature of this volume. In this situation, the size of the volume would be V=τ ṁ0 ⁄ ρ, where ρ is the density of the fluid.

#### Implementation

The above equation is implemented in such a way that it is differentiable in the mass flow rate.

Note that the implementation of the dynamic sensors does not use the model Buildings.Fluid.MixingVolumes. The reason is that depending on the selected medium model, the mixing volume may introduce states for the pressure, species concentration, trace substance and enthalpy. Not all states are typically needed to model the dynamics of a sensor. Moreover, in many building system applications, the sensor dynamics is not of concern, but is rather used here to avoid numerical problems that steady-state models of sensors cause when flow rates are very close to zero.

Extends from Modelica.Icons.Information (Icon for general information packages).