Description: "Package with models for control set points"

- Home > Modelica

## Buildings.Controls.SetPoints

Package with models for control set points

### Information

This package contains components models to compute set points of control systems. For additional models, see also Modelica.Blocks.Continuous.

Extends from Modelica.Icons.VariantsPackage (Icon for package containing variants).

### Package Content

Name | Description
--- | ---
HotWaterTemperatureReset | Block to compute the supply and return set point of heating systems
OccupancySchedule | Occupancy schedule with look-ahead
Table | Model for a set point that is interpolated based on a user-specified table
Examples | Collection of models that illustrate model use and test models

## Buildings.Controls.SetPoints.HotWaterTemperatureReset

Block to compute the supply and return set point of heating systems

### Information

This block computes the set point temperatures for the supply and return temperature of a heating system. The set point for the room air temperature can either be specified by a parameter, or it can be an input to the model. The latter allows to use this model with systems that have night set back.

The parameter `dTOutHeaBal` can be used to shift the heating curve to take into account that heat gains from solar, equipment and people make up for some of the transmission losses. For example, in energy efficient houses, the heating may not be switched on if the outside air temperature is greater than 12°C, even if a room temperature of 20°C is required. In such a situation, set `dTOutHeaBal=20-12=8` Kelvin to shift the heating curve.

Extends from Modelica.Blocks.Icons.Block (Basic graphical layout of input/output block).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | m | 1.3 | Exponent for heat transfer
Boolean | use_TRoo_in | false | Get the room temperature set point from the input connector
Temperature | TRoo | 293.15 | Fixed value of room temperature set point [K]
TemperatureDifference | dTOutHeaBal | 8 | Offset for heating curve [K]
Nominal conditions
Temperature | TSup_nominal |  | Supply temperature [K]
Temperature | TRet_nominal |  | Return temperature [K]
Temperature | TRoo_nominal | 293.15 | Room temperature [K]
Temperature | TOut_nominal |  | Outside temperature [K]

### Connectors

Type | Name | Description
--- | --- | ---
input RealInput | TRoo_in | Room air temperature set point [K]
input RealInput | TOut | Outside temperature [K]
output RealOutput | TSup | Setpoint for supply temperature [K]
output RealOutput | TRet | Setpoint for return temperature [K]

### Modelica definition

block HotWaterTemperatureReset "Block to compute the supply and return set point of heating systems" extends Modelica.Blocks.Icons.Block; parameter Real m = 1.3 "Exponent for heat transfer"; parameter Modelica.SIunits.Temperature TSup_nominal "Supply temperature"; parameter Modelica.SIunits.Temperature TRet_nominal "Return temperature"; parameter Modelica.SIunits.Temperature TRoo_nominal = 293.15 "Room temperature"; parameter Modelica.SIunits.Temperature TOut_nominal "Outside temperature"; parameter Boolean use_TRoo_in = false "Get the room temperature set point from the input connector"; parameter Modelica.SIunits.Temperature TRoo = 293.15 "Fixed value of room temperature set point"; parameter Modelica.SIunits.TemperatureDifference dTOutHeaBal(displayUnit="K") = 8 "Offset for heating curve"; Modelica.Blocks.Interfaces.RealInput TRoo_in(final quantity="ThermodynamicTemperature", final unit = "K", displayUnit = "degC", min=0) if use_TRoo_in "Room air temperature set point"; Modelica.Blocks.Interfaces.RealInput TOut(final quantity="ThermodynamicTemperature", final unit = "K", displayUnit = "degC", min=0) "Outside temperature"; Modelica.Blocks.Interfaces.RealOutput TSup(final quantity="ThermodynamicTemperature", final unit = "K", displayUnit = "degC", min=0) "Setpoint for supply temperature"; Modelica.Blocks.Interfaces.RealOutput TRet(final quantity="ThermodynamicTemperature", final unit = "K", displayUnit = "degC", min=0) "Setpoint for return temperature"; protected Modelica.Blocks.Interfaces.RealInput TRoo_in_internal(final quantity="ThermodynamicTemperature", final unit = "K", displayUnit = "degC", min=0) "Needed to connect to conditional connector"; Real qRel "Relative heating load = Q_flow/Q_flow_nominal"; Modelica.SIunits.Temperature TOutOffSet "Effective outside temperature for heat transfer (takes into account room heat gains)"; parameter Modelica.SIunits.Temperature TOutOffSet_nominal = TOut_nominal + dTOutHeaBal "Effective outside temperature for heat transfer at nominal conditions (takes into account room heat gains)"; equation connect(TRoo_in, TRoo_in_internal); if not use_TRoo_in then TRoo_in_internal = TRoo; end if; TOutOffSet = TOut + dTOutHeaBal; // Relative heating load, compared to nominal conditions qRel = max(0, (TRoo_in_internal-TOutOffSet)/(TRoo_nominal-TOutOffSet_nominal)); TSup = TRoo_in_internal + ((TSup_nominal+TRet_nominal)/2-TRoo_nominal) * qRel^(1/m) + (TSup_nominal-TRet_nominal)/2 * qRel; TRet = TSup - qRel * (TSup_nominal-TRet_nominal); end HotWaterTemperatureReset;

## Buildings.Controls.SetPoints.OccupancySchedule

Occupancy schedule with look-ahead

### Information

This model outputs whether the building is currently occupied, and how long it will take until the next time when the building will be occupied or non-occupied. The latter may be used, for example, to start a ventilation system half an hour before occupancy starts in order to ventilate the room.

The occupancy is defined by a time schedule of the form

      occupancy = 3600*{7, 12, 14, 19}

This indicates that the occupancy is from 7:00 until 12:00 and from 14:00 to 19:00. This will be repeated periodically. The parameter `periodicity` defines the periodicity. The period always starts at t=0 seconds.

Extends from Modelica.Blocks.Icons.Block (Basic graphical layout of input/output block).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | occupancy[:] | 3600*{7,19} | Occupancy table, each entry switching occupancy on or off
Boolean | firstEntryOccupied | true | Set to true if first entry in occupancy denotes a changed from unoccupied to occupied
Time | period | 86400 | End time of periodicity [s]

### Connectors

Type | Name | Description
--- | --- | ---
output RealOutput | tNexNonOcc | Time until next non-occupancy
output RealOutput | tNexOcc | Time until next occupancy
output BooleanOutput | occupied | Outputs true if occupied at current time

### Modelica definition

block OccupancySchedule "Occupancy schedule with look-ahead" extends Modelica.Blocks.Icons.Block; parameter Real occupancy[:]=3600*{7, 19} "Occupancy table, each entry switching occupancy on or off"; parameter Boolean firstEntryOccupied = true "Set to true if first entry in occupancy denotes a changed from unoccupied to occupied"; parameter Modelica.SIunits.Time period = 86400 "End time of periodicity"; Modelica.Blocks.Interfaces.RealOutput tNexNonOcc "Time until next non-occupancy"; Modelica.Blocks.Interfaces.RealOutput tNexOcc "Time until next occupancy"; Modelica.Blocks.Interfaces.BooleanOutput occupied "Outputs true if occupied at current time"; protected final parameter Integer nRow = size(occupancy,1) "Number of rows in the schedule"; output Modelica.SIunits.Time offSet=integer(time/period)*period "Time off-set, in multiples of period, that is used to switch the time when doing the table lookup"; output Integer nexStaInd "Next index when occupancy starts"; output Integer nexStoInd "Next index when occupancy stops"; output Integer iPerSta "Counter for the period in which the next occupancy starts"; output Integer iPerSto "Counter for the period in which the next occupancy stops"; output Modelica.SIunits.Time tOcc "Time when next occupancy starts"; output Modelica.SIunits.Time tNonOcc "Time when next non-occupancy starts"; encapsulated function switchInteger input Integer x1; input Integer x2; output Integer y1; output Integer y2; algorithm y1:=x2; y2:=x1; end switchInteger; encapsulated function switchReal input Real x1; input Real x2; output Real y1; output Real y2; algorithm y1:=x2; y2:=x1; end switchReal; initial algorithm // Check parameters for correctness assert(mod(nRow, 2) < 0.1, "The parameter \"occupancy\" must have an even number of elements.\n"); assert(0 < occupancy[1], "The first element of \"occupancy\" must be bigger than zero." + "\n Received occupancy[1] = " + String(occupancy[1])); assert(period > occupancy[nRow], "The parameter \"period\" must be greater than the last element of \"occupancy\"." + "\n Received period = " + String(period) + "\n occupancy[" + String(nRow) + "] = " + String(occupancy[nRow])); for i in 1:nRow-1 loop assert(occupancy[i] < occupancy[i+1], "The elements of the parameter \"occupancy\" must be strictly increasing."); end for; // Initialize variables iPerSta := integer(time/period); iPerSto := iPerSta; // First, assume that the first entry is occupied nexStaInd := 1; nexStoInd := 2; // nRow is an even number for i in 1:2:nRow-1 loop if time >= occupancy[i] + iPerSta*period then nexStaInd := i+2; end if; end for; for i in 2:2:nRow loop if time >= occupancy[i] + iPerSto*period then nexStoInd := i+2; end if; end for; if nexStaInd > nRow then nexStaInd := 1; iPerSta :=iPerSta + 1; end if; if nexStoInd > nRow then nexStoInd := 2; iPerSto :=iPerSto + 1; end if; tOcc := occupancy[nexStaInd]+iPerSta*period; tNonOcc := occupancy[nexStoInd]+iPerSto*period; occupied := tNonOcc < tOcc; // Now, correct if the first entry is vaccant instead of occupied if not firstEntryOccupied then (nexStaInd, nexStoInd) := switchInteger(nexStaInd, nexStoInd); (iPerSta, iPerSto) := switchInteger(iPerSta, iPerSto); (tOcc, tNonOcc) := switchReal(tOcc, tNonOcc); occupied := not occupied; end if; algorithm when time >= pre(tOcc) then nexStaInd :=nexStaInd + 2; occupied := not occupied; // Wrap index around if nexStaInd > nRow then nexStaInd := if firstEntryOccupied then 1 else 2; iPerSta :=iPerSta + 1; end if; tOcc := occupancy[nexStaInd] + iPerSta*period; end when; // Changed the index that computes the time until the next non-occupancy when time >= pre(tNonOcc) then nexStoInd :=nexStoInd + 2; occupied := not occupied; // Wrap index around if nexStoInd > nRow then nexStoInd := if firstEntryOccupied then 2 else 1; iPerSto :=iPerSto + 1; end if; tNonOcc := occupancy[nexStoInd] + iPerSto*period; end when; tNexOcc := tOcc-time; tNexNonOcc := tNonOcc-time; assert(tNexOcc > -1e-3 and tNexOcc < period+1E-3, "tNexOcc must be non-zero and smaller than period. Received tNexOcc = " + String(tNexOcc)); assert(tNexNonOcc > -1e-3 and tNexOcc < period+1E-3, "tNexNonOcc must be non-zero and smaller than period. Received tNexNonOcc = " + String(tNexNonOcc)); end OccupancySchedule;

## Buildings.Controls.SetPoints.Table

Model for a set point that is interpolated based on a user-specified table

### Information

This block can be used to schedule a set-point by using piecewise linear functions. For example, the instances

    Buildings.Controls.SetPoints.Table tabLinExt(constantExtrapolation=false,
                                                 table=[20, 0.0;
                                                        22, 0.5;
                                                        25, 0.5;
                                                        26, 1.0]);
    Buildings.Controls.SetPoints.Table tabConExt(constantExtrapolation=true,
                                                 table=[20, 0.0;
                                                        22, 0.5;
                                                        25, 0.5;
                                                        26, 1.0]);

will cause the following output:

For the default setting `constantExtrapolation=true`, the block outputs `y=y1+offset` for `u ≤ u1`, and `y=yMax+offset` for `u ≥ uMax`. Otherwise, the table is linearly extrapolated with a constant derivative.

Note that the first column must be strictly increasing.

Extends from Modelica.Blocks.Interfaces.SISO (Single Input Single Output continuous control block).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | table[:, 2] | fill(0.0, 1, 2) | Table matrix ( e.g., table=[u1, y1; u2, y2; u3, y3])
Real | offset | 0 | Offset of output signal
Boolean | constantExtrapolation | true | If true, then y=y1 for u<u1, and y=yMax for u>uMax

### Connectors

Type | Name | Description
--- | --- | ---
input RealInput | u | Connector of Real input signal
output RealOutput | y | Connector of Real output signal

### Modelica definition

model Table "Model for a set point that is interpolated based on a user-specified table" extends Modelica.Blocks.Interfaces.SISO; parameter Real table[:,2]=fill(0.0, 1, 2) "Table matrix ( e.g., table=[u1, y1; u2, y2; u3, y3])"; parameter Real offset=0 "Offset of output signal"; parameter Boolean constantExtrapolation = true "If true, then y=y1 for u<u1, and y=yMax for u>uMax"; protected final parameter Integer nCol = if constantExtrapolation then size(table,1)+2 else size(table,1) "Number of columns"; final parameter Real[nCol,2] offsetVector = [zeros(nCol), offset*ones(nCol)] "Vector to take offset of output signal into account"; Modelica.Blocks.Tables.CombiTable1D tab( tableOnFile=false, final table= (if constantExtrapolation then cat(1, [table[1,1]-1, table[1,2]], table, [table[end,1]+1, table[end,2]]) else table) +offsetVector) "Table used for interpolation"; equation connect(u, tab.u[1]); connect(tab.y[1], y); end Table;