Description: "Performance data for chiller ElectricEIR"

- Home > Modelica

## Buildings.Fluid.Chillers.Data.ElectricEIR

Performance data for chiller ElectricEIR

### Information

Package with performance data for chillers.

Extends from Modelica.Icons.MaterialPropertiesPackage (Icon for package containing property classes).

### Package Content

Name | Description
--- | ---
Generic | Generic data record for chiller ElectricEIR
ElectricEIRChiller_McQuay_WSC_471kW_5_89COP_Vanes | ElectricEIRChiller McQuay WSC 471kW/5.89COP/Vanes
ElectricEIRChiller_York_YT_563kW_10_61COP_Vanes | ElectricEIRChiller York YT 563kW/10.61COP/Vanes
ElectricEIRChiller_McQuay_PEH_703kW_7_03COP_Vanes | ElectricEIRChiller McQuay PEH 703kW/7.03COP/Vanes
ElectricEIRChiller_Carrier_23XL_724kW_6_04COP_Vanes | ElectricEIRChiller Carrier 23XL 724kW/6.04COP/Vanes
ElectricEIRChiller_Carrier_19XR_742kW_5_42COP_VSD | ElectricEIRChiller Carrier 19XR 742kW/5.42COP/VSD
ElectricEIRChiller_McQuay_WSC_816kW_6_74COP_Vanes | ElectricEIRChiller McQuay WSC 816kW/6.74COP/Vanes
ElectricEIRChiller_McQuay_PEH_819kW_8_11COP_Vanes | ElectricEIRChiller McQuay PEH 819kW/8.11COP/Vanes
ElectricEIRChiller_Carrier_19XR_823kW_6_28COP_Vanes | ElectricEIRChiller Carrier 19XR 823kW/6.28COP/Vanes
ElectricEIRChiller_Carrier_19XR_869kW_5_57COP_VSD | ElectricEIRChiller Carrier 19XR 869kW/5.57COP/VSD
ElectricEIRChiller_Carrier_19XR_897kW_7_23COP_VSD | ElectricEIRChiller Carrier 19XR 897kW/7.23COP/VSD
ElectricEIRChiller_Carrier_19XR_897kW_6_50COP_Vanes | ElectricEIRChiller Carrier 19XR 897kW/6.50COP/Vanes
ElectricEIRChiller_York_YT_897kW_7_60COP_VSD | ElectricEIRChiller York YT 897kW/7.60COP/VSD
ElectricEIRChiller_York_YT_897kW_6_27COP_VSD | ElectricEIRChiller York YT 897kW/6.27COP/VSD
ElectricEIRChiller_Carrier_19XR_897kW_6_23COP_VSD | ElectricEIRChiller Carrier 19XR 897kW/6.23COP/VSD
ElectricEIRChiller_McQuay_PFH_932kW_5_09COP_Vanes | ElectricEIRChiller McQuay PFH 932kW/5.09COP/Vanes
ElectricEIRChiller_York_YT_960kW_4_64COP_Vanes | ElectricEIRChiller York YT 960kW/4.64COP/Vanes
ElectricEIRChiller_York_YT_1023kW_5_81COP_Vanes | ElectricEIRChiller York YT 1023kW/5.81COP/Vanes
ElectricEIRChiller_McQuay_PEH_1030kW_8_58COP_Vanes | ElectricEIRChiller McQuay PEH 1030kW/8.58COP/Vanes
ElectricEIRChiller_York_YT_1048kW_6_06COP_Vanes | ElectricEIRChiller York YT 1048kW/6.06COP/Vanes
ElectricEIRChiller_York_YT_1055kW_5_96COP_Vanes | ElectricEIRChiller York YT 1055kW/5.96COP/Vanes
ElectricEIRChiller_Carrier_19XR_1076kW_5_52COP_Vanes | ElectricEIRChiller Carrier 19XR 1076kW/5.52COP/Vanes
ElectricEIRChiller_Trane_CVHE_1080kW_7_39COP_Vanes | ElectricEIRChiller Trane CVHE 1080kW/7.39COP/Vanes
ElectricEIRChiller_York_YT_1090kW_7_57COP_VSD | ElectricEIRChiller York YT 1090kW/7.57COP/VSD
ElectricEIRChiller_McQuay_PEH_1104kW_8_00COP_Vanes | ElectricEIRChiller McQuay PEH 1104kW/8.00COP/Vanes
ElectricEIRChiller_Trane_CVHE_1125kW_4_89COP_Vanes | ElectricEIRChiller Trane CVHE 1125kW/4.89COP/Vanes
ElectricEIRChiller_York_YT_1125kW_7_92COP_VSD | ElectricEIRChiller York YT 1125kW/7.92COP/VSD
ElectricEIRChiller_Trane_CVHE_1129kW_7_19COP_Vanes | ElectricEIRChiller Trane CVHE 1129kW/7.19COP/Vanes
ElectricEIRChiller_Carrier_19XR_1143kW_6_57COP_VSD | ElectricEIRChiller Carrier 19XR 1143kW/6.57COP/VSD
ElectricEIRChiller_Carrier_19XR_1157kW_5_62COP_VSD | ElectricEIRChiller Carrier 19XR 1157kW/5.62COP/VSD
ElectricEIRChiller_Carrier_19XR_1196kW_6_50COP_Vanes | ElectricEIRChiller Carrier 19XR 1196kW/6.50COP/Vanes
ElectricEIRChiller_Carrier_19XR_1213kW_7_78COP_Vanes | ElectricEIRChiller Carrier 19XR 1213kW/7.78COP/Vanes
ElectricEIRChiller_McQuay_PEH_1231kW_6_18COP_Vanes | ElectricEIRChiller McQuay PEH 1231kW/6.18COP/Vanes
ElectricEIRChiller_Carrier_19XR_1234kW_5_39COP_VSD | ElectricEIRChiller Carrier 19XR 1234kW/5.39COP/VSD
ElectricEIRChiller_Carrier_19XR_1259kW_6_26COP_Vanes | ElectricEIRChiller Carrier 19XR 1259kW/6.26COP/Vanes
ElectricEIRChiller_York_YK_1259kW_6_45COP_Vanes | ElectricEIRChiller York YK 1259kW/6.45COP/Vanes
ElectricEIRChiller_York_YT_1266kW_4_39COP_Vanes | ElectricEIRChiller York YT 1266kW/4.39COP/Vanes
ElectricEIRChiller_Carrier_19XR_1284kW_6_20COP_Vanes | ElectricEIRChiller Carrier 19XR 1284kW/6.20COP/Vanes
ElectricEIRChiller_Carrier_19XR_1294kW_7_61COP_Vanes | ElectricEIRChiller Carrier 19XR 1294kW/7.61COP/Vanes
ElectricEIRChiller_Trane_CVHE_1329kW_5_38COP_Vanes | ElectricEIRChiller Trane CVHE 1329kW/5.38COP/Vanes
ElectricEIRChiller_Carrier_19XR_1350kW_7_90COP_VSD | ElectricEIRChiller Carrier 19XR 1350kW/7.90COP/VSD
ElectricEIRChiller_York_YT_1368kW_7_35COP_VSD | ElectricEIRChiller York YT 1368kW/7.35COP/VSD
ElectricEIRChiller_Trane_CVHE_1372kW_7_49COP_Vanes | ElectricEIRChiller Trane CVHE 1372kW/7.49COP/Vanes
ElectricEIRChiller_York_YT_1396kW_7_35COP_Vanes | ElectricEIRChiller York YT 1396kW/7.35COP/Vanes
ElectricEIRChiller_Carrier_19XR_1403kW_7_09COP_VSD | ElectricEIRChiller Carrier 19XR 1403kW/7.09COP/VSD
ElectricEIRChiller_York_YT_1403kW_6_94COP_VSD | ElectricEIRChiller York YT 1403kW/6.94COP/VSD
ElectricEIRChiller_Trane_CVHE_1407kW_7_14COP_VSD | ElectricEIRChiller Trane CVHE 1407kW/7.14COP/VSD
ElectricEIRChiller_McQuay_PFH_1407kW_6_60COP_Vanes | ElectricEIRChiller McQuay PFH 1407kW/6.60COP/Vanes
ElectricEIRChiller_Carrier_19XR_1407kW_6_04COP_VSD | ElectricEIRChiller Carrier 19XR 1407kW/6.04COP/VSD
ElectricEIRChiller_Carrier_19XR_1410kW_8_54COP_VSD | ElectricEIRChiller Carrier 19XR 1410kW/8.54COP/VSD
ElectricEIRChiller_Trane_CVHE_1442kW_6_61COP_VSD | ElectricEIRChiller Trane CVHE 1442kW/6.61COP/VSD
ElectricEIRChiller_York_YT_1459kW_6_40COP_VSD | ElectricEIRChiller York YT 1459kW/6.40COP/VSD
ElectricEIRChiller_Trane_CVHE_1484kW_9_96COP_VSD | ElectricEIRChiller Trane CVHE 1484kW/9.96COP/VSD
ElectricEIRChiller_York_YT_1495kW_7_51COP_VSD | ElectricEIRChiller York YT 1495kW/7.51COP/VSD
ElectricEIRChiller_McQuay_WSC_1519kW_7_10COP_Vanes | ElectricEIRChiller McQuay WSC 1519kW/7.10COP/Vanes
ElectricEIRChiller_Carrier_19XR_1558kW_5_81COP_VSD | ElectricEIRChiller Carrier 19XR 1558kW/5.81COP/VSD
ElectricEIRChiller_Carrier_19XR_1586kW_5_53COP_VSD | ElectricEIRChiller Carrier 19XR 1586kW/5.53COP/VSD
ElectricEIRChiller_McQuay_PEH_1635kW_7_47COP_Vanes | ElectricEIRChiller McQuay PEH 1635kW/7.47COP/Vanes
ElectricEIRChiller_Carrier_19XR_1635kW_6_36COP_Vanes | ElectricEIRChiller Carrier 19XR 1635kW/6.36COP/Vanes
ElectricEIRChiller_Carrier_19XR_1656kW_8_24COP_VSD | ElectricEIRChiller Carrier 19XR 1656kW/8.24COP/VSD
ElectricEIRChiller_York_YT_1663kW_9_34COP_Vanes | ElectricEIRChiller York YT 1663kW/9.34COP/Vanes
ElectricEIRChiller_Carrier_19XL_1674kW_7_89COP_Vanes | ElectricEIRChiller Carrier 19XL 1674kW/7.89COP/Vanes
ElectricEIRChiller_Trane_CVHF_1681kW_6_59COP_Vanes | ElectricEIRChiller Trane CVHF 1681kW/6.59COP/Vanes
ElectricEIRChiller_Carrier_19XR_1723kW_8_32COP_VSD | ElectricEIRChiller Carrier 19XR 1723kW/8.32COP/VSD
ElectricEIRChiller_Carrier_19XR_1727kW_9_04COP_Vanes | ElectricEIRChiller Carrier 19XR 1727kW/9.04COP/Vanes
ElectricEIRChiller_McQuay_WSC_1751kW_6_73COP_Vanes | ElectricEIRChiller McQuay WSC 1751kW/6.73COP/Vanes
ElectricEIRChiller_Trane_CVHF_1758kW_5_96COP_Vanes | ElectricEIRChiller Trane CVHF 1758kW/5.96COP/Vanes
ElectricEIRChiller_York_YT_1758kW_5_76COP_VSD | ElectricEIRChiller York YT 1758kW/5.76COP/VSD
ElectricEIRChiller_York_YT_1758kW_6_26COP_Vanes | ElectricEIRChiller York YT 1758kW/6.26COP/Vanes
ElectricEIRChiller_York_YT_1758kW_5_96COP_Vanes | ElectricEIRChiller York YT 1758kW/5.96COP/Vanes
ElectricEIRChiller_Trane_CVHE_1758kW_5_96COP_Vanes | ElectricEIRChiller Trane CVHE 1758kW/5.96COP/Vanes
ElectricEIRChiller_York_YT_1758kW_6_28COP_Vanes | ElectricEIRChiller York YT 1758kW/6.28COP/Vanes
ElectricEIRChiller_Carrier_19XR_1758kW_5_86COP_VSD | ElectricEIRChiller Carrier 19XR 1758kW/5.86COP/VSD
ElectricEIRChiller_Trane_CVHF_1758kW_6_46COP_VSD | ElectricEIRChiller Trane CVHF 1758kW/6.46COP/VSD
ElectricEIRChiller_Trane_CVHF_1758kW_6_87COP_Vanes | ElectricEIRChiller Trane CVHF 1758kW/6.87COP/Vanes
ElectricEIRChiller_Carrier_19XR_1776kW_8_00COP_Vanes | ElectricEIRChiller Carrier 19XR 1776kW/8.00COP/Vanes
ElectricEIRChiller_Carrier_19XL_1779kW_6_18COP_Vanes | ElectricEIRChiller Carrier 19XL 1779kW/6.18COP/Vanes
ElectricEIRChiller_Trane_CVHF_1779kW_6_18COP_Vanes | ElectricEIRChiller Trane CVHF 1779kW/6.18COP/Vanes
ElectricEIRChiller_York_YT_1794kW_8_11COP_Vanes | ElectricEIRChiller York YT 1794kW/8.11COP/Vanes
ElectricEIRChiller_York_YT_1794kW_7_90COP_VSD | ElectricEIRChiller York YT 1794kW/7.90COP/VSD
ElectricEIRChiller_Carrier_19XL_1797kW_5_69COP_Vanes | ElectricEIRChiller Carrier 19XL 1797kW/5.69COP/Vanes
ElectricEIRChiller_Carrier_19XR_1801kW_6_34COP_VSD | ElectricEIRChiller Carrier 19XR 1801kW/6.34COP/VSD
ElectricEIRChiller_York_YT_1867kW_10_09COP_Vanes | ElectricEIRChiller York YT 1867kW/10.09COP/Vanes
ElectricEIRChiller_Carrier_19XL_1871kW_6_49COP_Vanes | ElectricEIRChiller Carrier 19XL 1871kW/6.49COP/Vanes
ElectricEIRChiller_York_YT_1881kW_6_77COP_VSD | ElectricEIRChiller York YT 1881kW/6.77COP/VSD
ElectricEIRChiller_York_YK_1881kW_6_53COP_Vanes | ElectricEIRChiller York YK 1881kW/6.53COP/Vanes
ElectricEIRChiller_McQuay_PEH_1895kW_6_42COP_Vanes | ElectricEIRChiller McQuay PEH 1895kW/6.42COP/Vanes
ElectricEIRChiller_York_YT_1934kW_7_55COP_Vanes | ElectricEIRChiller York YT 1934kW/7.55COP/Vanes
ElectricEIRChiller_McQuay_PEH_1934kW_6_01COP_Vanes | ElectricEIRChiller McQuay PEH 1934kW/6.01COP/Vanes
ElectricEIRChiller_McQuay_WDC_1973kW_6_28COP_Vanes | ElectricEIRChiller McQuay WDC 1973kW/6.28COP/Vanes
ElectricEIRChiller_York_YK_1997kW_7_24COP_Vanes | ElectricEIRChiller York YK 1997kW/7.24COP/Vanes
ElectricEIRChiller_McQuay_PFH_2043kW_8_44COP_Vanes | ElectricEIRChiller McQuay PFH 2043kW/8.44COP/Vanes
ElectricEIRChiller_Trane_CVHF_2043kW_9_08COP_Vanes | ElectricEIRChiller Trane CVHF 2043kW/9.08COP/Vanes
ElectricEIRChiller_Carrier_19XL_2057kW_6_05COP_Vanes | ElectricEIRChiller Carrier 19XL 2057kW/6.05COP/Vanes
ElectricEIRChiller_York_YT_2110kW_7_15COP_Vanes | ElectricEIRChiller York YT 2110kW/7.15COP/Vanes
ElectricEIRChiller_McQuay_PFH_2124kW_6_03COP_Vanes | ElectricEIRChiller McQuay PFH 2124kW/6.03COP/Vanes
ElectricEIRChiller_York_YK_2159kW_6_85COP_Vanes | ElectricEIRChiller York YK 2159kW/6.85COP/Vanes
ElectricEIRChiller_Trane_CVHF_2184kW_6_78COP_Vanes | ElectricEIRChiller Trane CVHF 2184kW/6.78COP/Vanes
ElectricEIRChiller_York_YK_2201kW_6_69COP_Vanes | ElectricEIRChiller York YK 2201kW/6.69COP/Vanes
ElectricEIRChiller_York_YT_2233kW_9_54COP_VSD | ElectricEIRChiller York YT 2233kW/9.54COP/VSD
ElectricEIRChiller_York_YK_2237kW_6_41COP_Vanes | ElectricEIRChiller York YK 2237kW/6.41COP/Vanes
ElectricEIRChiller_York_YK_2275kW_6_32COP_Vanes | ElectricEIRChiller York YK 2275kW/6.32COP/Vanes
ElectricEIRChiller_Trane_CVHF_2300kW_8_10COP_Vanes | ElectricEIRChiller Trane CVHF 2300kW/8.10COP/Vanes
ElectricEIRChiller_Trane_CVHF_2317kW_6_33COP_VSD | ElectricEIRChiller Trane CVHF 2317kW/6.33COP/VSD
ElectricEIRChiller_Carrier_19XR_2391kW_6_77COP_Vanes | ElectricEIRChiller Carrier 19XR 2391kW/6.77COP/Vanes
ElectricEIRChiller_Carrier_19XR_2391kW_6_44COP_VSD | ElectricEIRChiller Carrier 19XR 2391kW/6.44COP/VSD
ElectricEIRChiller_York_YK_2412kW_5_58COP_Vanes | ElectricEIRChiller York YK 2412kW/5.58COP/Vanes
ElectricEIRChiller_McQuay_PFH_2462kW_6_67COP_Vanes | ElectricEIRChiller McQuay PFH 2462kW/6.67COP/Vanes
ElectricEIRChiller_Trane_CVHF_2567kW_11_77COP_VSD | ElectricEIRChiller Trane CVHF 2567kW/11.77COP/VSD
ElectricEIRChiller_York_YK_2771kW_6_84COP_VSD | ElectricEIRChiller York YK 2771kW/6.84COP/VSD
ElectricEIRChiller_Trane_CVHF_2799kW_6_40COP_Vanes | ElectricEIRChiller Trane CVHF 2799kW/6.40COP/Vanes
ElectricEIRChiller_York_YT_3133kW_9_16COP_Vanes | ElectricEIRChiller York YT 3133kW/9.16COP/Vanes
ElectricEIRChiller_McQuay_PFH_3165kW_6_48COP_Vanes | ElectricEIRChiller McQuay PFH 3165kW/6.48COP/Vanes
ElectricEIRChiller_McQuay_PFH_4020kW_7_35COP_Vanes | ElectricEIRChiller McQuay PFH 4020kW/7.35COP/Vanes
ElectricEIRChiller_York_YK_4396kW_6_63COP_Vanes | ElectricEIRChiller York YK 4396kW/6.63COP/Vanes
ElectricEIRChiller_York_YK_4477kW_6_64COP_Vanes | ElectricEIRChiller York YK 4477kW/6.64COP/Vanes
ElectricEIRChiller_York_YK_4515kW_6_22COP_Vanes | ElectricEIRChiller York YK 4515kW/6.22COP/Vanes
ElectricEIRChiller_York_YK_4537kW_6_28COP_Vanes | ElectricEIRChiller York YK 4537kW/6.28COP/Vanes
ElectricEIRChiller_Trane_CVHF_4610kW_6_34COP_Vanes | ElectricEIRChiller Trane CVHF 4610kW/6.34COP/Vanes
ElectricEIRChiller_Carrier_19EX_4667kW_6_16COP_Vanes | ElectricEIRChiller Carrier 19EX 4667kW/6.16COP/Vanes
ElectricEIRChiller_Trane_CVHF_4677kW_6_27COP_Vanes | ElectricEIRChiller Trane CVHF 4677kW/6.27COP/Vanes
ElectricEIRChiller_York_YK_4966kW_6_05COP_Vanes | ElectricEIRChiller York YK 4966kW/6.05COP/Vanes
ElectricEIRChiller_York_YK_4969kW_7_14COP_Vanes | ElectricEIRChiller York YK 4969kW/7.14COP/Vanes
ElectricEIRChiller_York_YK_4969kW_7_07COP_Vanes | ElectricEIRChiller York YK 4969kW/7.07COP/Vanes
ElectricEIRChiller_Carrier_19EX_4997kW_6_40COP_Vanes | ElectricEIRChiller Carrier 19EX 4997kW/6.40COP/Vanes
ElectricEIRChiller_Carrier_19EX_5148kW_6_34COP_Vanes | ElectricEIRChiller Carrier 19EX 5148kW/6.34COP/Vanes
ElectricEIRChiller_York_YK_5170kW_7_15COP_Vanes | ElectricEIRChiller York YK 5170kW/7.15COP/Vanes
ElectricEIRChiller_Carrier_19EX_5208kW_6_88COP_Vanes | ElectricEIRChiller Carrier 19EX 5208kW/6.88COP/Vanes
ElectricEIRChiller_York_YK_5465kW_6_94COP_Vanes | ElectricEIRChiller York YK 5465kW/6.94COP/Vanes
ElectricEIRChiller_York_YK_5549kW_6_50COP_Vanes | ElectricEIRChiller York YK 5549kW/6.50COP/Vanes
ElectricEIRChiller_Carrier_19FA_5651kW_5_50COP_Vanes | ElectricEIRChiller Carrier 19FA 5651kW/5.50COP/Vanes
DOE_2_Centrifugal_5_50COP | DOE-2 Centrifugal/5.50COP
ElectricEIRChiller_Multistack_MS_172kW_3_67COP_None | ElectricEIRChiller Multistack MS 172kW/3.67COP/None
DOE_2_Reciprocating_3_67COP | DOE-2 Reciprocating/3.67COP
ElectricEIRChiller_Trane_RTWA_383kW_4_17COP_Valve | ElectricEIRChiller Trane RTWA 383kW/4.17COP/Valve
ElectricEIRChiller_Trane_RTHB_531kW_4_83COP_Valve | ElectricEIRChiller Trane RTHB 531kW/4.83COP/Valve
ElectricEIRChiller_Trane_RTHB_538kW_5_12COP_Valve | ElectricEIRChiller Trane RTHB 538kW/5.12COP/Valve
ElectricEIRChiller_Trane_RTHB_542kW_5_26COP_Valve | ElectricEIRChiller Trane RTHB 542kW/5.26COP/Valve
ElectricEIRChiller_York_YS_672kW_7_90COP_Valve | ElectricEIRChiller York YS 672kW/7.90COP/Valve
ElectricEIRChiller_Carrier_23XL_686kW_5_91COP_Valve | ElectricEIRChiller Carrier 23XL 686kW/5.91COP/Valve
ElectricEIRChiller_Trane_RTHC_707kW_7_77COP_Valve | ElectricEIRChiller Trane RTHC 707kW/7.77COP/Valve
ElectricEIRChiller_York_YS_756kW_7_41COP_Valve | ElectricEIRChiller York YS 756kW/7.41COP/Valve
ElectricEIRChiller_York_YS_781kW_5_42COP_Valve | ElectricEIRChiller York YS 781kW/5.42COP/Valve
ElectricEIRChiller_Carrier_23XL_830kW_6_97COP_Valve | ElectricEIRChiller Carrier 23XL 830kW/6.97COP/Valve
ElectricEIRChiller_Carrier_23XL_862kW_6_11COP_Valve | ElectricEIRChiller Carrier 23XL 862kW/6.11COP/Valve
ElectricEIRChiller_Carrier_23XL_862kW_6_84COP_Valve | ElectricEIRChiller Carrier 23XL 862kW/6.84COP/Valve
ElectricEIRChiller_Carrier_23XL_865kW_6_05COP_Valve | ElectricEIRChiller Carrier 23XL 865kW/6.05COP/Valve
ElectricEIRChiller_York_YS_879kW_5_82COP_Valve | ElectricEIRChiller York YS 879kW/5.82COP/Valve
ElectricEIRChiller_Trane_RTHC_1009kW_5_37COP_Valve | ElectricEIRChiller Trane RTHC 1009kW/5.37COP/Valve
ElectricEIRChiller_Trane_RTHB_1051kW_5_05COP_Valve | ElectricEIRChiller Trane RTHB 1051kW/5.05COP/Valve
ElectricEIRChiller_Carrier_23XL_1062kW_5_50COP_Valve | ElectricEIRChiller Carrier 23XL 1062kW/5.50COP/Valve
ElectricEIRChiller_Trane_RTHC_1066kW_5_73COP_Valve | ElectricEIRChiller Trane RTHC 1066kW/5.73COP/Valve
ElectricEIRChiller_Trane_RTHC_1094kW_6_55COP_Valve | ElectricEIRChiller Trane RTHC 1094kW/6.55COP/Valve
ElectricEIRChiller_Carrier_23XL_1108kW_6_92COP_Valve | ElectricEIRChiller Carrier 23XL 1108kW/6.92COP/Valve
ElectricEIRChiller_York_YS_1171kW_9_15COP_Valve | ElectricEIRChiller York YS 1171kW/9.15COP/Valve
ElectricEIRChiller_Carrier_23XL_1196kW_6_39COP_Valve | ElectricEIRChiller Carrier 23XL 1196kW/6.39COP/Valve
ElectricEIRChiller_York_YS_1554kW_9_31COP_Valve | ElectricEIRChiller York YS 1554kW/9.31COP/Valve
ElectricEIRChiller_York_YS_1758kW_5_84COP_Valve | ElectricEIRChiller York YS 1758kW/5.84COP/Valve
ElectricEIRChiller_Trane_CGWD_207kW_3_99COP_None | ElectricEIRChiller Trane CGWD 207kW/3.99COP/None

## Buildings.Fluid.Chillers.Data.ElectricEIR.Generic

Generic data record for chiller ElectricEIR

### Information

This record is used as a template for performance data for the chiller model Buildings.Fluid.Chillers.ElectricEIR.

Extends from Buildings.Fluid.Chillers.Data.BaseClasses.Chiller (Base classes for chiller models).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax |  | Maximum part load ratio
Real | PLRMinUnl |  | Minimum part unload ratio
Real | PLRMin |  | Minimum part load ratio
Real | etaMotor |  | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal |  | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal |  | Reference capacity (negative number) [W]
Real | COP_nominal |  | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal |  | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal |  | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal |  | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Integer | nCapFunT | 6 | Number of coefficients for capFunT
Integer | nEIRFunT | 6 | Number of coefficients for capFunT
Integer | nEIRFunPLR | 3 | Number of coefficients for capFunT
Real | capFunT[nCapFunT] |  | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] |  | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] |  | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin |  | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax |  | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin |  | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax |  | Maximum value for entering condenser temperature [K]

### Modelica definition

record Generic "Generic data record for chiller ElectricEIR" extends Buildings.Fluid.Chillers.Data.BaseClasses.Chiller( final nCapFunT=6, final nEIRFunT=6, final nEIRFunPLR=3); parameter Modelica.SIunits.Temperature TConEnt_nominal "Temperature of fluid entering condenser at nominal condition"; parameter Modelica.SIunits.Temperature TConEntMin "Minimum value for entering condenser temperature"; parameter Modelica.SIunits.Temperature TConEntMax "Maximum value for entering condenser temperature"; end Generic;

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_McQuay_WSC_471kW_5_89COP_Vanes

ElectricEIRChiller McQuay WSC 471kW/5.89COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller McQuay WSC 471kW/5.89COP/Vanes,  !- Name
        471200,                  !- Reference Capacity {W}
        5.89,                    !- Reference COP {W/W}
        8.89,                    !- Reference Leaving Chilled Water Temperature {C}
        26.67,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.01035,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.01924,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller McQuay WSC 471kW/5.89COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller McQuay WSC 471kW/5.89COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller McQuay WSC 471kW/5.89COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.15,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.15 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.67 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -471200 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.89 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.01035 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.01924 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 8.89 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {2.521130E-01,1.324053E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {4.475238E-01,-2.588210E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.778889E-01,2.338363E-01,4... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 7.22 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 26.67 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_McQuay_WSC_471kW_5_89COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -471200, COP_nominal = 5.89, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.15, mEva_flow_nominal = 1000 * 0.01035, mCon_flow_nominal = 1000 * 0.01924, TEvaLvg_nominal = 273.15 + 8.89, TConEnt_nominal = 273.15 + 26.67, TEvaLvgMin = 273.15 + 7.22, TEvaLvgMax = 273.15 + 12.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 26.67, capFunT = {2.521130E-01,1.324053E-02,-8.637329E-03,8.581056E-02,-4.261176E-03,8.661899E-03}, EIRFunT = {4.475238E-01,-2.588210E-02,-1.459053E-03,4.342595E-02,-1.000651E-03,1.920106E-03}, EIRFunPLR = {2.778889E-01,2.338363E-01,4.883748E-01}, etaMotor = 1.0) "ElectricEIRChiller McQuay WSC 471kW/5.89COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YT_563kW_10_61COP_Vanes

ElectricEIRChiller York YT 563kW/10.61COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YT 563kW/10.61COP/Vanes,  !- Name
        562600,                  !- Reference Capacity {W}
        10.61,                   !- Reference COP {W/W}
        6.11,                    !- Reference Leaving Chilled Water Temperature {C}
        12.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.01514,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.0241,                  !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YT 563kW/10.61COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YT 563kW/10.61COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YT 563kW/10.61COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.09,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.09,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.09 | Minimum part unload ratio
Real | PLRMin | 0.09 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 12.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -562600 | Reference capacity (negative number) [W]
Real | COP_nominal | 10.61 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.01514 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.0241 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.11 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {-1.288612E-01,-8.919540E-02... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {-5.781003E-01,-1.169130E-01... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {5.203969E-01,-7.775900E-01,... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 6.11 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YT_563kW_10_61COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -562600, COP_nominal = 10.61, PLRMin = 0.09, PLRMinUnl = 0.09, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.01514, mCon_flow_nominal = 1000 * 0.0241, TEvaLvg_nominal = 273.15 + 6.11, TConEnt_nominal = 273.15 + 12.78, TEvaLvgMin = 273.15 + 6.11, TEvaLvgMax = 273.15 + 12.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {-1.288612E-01,-8.919540E-02,-2.190195E-03,1.538357E-01,-5.129402E-03,7.813636E-03}, EIRFunT = {-5.781003E-01,-1.169130E-01,-4.760535E-03,2.230082E-01,-5.313649E-03,6.846644E-03}, EIRFunPLR = {5.203969E-01,-7.775900E-01,1.255394E+00}, etaMotor = 1.0) "ElectricEIRChiller York YT 563kW/10.61COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_McQuay_PEH_703kW_7_03COP_Vanes

ElectricEIRChiller McQuay PEH 703kW/7.03COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller McQuay PEH 703kW/7.03COP/Vanes,  !- Name
        703300,                  !- Reference Capacity {W}
        7.03,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        22.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.02019,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.02902,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller McQuay PEH 703kW/7.03COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller McQuay PEH 703kW/7.03COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller McQuay PEH 703kW/7.03COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 22.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -703300 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.03 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.02019 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.02902 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {4.779439E-01,1.073486E-01,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {8.234029E-01,-1.171542E-01,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {3.864389E-01,-2.522595E-01,... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_McQuay_PEH_703kW_7_03COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -703300, COP_nominal = 7.03, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.02019, mCon_flow_nominal = 1000 * 0.02902, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 22.78, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {4.779439E-01,1.073486E-01,-1.055896E-02,4.208433E-02,-2.346870E-03,4.019632E-03}, EIRFunT = {8.234029E-01,-1.171542E-01,5.869351E-04,2.964642E-02,-9.190377E-04,5.035796E-03}, EIRFunPLR = {3.864389E-01,-2.522595E-01,8.672354E-01}, etaMotor = 1.0) "ElectricEIRChiller McQuay PEH 703kW/7.03COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_23XL_724kW_6_04COP_Vanes

ElectricEIRChiller Carrier 23XL 724kW/6.04COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 23XL 724kW/6.04COP/Vanes,  !- Name
        724400,                  !- Reference Capacity {W}
        6.04,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        21.11,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.01779,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.01956,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 23XL 724kW/6.04COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 23XL 724kW/6.04COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 23XL 724kW/6.04COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.19,                    !- Minimum Part Load Ratio
        1.04,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.19,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.04 | Maximum part load ratio
Real | PLRMinUnl | 0.19 | Minimum part unload ratio
Real | PLRMin | 0.19 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 21.11 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -724400 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.04 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.01779 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.01956 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {4.418712E-01,-8.384251E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.059102E-01,-1.621557E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.879418E-01,3.562862E-01,4... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 13.75 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_23XL_724kW_6_04COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -724400, COP_nominal = 6.04, PLRMin = 0.19, PLRMinUnl = 0.19, PLRMax = 1.04, mEva_flow_nominal = 1000 * 0.01779, mCon_flow_nominal = 1000 * 0.01956, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 21.11, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 13.75, TConEntMax = 273.15 + 23.89, capFunT = {4.418712E-01,-8.384251E-02,-2.190707E-03,8.594633E-02,-3.322575E-03,6.652189E-03}, EIRFunT = {5.059102E-01,-1.621557E-02,3.346388E-04,2.350906E-02,3.514201E-04,-6.342981E-04}, EIRFunPLR = {1.879418E-01,3.562862E-01,4.540392E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 23XL 724kW/6.04COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_742kW_5_42COP_VSD

ElectricEIRChiller Carrier 19XR 742kW/5.42COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 742kW/5.42COP/VSD,  !- Name
        742000,                  !- Reference Capacity {W}
        5.42,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        21.11,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.01779,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.01956,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 742kW/5.42COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 742kW/5.42COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 742kW/5.42COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.19,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.19,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.19 | Minimum part unload ratio
Real | PLRMin | 0.19 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 21.11 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -742000 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.42 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.01779 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.01956 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {9.797101E-01,-2.895701E-03,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {9.946139E-01,-4.829399E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.202277E-01,1.396384E-01,7... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 11.25 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_742kW_5_42COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -742000, COP_nominal = 5.42, PLRMin = 0.19, PLRMinUnl = 0.19, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.01779, mCon_flow_nominal = 1000 * 0.01956, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 21.11, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 11.25, TConEntMax = 273.15 + 23.89, capFunT = {9.797101E-01,-2.895701E-03,-8.970718E-04,1.031440E-02,-7.431651E-04,1.453508E-03}, EIRFunT = {9.946139E-01,-4.829399E-02,4.674277E-04,-1.158726E-03,5.762583E-04,2.148192E-04}, EIRFunPLR = {1.202277E-01,1.396384E-01,7.394038E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 742kW/5.42COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_McQuay_WSC_816kW_6_74COP_Vanes

ElectricEIRChiller McQuay WSC 816kW/6.74COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller McQuay WSC 816kW/6.74COP/Vanes,  !- Name
        815800,                  !- Reference Capacity {W}
        6.74,                    !- Reference COP {W/W}
        8.89,                    !- Reference Leaving Chilled Water Temperature {C}
        26.67,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.01748,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.04164,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller McQuay WSC 816kW/6.74COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller McQuay WSC 816kW/6.74COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller McQuay WSC 816kW/6.74COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.09,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.09,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.09 | Minimum part unload ratio
Real | PLRMin | 0.09 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.67 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -815800 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.74 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.01748 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.04164 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 8.89 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {9.862590E-01,5.799373E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {7.335321E-01,4.465107E-04,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {3.070136E-01,8.654874E-02,6... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 7.22 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 26.67 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_McQuay_WSC_816kW_6_74COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -815800, COP_nominal = 6.74, PLRMin = 0.09, PLRMinUnl = 0.09, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.01748, mCon_flow_nominal = 1000 * 0.04164, TEvaLvg_nominal = 273.15 + 8.89, TConEnt_nominal = 273.15 + 26.67, TEvaLvgMin = 273.15 + 7.22, TEvaLvgMax = 273.15 + 12.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 26.67, capFunT = {9.862590E-01,5.799373E-02,-5.355626E-03,-8.941705E-04,-1.670098E-03,4.733054E-03}, EIRFunT = {7.335321E-01,4.465107E-04,-3.448575E-03,3.770822E-03,-2.189675E-04,2.400267E-03}, EIRFunPLR = {3.070136E-01,8.654874E-02,6.081551E-01}, etaMotor = 1.0) "ElectricEIRChiller McQuay WSC 816kW/6.74COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_McQuay_PEH_819kW_8_11COP_Vanes

ElectricEIRChiller McQuay PEH 819kW/8.11COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller McQuay PEH 819kW/8.11COP/Vanes,  !- Name
        819300,                  !- Reference Capacity {W}
        8.11,                    !- Reference COP {W/W}
        4.44,                    !- Reference Leaving Chilled Water Temperature {C}
        12.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.02524,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.03785,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller McQuay PEH 819kW/8.11COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller McQuay PEH 819kW/8.11COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller McQuay PEH 819kW/8.11COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.09,                    !- Minimum Part Load Ratio
        1.05,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.09,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.05 | Maximum part load ratio
Real | PLRMinUnl | 0.09 | Minimum part unload ratio
Real | PLRMin | 0.09 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 12.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -819300 | Reference capacity (negative number) [W]
Real | COP_nominal | 8.11 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.02524 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.03785 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 4.44 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {7.392673E-01,4.328784E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.925176E-01,-1.908391E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.830681E-01,2.254147E-01,4... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_McQuay_PEH_819kW_8_11COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -819300, COP_nominal = 8.11, PLRMin = 0.09, PLRMinUnl = 0.09, PLRMax = 1.05, mEva_flow_nominal = 1000 * 0.02524, mCon_flow_nominal = 1000 * 0.03785, TEvaLvg_nominal = 273.15 + 4.44, TConEnt_nominal = 273.15 + 12.78, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {7.392673E-01,4.328784E-02,-4.529446E-03,1.525410E-02,-1.141458E-03,2.651124E-03}, EIRFunT = {5.925176E-01,-1.908391E-02,-1.852692E-03,4.051551E-02,-2.908719E-04,1.059047E-03}, EIRFunPLR = {2.830681E-01,2.254147E-01,4.916649E-01}, etaMotor = 1.0) "ElectricEIRChiller McQuay PEH 819kW/8.11COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_823kW_6_28COP_Vanes

ElectricEIRChiller Carrier 19XR 823kW/6.28COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 823kW/6.28COP/Vanes,  !- Name
        822900,                  !- Reference Capacity {W}
        6.28,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.03186,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.04744,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 823kW/6.28COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 823kW/6.28COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 823kW/6.28COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -822900 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.28 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.03186 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.04744 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {5.573150E-01,8.714616E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {8.029134E-01,2.171359E-02,2... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.965419E-01,4.689744E-01,2... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_823kW_6_28COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -822900, COP_nominal = 6.28, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.03186, mCon_flow_nominal = 1000 * 0.04744, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {5.573150E-01,8.714616E-02,-2.917582E-03,2.500000E-02,-8.861538E-04,-3.184615E-04}, EIRFunT = {8.029134E-01,2.171359E-02,2.388123E-04,-1.096173E-02,1.065277E-03,-2.057538E-03}, EIRFunPLR = {2.965419E-01,4.689744E-01,2.332341E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 823kW/6.28COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_869kW_5_57COP_VSD

ElectricEIRChiller Carrier 19XR 869kW/5.57COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 869kW/5.57COP/VSD,  !- Name
        868600,                  !- Reference Capacity {W}
        5.57,                    !- Reference COP {W/W}
        8.89,                    !- Reference Leaving Chilled Water Temperature {C}
        26.67,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.01754,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.02593,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 869kW/5.57COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 869kW/5.57COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 869kW/5.57COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.18,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.18,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.18 | Minimum part unload ratio
Real | PLRMin | 0.18 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.67 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -868600 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.57 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.01754 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.02593 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 8.89 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {5.406799E-01,1.253709E-01,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {3.943721E-01,1.079147E-01,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.501042E-01,-6.804336E-02,... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 7.22 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 26.67 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_869kW_5_57COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -868600, COP_nominal = 5.57, PLRMin = 0.18, PLRMinUnl = 0.18, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.01754, mCon_flow_nominal = 1000 * 0.02593, TEvaLvg_nominal = 273.15 + 8.89, TConEnt_nominal = 273.15 + 26.67, TEvaLvgMin = 273.15 + 7.22, TEvaLvgMax = 273.15 + 12.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 26.67, capFunT = {5.406799E-01,1.253709E-01,-8.025360E-03,-7.357554E-03,-4.477789E-04,2.140733E-03}, EIRFunT = {3.943721E-01,1.079147E-01,-8.912223E-03,-3.229487E-04,1.302402E-05,1.561862E-03}, EIRFunPLR = {1.501042E-01,-6.804336E-02,9.171460E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 869kW/5.57COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_897kW_7_23COP_VSD

ElectricEIRChiller Carrier 19XR 897kW/7.23COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 897kW/7.23COP/VSD,  !- Name
        896700,                  !- Reference Capacity {W}
        7.23,                    !- Reference COP {W/W}
        9.82,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.06782,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.0436,                  !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 897kW/7.23COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 897kW/7.23COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 897kW/7.23COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.04,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.04 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -896700 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.23 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.06782 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.0436 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 9.82 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {5.559679E-01,7.630860E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {6.511011E-01,4.948557E-02,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.036380E-01,-3.913200E-01,... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_897kW_7_23COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -896700, COP_nominal = 7.23, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.04, mEva_flow_nominal = 1000 * 0.06782, mCon_flow_nominal = 1000 * 0.0436, TEvaLvg_nominal = 273.15 + 9.82, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {5.559679E-01,7.630860E-02,-1.431181E-03,2.167593E-02,-6.233447E-04,-9.876498E-04}, EIRFunT = {6.511011E-01,4.948557E-02,-8.152733E-04,2.322946E-02,1.990802E-04,-2.669401E-03}, EIRFunPLR = {2.036380E-01,-3.913200E-01,1.187172E+00}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 897kW/7.23COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_897kW_6_50COP_Vanes

ElectricEIRChiller Carrier 19XR 897kW/6.50COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 897kW/6.50COP/Vanes,  !- Name
        896700,                  !- Reference Capacity {W}
        6.50,                    !- Reference COP {W/W}
        9.82,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.06782,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.04423,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 897kW/6.50COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 897kW/6.50COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 897kW/6.50COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -896700 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.50 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.06782 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.04423 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 9.82 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {7.009156E-01,2.151274E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {8.527749E-01,-4.336881E-03,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {3.323416E-01,2.561103E-01,4... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_897kW_6_50COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -896700, COP_nominal = 6.50, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.06782, mCon_flow_nominal = 1000 * 0.04423, TEvaLvg_nominal = 273.15 + 9.82, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {7.009156E-01,2.151274E-02,-6.029650E-04,1.864266E-02,-1.084545E-03,1.418575E-03}, EIRFunT = {8.527749E-01,-4.336881E-03,8.972177E-04,-1.888039E-03,8.648075E-04,-1.438797E-03}, EIRFunPLR = {3.323416E-01,2.561103E-01,4.106954E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 897kW/6.50COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YT_897kW_7_60COP_VSD

ElectricEIRChiller York YT 897kW/7.60COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YT 897kW/7.60COP/VSD,  !- Name
        896700,                  !- Reference Capacity {W}
        7.60,                    !- Reference COP {W/W}
        9.83,                    !- Reference Leaving Chilled Water Temperature {C}
        22.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.06782,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.05142,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YT 897kW/7.60COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YT 897kW/7.60COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YT 897kW/7.60COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 22.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -896700 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.60 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.06782 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.05142 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 9.83 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {5.699948E-01,2.961470E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.526128E-01,3.299472E-03,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {4.708628E-02,7.070062E-02,8... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YT_897kW_7_60COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -896700, COP_nominal = 7.60, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.06782, mCon_flow_nominal = 1000 * 0.05142, TEvaLvg_nominal = 273.15 + 9.83, TConEnt_nominal = 273.15 + 22.78, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {5.699948E-01,2.961470E-02,-1.064930E-03,3.062313E-02,-1.753205E-03,2.142105E-03}, EIRFunT = {5.526128E-01,3.299472E-03,-7.981925E-04,4.245710E-02,-3.533658E-04,-9.415137E-04}, EIRFunPLR = {4.708628E-02,7.070062E-02,8.802198E-01}, etaMotor = 1.0) "ElectricEIRChiller York YT 897kW/7.60COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YT_897kW_6_27COP_VSD

ElectricEIRChiller York YT 897kW/6.27COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YT 897kW/6.27COP/VSD,  !- Name
        896700,                  !- Reference Capacity {W}
        6.27,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        22.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.06782,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.05142,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YT 897kW/6.27COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YT 897kW/6.27COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YT 897kW/6.27COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 22.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -896700 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.27 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.06782 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.05142 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.197991E-01,1.568955E-01,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.530767E-01,-5.683068E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {9.836320E-02,-1.638320E-02,... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YT_897kW_6_27COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -896700, COP_nominal = 6.27, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.06782, mCon_flow_nominal = 1000 * 0.05142, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 22.78, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {1.197991E-01,1.568955E-01,-4.426242E-03,3.449640E-02,-8.163597E-04,-2.236230E-03}, EIRFunT = {5.530767E-01,-5.683068E-02,4.423475E-03,6.472411E-02,-7.378933E-04,-2.491202E-03}, EIRFunPLR = {9.836320E-02,-1.638320E-02,9.127289E-01}, etaMotor = 1.0) "ElectricEIRChiller York YT 897kW/6.27COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_897kW_6_23COP_VSD

ElectricEIRChiller Carrier 19XR 897kW/6.23COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 897kW/6.23COP/VSD,  !- Name
        896700,                  !- Reference Capacity {W}
        6.23,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.06782,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.04442,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 897kW/6.23COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 897kW/6.23COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 897kW/6.23COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -896700 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.23 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.06782 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.04442 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {8.862185E-01,3.144947E-02,2... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {8.606461E-01,-1.202294E-03,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.075556E-01,-2.126466E-01,... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_897kW_6_23COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -896700, COP_nominal = 6.23, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.06782, mCon_flow_nominal = 1000 * 0.04442, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {8.862185E-01,3.144947E-02,2.328997E-04,1.339712E-03,-2.923430E-04,2.320709E-04}, EIRFunT = {8.606461E-01,-1.202294E-03,9.398625E-04,2.983262E-03,4.119228E-04,-1.123884E-03}, EIRFunPLR = {2.075556E-01,-2.126466E-01,1.004182E+00}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 897kW/6.23COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_McQuay_PFH_932kW_5_09COP_Vanes

ElectricEIRChiller McQuay PFH 932kW/5.09COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller McQuay PFH 932kW/5.09COP/Vanes,  !- Name
        931900,                  !- Reference Capacity {W}
        5.09,                    !- Reference COP {W/W}
        4.44,                    !- Reference Leaving Chilled Water Temperature {C}
        26.11,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.03785,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.04732,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller McQuay PFH 932kW/5.09COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller McQuay PFH 932kW/5.09COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller McQuay PFH 932kW/5.09COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.09,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.09,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.09 | Minimum part unload ratio
Real | PLRMin | 0.09 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.11 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -931900 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.09 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.03785 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.04732 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 4.44 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.182278E+00,3.259490E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {6.053491E-01,-1.089778E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {6.823245E-02,6.672421E-01,2... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 3.33 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 7.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_McQuay_PFH_932kW_5_09COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -931900, COP_nominal = 5.09, PLRMin = 0.09, PLRMinUnl = 0.09, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.03785, mCon_flow_nominal = 1000 * 0.04732, TEvaLvg_nominal = 273.15 + 4.44, TConEnt_nominal = 273.15 + 26.11, TEvaLvgMin = 273.15 + 3.33, TEvaLvgMax = 273.15 + 7.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {1.182278E+00,3.259490E-02,-3.904288E-03,4.579721E-03,-1.028178E-03,2.855063E-03}, EIRFunT = {6.053491E-01,-1.089778E-02,-1.511327E-03,1.902687E-02,-1.910750E-04,9.008184E-04}, EIRFunPLR = {6.823245E-02,6.672421E-01,2.654211E-01}, etaMotor = 1.0) "ElectricEIRChiller McQuay PFH 932kW/5.09COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YT_960kW_4_64COP_Vanes

ElectricEIRChiller York YT 960kW/4.64COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YT 960kW/4.64COP/Vanes,  !- Name
        960000,                  !- Reference Capacity {W}
        4.64,                    !- Reference COP {W/W}
        4.44,                    !- Reference Leaving Chilled Water Temperature {C}
        26.11,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.03785,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.04732,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YT 960kW/4.64COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YT 960kW/4.64COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YT 960kW/4.64COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.09,                    !- Minimum Part Load Ratio
        1.09,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.09,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.09 | Maximum part load ratio
Real | PLRMinUnl | 0.09 | Minimum part unload ratio
Real | PLRMin | 0.09 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.11 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -960000 | Reference capacity (negative number) [W]
Real | COP_nominal | 4.64 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.03785 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.04732 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 4.44 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {-2.278537E-01,4.055945E-01,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.735924E-01,2.270414E-02,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.737941E-01,3.141127E-01,4... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 3.33 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 7.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YT_960kW_4_64COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -960000, COP_nominal = 4.64, PLRMin = 0.09, PLRMinUnl = 0.09, PLRMax = 1.09, mEva_flow_nominal = 1000 * 0.03785, mCon_flow_nominal = 1000 * 0.04732, TEvaLvg_nominal = 273.15 + 4.44, TConEnt_nominal = 273.15 + 26.11, TEvaLvgMin = 273.15 + 3.33, TEvaLvgMax = 273.15 + 7.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {-2.278537E-01,4.055945E-01,-3.246694E-02,3.788230E-03,-2.236584E-04,6.715520E-04}, EIRFunT = {5.735924E-01,2.270414E-02,-3.331832E-03,6.025574E-03,3.245033E-04,3.229690E-05}, EIRFunPLR = {2.737941E-01,3.141127E-01,4.113671E-01}, etaMotor = 1.0) "ElectricEIRChiller York YT 960kW/4.64COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YT_1023kW_5_81COP_Vanes

ElectricEIRChiller York YT 1023kW/5.81COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YT 1023kW/5.81COP/Vanes,  !- Name
        1023300,                 !- Reference Capacity {W}
        5.81,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        29.44,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.02366,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.04732,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YT 1023kW/5.81COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YT 1023kW/5.81COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YT 1023kW/5.81COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.09,                    !- Minimum Part Load Ratio
        1.06,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.09,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.06 | Maximum part load ratio
Real | PLRMinUnl | 0.09 | Minimum part unload ratio
Real | PLRMin | 0.09 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 29.44 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1023300 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.81 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.02366 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.04732 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {2.571195E-01,-1.571421E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.254964E-01,-1.972389E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.368399E-01,3.286421E-01,4... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 35.00 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YT_1023kW_5_81COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1023300, COP_nominal = 5.81, PLRMin = 0.09, PLRMinUnl = 0.09, PLRMax = 1.06, mEva_flow_nominal = 1000 * 0.02366, mCon_flow_nominal = 1000 * 0.04732, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 29.44, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 35.00, capFunT = {2.571195E-01,-1.571421E-02,-3.041761E-03,8.106512E-02,-2.568598E-03,4.247073E-03}, EIRFunT = {5.254964E-01,-1.972389E-02,3.441072E-04,1.651466E-02,2.005198E-04,-3.193246E-04}, EIRFunPLR = {2.368399E-01,3.286421E-01,4.344939E-01}, etaMotor = 1.0) "ElectricEIRChiller York YT 1023kW/5.81COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_McQuay_PEH_1030kW_8_58COP_Vanes

ElectricEIRChiller McQuay PEH 1030kW/8.58COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller McQuay PEH 1030kW/8.58COP/Vanes,  !- Name
        1030300,                 !- Reference Capacity {W}
        8.58,                    !- Reference COP {W/W}
        6.11,                    !- Reference Leaving Chilled Water Temperature {C}
        12.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.02378,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.03407,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller McQuay PEH 1030kW/8.58COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller McQuay PEH 1030kW/8.58COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller McQuay PEH 1030kW/8.58COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.08,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.08,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.08 | Minimum part unload ratio
Real | PLRMin | 0.08 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 12.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1030300 | Reference capacity (negative number) [W]
Real | COP_nominal | 8.58 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.02378 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.03407 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.11 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {7.736028E-01,5.571395E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {7.125878E-01,1.388940E-02,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {3.215320E-01,-9.188416E-03,... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 6.11 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_McQuay_PEH_1030kW_8_58COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1030300, COP_nominal = 8.58, PLRMin = 0.08, PLRMinUnl = 0.08, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.02378, mCon_flow_nominal = 1000 * 0.03407, TEvaLvg_nominal = 273.15 + 6.11, TConEnt_nominal = 273.15 + 12.78, TEvaLvgMin = 273.15 + 6.11, TEvaLvgMax = 273.15 + 12.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {7.736028E-01,5.571395E-02,-3.058312E-03,-1.789007E-04,-9.808878E-04,2.123462E-03}, EIRFunT = {7.125878E-01,1.388940E-02,-2.473407E-03,2.096719E-02,-1.566098E-04,6.035460E-04}, EIRFunPLR = {3.215320E-01,-9.188416E-03,6.881582E-01}, etaMotor = 1.0) "ElectricEIRChiller McQuay PEH 1030kW/8.58COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YT_1048kW_6_06COP_Vanes

ElectricEIRChiller York YT 1048kW/6.06COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YT 1048kW/6.06COP/Vanes,  !- Name
        1047900,                 !- Reference Capacity {W}
        6.06,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        29.44,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.04542,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.05678,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YT 1048kW/6.06COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YT 1048kW/6.06COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YT 1048kW/6.06COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.06,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.06 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 29.44 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1047900 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.06 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.04542 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.05678 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {7.238221E-01,1.747548E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {7.255594E-01,-3.502968E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.543796E-01,7.276121E-01,1... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 15.56 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 35.00 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YT_1048kW_6_06COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1047900, COP_nominal = 6.06, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.06, mEva_flow_nominal = 1000 * 0.04542, mCon_flow_nominal = 1000 * 0.05678, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 29.44, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 15.56, TConEntMax = 273.15 + 35.00, capFunT = {7.238221E-01,1.747548E-02,-4.524718E-03,2.138468E-02,-9.342801E-04,2.515069E-03}, EIRFunT = {7.255594E-01,-3.502968E-02,2.213476E-03,3.925410E-03,5.538176E-04,-8.638012E-04}, EIRFunPLR = {1.543796E-01,7.276121E-01,1.162393E-01}, etaMotor = 1.0) "ElectricEIRChiller York YT 1048kW/6.06COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YT_1055kW_5_96COP_Vanes

ElectricEIRChiller York YT 1055kW/5.96COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YT 1055kW/5.96COP/Vanes,  !- Name
        1055000,                 !- Reference Capacity {W}
        5.96,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        29.44,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.02839,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.05678,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YT 1055kW/5.96COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YT 1055kW/5.96COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YT 1055kW/5.96COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.05,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.05 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 29.44 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1055000 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.96 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.02839 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.05678 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.785912E-01,-5.900023E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.245110E-01,-2.850126E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.619878E-01,2.393605E-01,4... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 35.00 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YT_1055kW_5_96COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1055000, COP_nominal = 5.96, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.05, mEva_flow_nominal = 1000 * 0.02839, mCon_flow_nominal = 1000 * 0.05678, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 29.44, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 35.00, capFunT = {1.785912E-01,-5.900023E-02,-5.946963E-04,9.297889E-02,-2.841024E-03,4.974221E-03}, EIRFunT = {5.245110E-01,-2.850126E-02,8.034720E-04,1.893133E-02,1.151629E-04,-9.340642E-05}, EIRFunPLR = {2.619878E-01,2.393605E-01,4.988306E-01}, etaMotor = 1.0) "ElectricEIRChiller York YT 1055kW/5.96COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_1076kW_5_52COP_Vanes

ElectricEIRChiller Carrier 19XR 1076kW/5.52COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 1076kW/5.52COP/Vanes,  !- Name
        1076100,                 !- Reference Capacity {W}
        5.52,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        24.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.03186,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.04744,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 1076kW/5.52COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1076kW/5.52COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1076kW/5.52COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 24.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1076100 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.52 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.03186 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.04744 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {9.187704E-01,4.509452E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {7.511044E-01,2.415573E-02,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.315760E-01,-3.004087E-02,... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 24.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_1076kW_5_52COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1076100, COP_nominal = 5.52, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.03186, mCon_flow_nominal = 1000 * 0.04744, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 24.89, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 24.89, capFunT = {9.187704E-01,4.509452E-02,-5.119187E-03,-2.095629E-04,-6.432511E-04,2.791545E-03}, EIRFunT = {7.511044E-01,2.415573E-02,-5.310959E-03,-1.073812E-03,1.189538E-04,1.604476E-03}, EIRFunPLR = {1.315760E-01,-3.004087E-02,8.967180E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 1076kW/5.52COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_CVHE_1080kW_7_39COP_Vanes

ElectricEIRChiller Trane CVHE 1080kW/7.39COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane CVHE 1080kW/7.39COP/Vanes,  !- Name
        1079600,                 !- Reference Capacity {W}
        7.39,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        23.61,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.03186,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.06416,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane CVHE 1080kW/7.39COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHE 1080kW/7.39COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHE 1080kW/7.39COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.05,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.05 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.61 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1079600 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.39 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.03186 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.06416 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {4.365583E-01,-3.677215E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {3.608716E-01,-5.637178E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.789841E-01,2.976513E-01,5... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 16.24 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.61 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_CVHE_1080kW_7_39COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1079600, COP_nominal = 7.39, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.05, mEva_flow_nominal = 1000 * 0.03186, mCon_flow_nominal = 1000 * 0.06416, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 23.61, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 16.24, TConEntMax = 273.15 + 23.61, capFunT = {4.365583E-01,-3.677215E-02,-2.779781E-03,6.063060E-02,-2.290704E-03,5.115883E-03}, EIRFunT = {3.608716E-01,-5.637178E-02,-3.428415E-04,4.230087E-02,-4.391632E-04,1.517182E-03}, EIRFunPLR = {1.789841E-01,2.976513E-01,5.243235E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane CVHE 1080kW/7.39COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YT_1090kW_7_57COP_VSD

ElectricEIRChiller York YT 1090kW/7.57COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YT 1090kW/7.57COP/VSD,  !- Name
        1090100,                 !- Reference Capacity {W}
        7.57,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        22.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.06782,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.05142,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YT 1090kW/7.57COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YT 1090kW/7.57COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YT 1090kW/7.57COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.14,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.14,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.14 | Minimum part unload ratio
Real | PLRMin | 0.14 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 22.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1090100 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.57 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.06782 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.05142 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {6.769028E-01,5.711844E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {9.241019E-01,-4.961574E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.431969E-01,-4.920686E-01,... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YT_1090kW_7_57COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1090100, COP_nominal = 7.57, PLRMin = 0.14, PLRMinUnl = 0.14, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.06782, mCon_flow_nominal = 1000 * 0.05142, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 22.78, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {6.769028E-01,5.711844E-02,-6.072310E-04,1.656541E-02,-8.087831E-04,2.303904E-04}, EIRFunT = {9.241019E-01,-4.961574E-02,1.291675E-04,3.299013E-02,-6.769477E-04,1.692815E-03}, EIRFunPLR = {1.431969E-01,-4.920686E-01,1.341333E+00}, etaMotor = 1.0) "ElectricEIRChiller York YT 1090kW/7.57COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_McQuay_PEH_1104kW_8_00COP_Vanes

ElectricEIRChiller McQuay PEH 1104kW/8.00COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller McQuay PEH 1104kW/8.00COP/Vanes,  !- Name
        1104200,                 !- Reference Capacity {W}
        8.00,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        12.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.02423,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.03028,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller McQuay PEH 1104kW/8.00COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller McQuay PEH 1104kW/8.00COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller McQuay PEH 1104kW/8.00COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.08,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.08,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.08 | Minimum part unload ratio
Real | PLRMin | 0.08 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 12.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1104200 | Reference capacity (negative number) [W]
Real | COP_nominal | 8.00 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.02423 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.03028 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {8.210185E-01,4.386152E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {8.655242E-01,-3.808337E-04,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {3.091150E-01,-1.089639E-02,... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 6.67 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.22 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_McQuay_PEH_1104kW_8_00COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1104200, COP_nominal = 8.00, PLRMin = 0.08, PLRMinUnl = 0.08, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.02423, mCon_flow_nominal = 1000 * 0.03028, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 12.78, TEvaLvgMin = 273.15 + 6.67, TEvaLvgMax = 273.15 + 12.22, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {8.210185E-01,4.386152E-02,-1.521829E-03,-4.314921E-03,-7.251667E-04,1.497681E-03}, EIRFunT = {8.655242E-01,-3.808337E-04,-1.320050E-03,1.137834E-02,-4.095120E-05,6.531102E-04}, EIRFunPLR = {3.091150E-01,-1.089639E-02,7.022967E-01}, etaMotor = 1.0) "ElectricEIRChiller McQuay PEH 1104kW/8.00COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_CVHE_1125kW_4_89COP_Vanes

ElectricEIRChiller Trane CVHE 1125kW/4.89COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane CVHE 1125kW/4.89COP/Vanes,  !- Name
        1125300,                 !- Reference Capacity {W}
        4.89,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.02776,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.02618,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane CVHE 1125kW/4.89COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHE 1125kW/4.89COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHE 1125kW/4.89COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.01,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.01 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1125300 | Reference capacity (negative number) [W]
Real | COP_nominal | 4.89 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.02776 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.02618 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {6.151549E-01,-1.181250E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.810580E-01,-4.344257E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.807198E-01,-1.469686E-01,... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 15.56 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_CVHE_1125kW_4_89COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1125300, COP_nominal = 4.89, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.01, mEva_flow_nominal = 1000 * 0.02776, mCon_flow_nominal = 1000 * 0.02618, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 15.56, TConEntMax = 273.15 + 23.89, capFunT = {6.151549E-01,-1.181250E-02,-1.491630E-03,3.326625E-02,-9.315000E-04,1.771875E-03}, EIRFunT = {5.810580E-01,-4.344257E-02,-5.369108E-04,2.844405E-02,-1.609390E-04,7.004346E-04}, EIRFunPLR = {1.807198E-01,-1.469686E-01,9.658417E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane CVHE 1125kW/4.89COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YT_1125kW_7_92COP_VSD

ElectricEIRChiller York YT 1125kW/7.92COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YT 1125kW/7.92COP/VSD,  !- Name
        1125300,                 !- Reference Capacity {W}
        7.92,                    !- Reference COP {W/W}
        6.11,                    !- Reference Leaving Chilled Water Temperature {C}
        12.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.03243,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.05173,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YT 1125kW/7.92COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YT 1125kW/7.92COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YT 1125kW/7.92COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.09,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.09,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.09 | Minimum part unload ratio
Real | PLRMin | 0.09 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 12.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1125300 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.92 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.03243 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.05173 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.11 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.034212E-01,2.327078E-03,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {6.542286E-01,-2.451604E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.147453E-01,4.231235E-02,8... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 6.11 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YT_1125kW_7_92COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1125300, COP_nominal = 7.92, PLRMin = 0.09, PLRMinUnl = 0.09, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.03243, mCon_flow_nominal = 1000 * 0.05173, TEvaLvg_nominal = 273.15 + 6.11, TConEnt_nominal = 273.15 + 12.78, TEvaLvgMin = 273.15 + 6.11, TEvaLvgMax = 273.15 + 12.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {1.034212E-01,2.327078E-03,-9.117035E-04,9.104793E-02,-2.678967E-03,2.274649E-03}, EIRFunT = {6.542286E-01,-2.451604E-02,1.253508E-03,4.216477E-02,1.404867E-04,-1.508780E-03}, EIRFunPLR = {1.147453E-01,4.231235E-02,8.419681E-01}, etaMotor = 1.0) "ElectricEIRChiller York YT 1125kW/7.92COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_CVHE_1129kW_7_19COP_Vanes

ElectricEIRChiller Trane CVHE 1129kW/7.19COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane CVHE 1129kW/7.19COP/Vanes,  !- Name
        1128800,                 !- Reference Capacity {W}
        7.19,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.02776,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.05142,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane CVHE 1129kW/7.19COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHE 1129kW/7.19COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHE 1129kW/7.19COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.15,                    !- Minimum Part Load Ratio
        1.06,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.15,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.06 | Maximum part load ratio
Real | PLRMinUnl | 0.15 | Minimum part unload ratio
Real | PLRMin | 0.15 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1128800 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.19 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.02776 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.05142 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {3.922479E-01,-4.388411E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {3.742142E-01,-5.536709E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.693841E-01,2.475201E-01,5... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 15.56 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_CVHE_1129kW_7_19COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1128800, COP_nominal = 7.19, PLRMin = 0.15, PLRMinUnl = 0.15, PLRMax = 1.06, mEva_flow_nominal = 1000 * 0.02776, mCon_flow_nominal = 1000 * 0.05142, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 15.56, TConEntMax = 273.15 + 23.89, capFunT = {3.922479E-01,-4.388411E-02,-2.748665E-03,6.894954E-02,-2.563738E-03,5.420187E-03}, EIRFunT = {3.742142E-01,-5.536709E-02,-8.199663E-04,4.655032E-02,-7.312591E-04,1.887184E-03}, EIRFunPLR = {1.693841E-01,2.475201E-01,5.836059E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane CVHE 1129kW/7.19COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_1143kW_6_57COP_VSD

ElectricEIRChiller Carrier 19XR 1143kW/6.57COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 1143kW/6.57COP/VSD,  !- Name
        1142900,                 !- Reference Capacity {W}
        6.57,                    !- Reference COP {W/W}
        10.00,                   !- Reference Leaving Chilled Water Temperature {C}
        26.67,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.02593,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.05142,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 1143kW/6.57COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1143kW/6.57COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1143kW/6.57COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.67 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1142900 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.57 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.02593 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.05142 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 10.00 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {7.939538E-01,4.096493E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {9.475580E-01,-1.187942E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.408822E-01,-1.578153E-01,... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 7.22 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 26.67 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_1143kW_6_57COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1142900, COP_nominal = 6.57, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.02593, mCon_flow_nominal = 1000 * 0.05142, TEvaLvg_nominal = 273.15 + 10.00, TConEnt_nominal = 273.15 + 26.67, TEvaLvgMin = 273.15 + 7.22, TEvaLvgMax = 273.15 + 12.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 26.67, capFunT = {7.939538E-01,4.096493E-02,-1.419397E-03,-1.639813E-03,-5.220497E-04,1.348786E-03}, EIRFunT = {9.475580E-01,-1.187942E-02,8.799326E-05,2.250775E-04,1.815775E-04,2.178409E-04}, EIRFunPLR = {1.408822E-01,-1.578153E-01,1.014316E+00}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 1143kW/6.57COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_1157kW_5_62COP_VSD

ElectricEIRChiller Carrier 19XR 1157kW/5.62COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 1157kW/5.62COP/VSD,  !- Name
        1156900,                 !- Reference Capacity {W}
        5.62,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        21.11,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.02801,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.03186,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 1157kW/5.62COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1157kW/5.62COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1157kW/5.62COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.19,                    !- Minimum Part Load Ratio
        1.01,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.19,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.01 | Maximum part load ratio
Real | PLRMinUnl | 0.19 | Minimum part unload ratio
Real | PLRMin | 0.19 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 21.11 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1156900 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.62 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.02801 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.03186 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.076248E+00,5.436724E-03,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {1.075567E+00,-3.893571E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.608589E-01,-2.058215E-01,... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 11.25 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_1157kW_5_62COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1156900, COP_nominal = 5.62, PLRMin = 0.19, PLRMinUnl = 0.19, PLRMax = 1.01, mEva_flow_nominal = 1000 * 0.02801, mCon_flow_nominal = 1000 * 0.03186, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 21.11, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 11.25, TConEntMax = 273.15 + 23.89, capFunT = {1.076248E+00,5.436724E-03,-3.893302E-04,-4.353310E-03,-2.402031E-04,8.409080E-04}, EIRFunT = {1.075567E+00,-3.893571E-02,1.082499E-03,-5.782829E-03,6.574492E-04,-5.302886E-04}, EIRFunPLR = {1.608589E-01,-2.058215E-01,1.043133E+00}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 1157kW/5.62COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_1196kW_6_50COP_Vanes

ElectricEIRChiller Carrier 19XR 1196kW/6.50COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 1196kW/6.50COP/Vanes,  !- Name
        1195600,                 !- Reference Capacity {W}
        6.50,                    !- Reference COP {W/W}
        7.22,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.03426,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.04252,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 1196kW/6.50COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1196kW/6.50COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1196kW/6.50COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1195600 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.50 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.03426 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.04252 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 7.22 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.126801E+00,-4.220591E-03,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {9.514432E-01,-2.252147E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.724491E-01,2.710369E-01,4... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 6.67 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.22 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_1196kW_6_50COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1195600, COP_nominal = 6.50, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.03426, mCon_flow_nominal = 1000 * 0.04252, TEvaLvg_nominal = 273.15 + 7.22, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 6.67, TEvaLvgMax = 273.15 + 12.22, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {1.126801E+00,-4.220591E-03,-2.002964E-03,7.360880E-03,-1.156890E-03,3.064875E-03}, EIRFunT = {9.514432E-01,-2.252147E-02,-1.062456E-05,-1.383194E-04,3.914644E-04,8.126485E-05}, EIRFunPLR = {2.724491E-01,2.710369E-01,4.552356E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 1196kW/6.50COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_1213kW_7_78COP_Vanes

ElectricEIRChiller Carrier 19XR 1213kW/7.78COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 1213kW/7.78COP/Vanes,  !- Name
        1213200,                 !- Reference Capacity {W}
        7.78,                    !- Reference COP {W/W}
        6.11,                    !- Reference Leaving Chilled Water Temperature {C}
        12.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.03243,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.04782,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 1213kW/7.78COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1213kW/7.78COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1213kW/7.78COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.17,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.17,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.17 | Minimum part unload ratio
Real | PLRMin | 0.17 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 12.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1213200 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.78 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.03243 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.04782 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.11 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {9.070437E-01,-7.437456E-03,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {1.002142E+00,-2.505239E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.847744E-01,4.027863E-01,3... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 6.11 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_1213kW_7_78COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1213200, COP_nominal = 7.78, PLRMin = 0.17, PLRMinUnl = 0.17, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.03243, mCon_flow_nominal = 1000 * 0.04782, TEvaLvg_nominal = 273.15 + 6.11, TConEnt_nominal = 273.15 + 12.78, TEvaLvgMin = 273.15 + 6.11, TEvaLvgMax = 273.15 + 12.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {9.070437E-01,-7.437456E-03,-9.695325E-04,1.529092E-02,-1.069664E-03,1.994583E-03}, EIRFunT = {1.002142E+00,-2.505239E-02,5.169707E-04,6.321862E-03,5.116807E-04,-4.794244E-04}, EIRFunPLR = {2.847744E-01,4.027863E-01,3.114896E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 1213kW/7.78COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_McQuay_PEH_1231kW_6_18COP_Vanes

ElectricEIRChiller McQuay PEH 1231kW/6.18COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller McQuay PEH 1231kW/6.18COP/Vanes,  !- Name
        1230800,                 !- Reference Capacity {W}
        6.18,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        22.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.03533,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.0511,                  !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller McQuay PEH 1231kW/6.18COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller McQuay PEH 1231kW/6.18COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller McQuay PEH 1231kW/6.18COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 22.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1230800 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.18 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.03533 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.0511 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.152795E+00,9.770474E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {8.067591E-01,1.868314E-02,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.117054E-01,4.263662E-01,3... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_McQuay_PEH_1231kW_6_18COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1230800, COP_nominal = 6.18, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.03533, mCon_flow_nominal = 1000 * 0.0511, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 22.78, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {1.152795E+00,9.770474E-02,-6.719705E-03,-2.123401E-02,-3.641998E-04,1.473439E-03}, EIRFunT = {8.067591E-01,1.868314E-02,-5.569088E-03,-4.309148E-03,1.373034E-04,2.394081E-03}, EIRFunPLR = {2.117054E-01,4.263662E-01,3.614654E-01}, etaMotor = 1.0) "ElectricEIRChiller McQuay PEH 1231kW/6.18COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_1234kW_5_39COP_VSD

ElectricEIRChiller Carrier 19XR 1234kW/5.39COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 1234kW/5.39COP/VSD,  !- Name
        1234300,                 !- Reference Capacity {W}
        5.39,                    !- Reference COP {W/W}
        8.89,                    !- Reference Leaving Chilled Water Temperature {C}
        26.67,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.02593,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.03861,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 1234kW/5.39COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1234kW/5.39COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1234kW/5.39COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.19,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.19,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.19 | Minimum part unload ratio
Real | PLRMin | 0.19 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.67 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1234300 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.39 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.02593 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.03861 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 8.89 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {5.905815E-01,1.190927E-01,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {3.771659E-01,1.144965E-01,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.495681E-01,-1.449639E-01,... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 7.22 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 26.67 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_1234kW_5_39COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1234300, COP_nominal = 5.39, PLRMin = 0.19, PLRMinUnl = 0.19, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.02593, mCon_flow_nominal = 1000 * 0.03861, TEvaLvg_nominal = 273.15 + 8.89, TConEnt_nominal = 273.15 + 26.67, TEvaLvgMin = 273.15 + 7.22, TEvaLvgMax = 273.15 + 12.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 26.67, capFunT = {5.905815E-01,1.190927E-01,-6.727309E-03,-9.580836E-03,-3.034704E-04,1.540686E-03}, EIRFunT = {3.771659E-01,1.144965E-01,-8.186893E-03,-3.372584E-03,1.689440E-04,1.008523E-03}, EIRFunPLR = {1.495681E-01,-1.449639E-01,9.941070E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 1234kW/5.39COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_1259kW_6_26COP_Vanes

ElectricEIRChiller Carrier 19XR 1259kW/6.26COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 1259kW/6.26COP/Vanes,  !- Name
        1258900,                 !- Reference Capacity {W}
        6.26,                    !- Reference COP {W/W}
        8.89,                    !- Reference Leaving Chilled Water Temperature {C}
        26.67,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.02593,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.03823,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 1259kW/6.26COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1259kW/6.26COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1259kW/6.26COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.18,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.18,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.18 | Minimum part unload ratio
Real | PLRMin | 0.18 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.67 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1258900 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.26 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.02593 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.03823 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 8.89 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.082071E+00,3.200888E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {7.582035E-01,6.896017E-03,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.226232E-01,5.199282E-01,2... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 7.22 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 26.67 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_1259kW_6_26COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1258900, COP_nominal = 6.26, PLRMin = 0.18, PLRMinUnl = 0.18, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.02593, mCon_flow_nominal = 1000 * 0.03823, TEvaLvg_nominal = 273.15 + 8.89, TConEnt_nominal = 273.15 + 26.67, TEvaLvgMin = 273.15 + 7.22, TEvaLvgMax = 273.15 + 12.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 26.67, capFunT = {1.082071E+00,3.200888E-02,-3.994780E-03,-5.789604E-03,-8.238938E-04,2.933539E-03}, EIRFunT = {7.582035E-01,6.896017E-03,-1.491911E-03,2.249459E-03,3.908697E-04,-1.735265E-04}, EIRFunPLR = {2.226232E-01,5.199282E-01,2.578470E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 1259kW/6.26COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YK_1259kW_6_45COP_Vanes

ElectricEIRChiller York YK 1259kW/6.45COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YK 1259kW/6.45COP/Vanes,  !- Name
        1258900,                 !- Reference Capacity {W}
        6.45,                    !- Reference COP {W/W}
        8.89,                    !- Reference Leaving Chilled Water Temperature {C}
        26.67,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.02631,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.06246,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YK 1259kW/6.45COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YK 1259kW/6.45COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YK 1259kW/6.45COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.18,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.18,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.18 | Minimum part unload ratio
Real | PLRMin | 0.18 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.67 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1258900 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.45 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.02631 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.06246 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 8.89 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {9.609200E-01,7.223733E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {8.991536E-01,6.305932E-03,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.014593E-01,6.216537E-01,2... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 7.22 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 26.67 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YK_1259kW_6_45COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1258900, COP_nominal = 6.45, PLRMin = 0.18, PLRMinUnl = 0.18, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.02631, mCon_flow_nominal = 1000 * 0.06246, TEvaLvg_nominal = 273.15 + 8.89, TConEnt_nominal = 273.15 + 26.67, TEvaLvgMin = 273.15 + 7.22, TEvaLvgMax = 273.15 + 12.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 26.67, capFunT = {9.609200E-01,7.223733E-02,-1.693471E-03,2.543722E-03,-6.415570E-04,-3.028540E-04}, EIRFunT = {8.991536E-01,6.305932E-03,-3.756374E-04,-1.952076E-02,1.381302E-03,-1.615004E-03}, EIRFunPLR = {1.014593E-01,6.216537E-01,2.780213E-01}, etaMotor = 1.0) "ElectricEIRChiller York YK 1259kW/6.45COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YT_1266kW_4_39COP_Vanes

ElectricEIRChiller York YT 1266kW/4.39COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YT 1266kW/4.39COP/Vanes,  !- Name
        1266000,                 !- Reference Capacity {W}
        4.39,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        35.00,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.03533,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.05773,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YT 1266kW/4.39COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YT 1266kW/4.39COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YT 1266kW/4.39COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.11,                    !- Minimum Part Load Ratio
        1.05,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.11,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.05 | Maximum part load ratio
Real | PLRMinUnl | 0.11 | Minimum part unload ratio
Real | PLRMin | 0.11 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 35.00 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1266000 | Reference capacity (negative number) [W]
Real | COP_nominal | 4.39 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.03533 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.05773 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.285663E-01,-2.860032E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {8.284925E-02,4.206167E-02,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {7.326942E-01,-7.962527E-01,... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 35.00 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YT_1266kW_4_39COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1266000, COP_nominal = 4.39, PLRMin = 0.11, PLRMinUnl = 0.11, PLRMax = 1.05, mEva_flow_nominal = 1000 * 0.03533, mCon_flow_nominal = 1000 * 0.05773, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 35.00, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 35.00, capFunT = {1.285663E-01,-2.860032E-02,-1.369319E-03,6.676366E-02,-1.510647E-03,2.947167E-03}, EIRFunT = {8.284925E-02,4.206167E-02,-5.254555E-03,1.964407E-02,1.070646E-04,2.298241E-04}, EIRFunPLR = {7.326942E-01,-7.962527E-01,1.059148E+00}, etaMotor = 1.0) "ElectricEIRChiller York YT 1266kW/4.39COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_1284kW_6_20COP_Vanes

ElectricEIRChiller Carrier 19XR 1284kW/6.20COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 1284kW/6.20COP/Vanes,  !- Name
        1283500,                 !- Reference Capacity {W}
        6.20,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        22.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.03684,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.05337,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 1284kW/6.20COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1284kW/6.20COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1284kW/6.20COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 22.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1283500 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.20 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.03684 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.05337 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.119245E+00,-1.524417E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {7.815645E-01,-2.448971E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.324812E-01,7.690691E-01,-... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_1284kW_6_20COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1283500, COP_nominal = 6.20, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.03684, mCon_flow_nominal = 1000 * 0.05337, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 22.78, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {1.119245E+00,-1.524417E-02,-1.074186E-03,-1.260169E-03,-4.380237E-04,2.027779E-03}, EIRFunT = {7.815645E-01,-2.448971E-02,1.644370E-03,5.564580E-03,5.800428E-04,-1.086993E-03}, EIRFunPLR = {2.324812E-01,7.690691E-01,-6.532223E-04}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 1284kW/6.20COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_1294kW_7_61COP_Vanes

ElectricEIRChiller Carrier 19XR 1294kW/7.61COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 1294kW/7.61COP/Vanes,  !- Name
        1294100,                 !- Reference Capacity {W}
        7.61,                    !- Reference COP {W/W}
        6.11,                    !- Reference Leaving Chilled Water Temperature {C}
        12.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.03243,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.04732,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 1294kW/7.61COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1294kW/7.61COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1294kW/7.61COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.16,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.16,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.16 | Minimum part unload ratio
Real | PLRMin | 0.16 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 12.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1294100 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.61 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.03243 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.04732 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.11 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {9.274222E-01,1.278683E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {1.085249E+00,-9.441252E-04,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {9.344563E-02,3.993002E-01,5... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 6.11 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_1294kW_7_61COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1294100, COP_nominal = 7.61, PLRMin = 0.16, PLRMinUnl = 0.16, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.03243, mCon_flow_nominal = 1000 * 0.04732, TEvaLvg_nominal = 273.15 + 6.11, TConEnt_nominal = 273.15 + 12.78, TEvaLvgMin = 273.15 + 6.11, TEvaLvgMax = 273.15 + 12.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {9.274222E-01,1.278683E-02,-1.621880E-03,2.816339E-03,-7.658105E-04,1.881968E-03}, EIRFunT = {1.085249E+00,-9.441252E-04,-2.505100E-03,-8.724367E-03,4.164780E-04,8.473746E-04}, EIRFunPLR = {9.344563E-02,3.993002E-01,5.087169E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 1294kW/7.61COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_CVHE_1329kW_5_38COP_Vanes

ElectricEIRChiller Trane CVHE 1329kW/5.38COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane CVHE 1329kW/5.38COP/Vanes,  !- Name
        1329300,                 !- Reference Capacity {W}
        5.38,                    !- Reference COP {W/W}
        6.11,                    !- Reference Leaving Chilled Water Temperature {C}
        29.44,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.04732,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.07098,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane CVHE 1329kW/5.38COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHE 1329kW/5.38COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHE 1329kW/5.38COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.29,                    !- Minimum Part Load Ratio
        1.05,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.29,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.05 | Maximum part load ratio
Real | PLRMinUnl | 0.29 | Minimum part unload ratio
Real | PLRMin | 0.29 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 29.44 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1329300 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.38 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.04732 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.07098 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.11 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {5.339754E-01,1.016009E-01,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {8.074052E-01,3.355495E-02,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {4.079777E-02,1.174456E+00,-... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 6.11 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 21.11 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_CVHE_1329kW_5_38COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1329300, COP_nominal = 5.38, PLRMin = 0.29, PLRMinUnl = 0.29, PLRMax = 1.05, mEva_flow_nominal = 1000 * 0.04732, mCon_flow_nominal = 1000 * 0.07098, TEvaLvg_nominal = 273.15 + 6.11, TConEnt_nominal = 273.15 + 29.44, TEvaLvgMin = 273.15 + 6.11, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 21.11, TConEntMax = 273.15 + 29.44, capFunT = {5.339754E-01,1.016009E-01,-3.979592E-03,1.261254E-02,-4.666667E-04,-8.351648E-05}, EIRFunT = {8.074052E-01,3.355495E-02,-1.549617E-03,-7.142554E-03,5.056363E-04,-7.547786E-04}, EIRFunPLR = {4.079777E-02,1.174456E+00,-2.212711E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane CVHE 1329kW/5.38COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_1350kW_7_90COP_VSD

ElectricEIRChiller Carrier 19XR 1350kW/7.90COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 1350kW/7.90COP/VSD,  !- Name
        1350400,                 !- Reference Capacity {W}
        7.90,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        12.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.03684,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.05337,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 1350kW/7.90COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1350kW/7.90COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1350kW/7.90COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.19,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.19,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.19 | Minimum part unload ratio
Real | PLRMin | 0.19 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 12.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1350400 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.90 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.03684 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.05337 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.063866E+00,-1.448990E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {9.953536E-01,-3.118863E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {3.336374E-01,-4.098166E-01,... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_1350kW_7_90COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1350400, COP_nominal = 7.90, PLRMin = 0.19, PLRMinUnl = 0.19, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.03684, mCon_flow_nominal = 1000 * 0.05337, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 12.78, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {1.063866E+00,-1.448990E-02,-1.021036E-03,-1.197817E-03,-4.163507E-04,1.927446E-03}, EIRFunT = {9.953536E-01,-3.118863E-02,2.094171E-03,7.086716E-03,7.387078E-04,-1.384330E-03}, EIRFunPLR = {3.336374E-01,-4.098166E-01,1.077791E+00}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 1350kW/7.90COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YT_1368kW_7_35COP_VSD

ElectricEIRChiller York YT 1368kW/7.35COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YT 1368kW/7.35COP/VSD,  !- Name
        1367900,                 !- Reference Capacity {W}
        7.35,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.05047,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.07571,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YT 1368kW/7.35COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YT 1368kW/7.35COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YT 1368kW/7.35COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1367900 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.35 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.05047 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.07571 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {3.832184E-01,-3.265439E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {3.227543E-01,-1.415418E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {9.483562E-02,1.521114E-01,7... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YT_1368kW_7_35COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1367900, COP_nominal = 7.35, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.05047, mCon_flow_nominal = 1000 * 0.07571, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {3.832184E-01,-3.265439E-02,-3.392654E-03,8.580180E-02,-3.513013E-03,6.528440E-03}, EIRFunT = {3.227543E-01,-1.415418E-02,-5.090650E-03,4.606511E-02,-8.769578E-04,2.600343E-03}, EIRFunPLR = {9.483562E-02,1.521114E-01,7.543027E-01}, etaMotor = 1.0) "ElectricEIRChiller York YT 1368kW/7.35COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_CVHE_1372kW_7_49COP_Vanes

ElectricEIRChiller Trane CVHE 1372kW/7.49COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane CVHE 1372kW/7.49COP/Vanes,  !- Name
        1371500,                 !- Reference Capacity {W}
        7.49,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.05047,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.07571,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane CVHE 1372kW/7.49COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHE 1372kW/7.49COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHE 1372kW/7.49COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.41,                    !- Minimum Part Load Ratio
        1.07,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.41,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.07 | Maximum part load ratio
Real | PLRMinUnl | 0.41 | Minimum part unload ratio
Real | PLRMin | 0.41 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1371500 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.49 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.05047 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.07571 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {5.993784E-01,6.523380E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {9.123765E-01,1.616509E-02,1... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {5.154478E-02,9.635713E-01,-... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_CVHE_1372kW_7_49COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1371500, COP_nominal = 7.49, PLRMin = 0.41, PLRMinUnl = 0.41, PLRMax = 1.07, mEva_flow_nominal = 1000 * 0.05047, mCon_flow_nominal = 1000 * 0.07571, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {5.993784E-01,6.523380E-02,-7.714286E-03,3.114955E-02,-1.843989E-03,4.096552E-03}, EIRFunT = {9.123765E-01,1.616509E-02,1.906349E-03,-1.143164E-02,1.080775E-03,-2.873661E-03}, EIRFunPLR = {5.154478E-02,9.635713E-01,-1.896824E-02}, etaMotor = 1.0) "ElectricEIRChiller Trane CVHE 1372kW/7.49COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YT_1396kW_7_35COP_Vanes

ElectricEIRChiller York YT 1396kW/7.35COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YT 1396kW/7.35COP/Vanes,  !- Name
        1396100,                 !- Reference Capacity {W}
        7.35,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.05047,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.07571,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YT 1396kW/7.35COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YT 1396kW/7.35COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YT 1396kW/7.35COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1396100 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.35 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.05047 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.07571 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {5.167863E-01,-2.788454E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.207500E-01,-9.073869E-03,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {3.043032E-01,3.720107E-02,6... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YT_1396kW_7_35COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1396100, COP_nominal = 7.35, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.05047, mCon_flow_nominal = 1000 * 0.07571, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {5.167863E-01,-2.788454E-02,-9.497810E-04,6.693411E-02,-2.728430E-03,4.723123E-03}, EIRFunT = {5.207500E-01,-9.073869E-03,-1.812171E-04,2.568740E-02,4.255936E-05,-5.899242E-04}, EIRFunPLR = {3.043032E-01,3.720107E-02,6.590338E-01}, etaMotor = 1.0) "ElectricEIRChiller York YT 1396kW/7.35COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_1403kW_7_09COP_VSD

ElectricEIRChiller Carrier 19XR 1403kW/7.09COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 1403kW/7.09COP/VSD,  !- Name
        1403100,                 !- Reference Capacity {W}
        7.09,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        12.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.03426,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.04252,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 1403kW/7.09COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1403kW/7.09COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1403kW/7.09COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.17,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.17,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.17 | Minimum part unload ratio
Real | PLRMin | 0.17 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 12.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1403100 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.09 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.03426 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.04252 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {9.601814E-01,-3.596494E-03,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {1.098641E+00,-2.485880E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {8.788698E-02,2.678891E-01,6... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 6.67 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.22 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_1403kW_7_09COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1403100, COP_nominal = 7.09, PLRMin = 0.17, PLRMinUnl = 0.17, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.03426, mCon_flow_nominal = 1000 * 0.04252, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 12.78, TEvaLvgMin = 273.15 + 6.67, TEvaLvgMax = 273.15 + 12.22, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {9.601814E-01,-3.596494E-03,-1.706786E-03,6.272429E-03,-9.858212E-04,2.611673E-03}, EIRFunT = {1.098641E+00,-2.485880E-02,-6.240421E-05,-1.719488E-03,4.887321E-04,9.618075E-05}, EIRFunPLR = {8.788698E-02,2.678891E-01,6.445180E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 1403kW/7.09COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YT_1403kW_6_94COP_VSD

ElectricEIRChiller York YT 1403kW/6.94COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YT 1403kW/6.94COP/VSD,  !- Name
        1403100,                 !- Reference Capacity {W}
        6.94,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.05047,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.05047,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YT 1403kW/6.94COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YT 1403kW/6.94COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YT 1403kW/6.94COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.1,                     !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.1 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1403100 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.94 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.05047 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.05047 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {-3.447077E-02,1.273138E-01,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {3.983846E-01,2.396665E-02,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {3.272242E-02,3.873540E-01,5... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YT_1403kW_6_94COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1403100, COP_nominal = 6.94, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.1, mEva_flow_nominal = 1000 * 0.05047, mCon_flow_nominal = 1000 * 0.05047, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {-3.447077E-02,1.273138E-01,-9.716868E-03,8.863546E-02,-3.165958E-03,2.521351E-03}, EIRFunT = {3.983846E-01,2.396665E-02,-6.601871E-03,2.944077E-02,-4.570885E-04,1.873209E-03}, EIRFunPLR = {3.272242E-02,3.873540E-01,5.789579E-01}, etaMotor = 1.0) "ElectricEIRChiller York YT 1403kW/6.94COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_CVHE_1407kW_7_14COP_VSD

ElectricEIRChiller Trane CVHE 1407kW/7.14COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane CVHE 1407kW/7.14COP/VSD,  !- Name
        1406600,                 !- Reference Capacity {W}
        7.14,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.05047,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.07571,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane CVHE 1407kW/7.14COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHE 1407kW/7.14COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHE 1407kW/7.14COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.30,                    !- Minimum Part Load Ratio
        1.06,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.30,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.06 | Maximum part load ratio
Real | PLRMinUnl | 0.30 | Minimum part unload ratio
Real | PLRMin | 0.30 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1406600 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.14 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.05047 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.07571 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {4.521342E-01,5.248142E-03,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.674858E-01,4.461513E-02,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {5.963988E-02,3.503067E-01,5... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_CVHE_1407kW_7_14COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1406600, COP_nominal = 7.14, PLRMin = 0.30, PLRMinUnl = 0.30, PLRMax = 1.06, mEva_flow_nominal = 1000 * 0.05047, mCon_flow_nominal = 1000 * 0.07571, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {4.521342E-01,5.248142E-03,-6.687636E-03,5.869437E-02,-2.390647E-03,5.040171E-03}, EIRFunT = {5.674858E-01,4.461513E-02,-6.341978E-03,4.674972E-03,4.387295E-04,2.778096E-04}, EIRFunPLR = {5.963988E-02,3.503067E-01,5.870000E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane CVHE 1407kW/7.14COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_McQuay_PFH_1407kW_6_60COP_Vanes

ElectricEIRChiller McQuay PFH 1407kW/6.60COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller McQuay PFH 1407kW/6.60COP/Vanes,  !- Name
        1406600,                 !- Reference Capacity {W}
        6.60,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        22.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.04038,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.05804,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller McQuay PFH 1407kW/6.60COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller McQuay PFH 1407kW/6.60COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller McQuay PFH 1407kW/6.60COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.04,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.04 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 22.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1406600 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.60 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.04038 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.05804 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.191784E+00,2.070584E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {7.929709E-01,3.424884E-02,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {7.700603E-02,5.414789E-01,3... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_McQuay_PFH_1407kW_6_60COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1406600, COP_nominal = 6.60, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.04, mEva_flow_nominal = 1000 * 0.04038, mCon_flow_nominal = 1000 * 0.05804, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 22.78, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {1.191784E+00,2.070584E-02,-4.952378E-03,1.757508E-02,-2.487599E-03,5.934709E-03}, EIRFunT = {7.929709E-01,3.424884E-02,-5.567434E-03,-6.974667E-03,2.531138E-04,1.862577E-03}, EIRFunPLR = {7.700603E-02,5.414789E-01,3.826334E-01}, etaMotor = 1.0) "ElectricEIRChiller McQuay PFH 1407kW/6.60COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_1407kW_6_04COP_VSD

ElectricEIRChiller Carrier 19XR 1407kW/6.04COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 1407kW/6.04COP/VSD,  !- Name
        1406600,                 !- Reference Capacity {W}
        6.04,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        29.44,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.06057,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.07571,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 1407kW/6.04COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1407kW/6.04COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1407kW/6.04COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.04,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.04 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 29.44 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1406600 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.04 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.06057 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.07571 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.042261E+00,2.644821E-03,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {1.026340E+00,-1.612819E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.188880E-01,6.723542E-01,2... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 32.22 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_1407kW_6_04COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1406600, COP_nominal = 6.04, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.04, mEva_flow_nominal = 1000 * 0.06057, mCon_flow_nominal = 1000 * 0.07571, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 29.44, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 32.22, capFunT = {1.042261E+00,2.644821E-03,-1.468026E-03,1.366256E-02,-8.302334E-04,1.573579E-03}, EIRFunT = {1.026340E+00,-1.612819E-02,-1.092591E-03,-1.784393E-02,7.961842E-04,-9.586049E-05}, EIRFunPLR = {1.188880E-01,6.723542E-01,2.068754E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 1407kW/6.04COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_1410kW_8_54COP_VSD

ElectricEIRChiller Carrier 19XR 1410kW/8.54COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 1410kW/8.54COP/VSD,  !- Name
        1410100,                 !- Reference Capacity {W}
        8.54,                    !- Reference COP {W/W}
        6.11,                    !- Reference Leaving Chilled Water Temperature {C}
        12.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.04,                    !- Reference Chilled Water Flow Rate {m3/s}
        0.05861,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 1410kW/8.54COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1410kW/8.54COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1410kW/8.54COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.18,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.18,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.18 | Minimum part unload ratio
Real | PLRMin | 0.18 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 12.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1410100 | Reference capacity (negative number) [W]
Real | COP_nominal | 8.54 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.04 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.05861 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.11 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {9.597856E-01,-6.247187E-03,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {1.131014E+00,-6.735406E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {9.662908E-02,7.475978E-01,1... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 6.11 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_1410kW_8_54COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1410100, COP_nominal = 8.54, PLRMin = 0.18, PLRMinUnl = 0.18, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.04, mCon_flow_nominal = 1000 * 0.05861, TEvaLvg_nominal = 273.15 + 6.11, TConEnt_nominal = 273.15 + 12.78, TEvaLvgMin = 273.15 + 6.11, TEvaLvgMax = 273.15 + 12.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {9.597856E-01,-6.247187E-03,-1.117998E-03,6.991040E-03,-6.321252E-04,1.765068E-03}, EIRFunT = {1.131014E+00,-6.735406E-02,3.034309E-06,1.307361E-02,3.384625E-04,7.872113E-04}, EIRFunPLR = {9.662908E-02,7.475978E-01,1.566368E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 1410kW/8.54COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_CVHE_1442kW_6_61COP_VSD

ElectricEIRChiller Trane CVHE 1442kW/6.61COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane CVHE 1442kW/6.61COP/VSD,  !- Name
        1441800,                 !- Reference Capacity {W}
        6.61,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.05047,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.05047,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane CVHE 1442kW/6.61COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHE 1442kW/6.61COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHE 1442kW/6.61COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.07,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.07 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1441800 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.61 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.05047 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.05047 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {4.007341E-01,1.148568E-03,1... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {6.287646E-01,-3.024605E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {9.299787E-02,3.244475E-01,5... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 35.00 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_CVHE_1442kW_6_61COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1441800, COP_nominal = 6.61, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.07, mEva_flow_nominal = 1000 * 0.05047, mCon_flow_nominal = 1000 * 0.05047, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 35.00, capFunT = {4.007341E-01,1.148568E-03,1.049504E-04,5.574667E-02,-1.646131E-03,1.323200E-03}, EIRFunT = {6.287646E-01,-3.024605E-02,6.137016E-04,1.805826E-02,1.640653E-04,-1.113802E-04}, EIRFunPLR = {9.299787E-02,3.244475E-01,5.818753E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane CVHE 1442kW/6.61COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YT_1459kW_6_40COP_VSD

ElectricEIRChiller York YT 1459kW/6.40COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YT 1459kW/6.40COP/VSD,  !- Name
        1459400,                 !- Reference Capacity {W}
        6.40,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.05047,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.05047,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YT 1459kW/6.40COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YT 1459kW/6.40COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YT 1459kW/6.40COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.13,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.13 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1459400 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.40 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.05047 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.05047 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {-1.665585E-01,2.211580E-01,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {1.438935E-01,9.821191E-02,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {3.999642E-02,2.509430E-01,7... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YT_1459kW_6_40COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1459400, COP_nominal = 6.40, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.13, mEva_flow_nominal = 1000 * 0.05047, mCon_flow_nominal = 1000 * 0.05047, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {-1.665585E-01,2.211580E-01,-1.408361E-02,6.476151E-02,-2.009341E-03,-7.897630E-05}, EIRFunT = {1.438935E-01,9.821191E-02,-1.174270E-02,3.748666E-02,-5.700518E-04,1.053698E-03}, EIRFunPLR = {3.999642E-02,2.509430E-01,7.067059E-01}, etaMotor = 1.0) "ElectricEIRChiller York YT 1459kW/6.40COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_CVHE_1484kW_9_96COP_VSD

ElectricEIRChiller Trane CVHE 1484kW/9.96COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane CVHE 1484kW/9.96COP/VSD,  !- Name
        1484000,                 !- Reference Capacity {W}
        9.96,                    !- Reference COP {W/W}
        4.44,                    !- Reference Leaving Chilled Water Temperature {C}
        12.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.07571,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.09085,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane CVHE 1484kW/9.96COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHE 1484kW/9.96COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHE 1484kW/9.96COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.24,                    !- Minimum Part Load Ratio
        1.06,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.24,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.06 | Maximum part load ratio
Real | PLRMinUnl | 0.24 | Minimum part unload ratio
Real | PLRMin | 0.24 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 12.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1484000 | Reference capacity (negative number) [W]
Real | COP_nominal | 9.96 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.07571 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.09085 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 4.44 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {-4.544480E-01,-3.615933E-02... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {-3.693940E-01,-6.387787E-02... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.353827E-01,1.385983E-02,8... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_CVHE_1484kW_9_96COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1484000, COP_nominal = 9.96, PLRMin = 0.24, PLRMinUnl = 0.24, PLRMax = 1.06, mEva_flow_nominal = 1000 * 0.07571, mCon_flow_nominal = 1000 * 0.09085, TEvaLvg_nominal = 273.15 + 4.44, TConEnt_nominal = 273.15 + 12.78, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {-4.544480E-01,-3.615933E-02,-2.734006E-03,1.683863E-01,-4.557649E-03,5.362840E-03}, EIRFunT = {-3.693940E-01,-6.387787E-02,-2.760494E-04,1.661135E-01,-3.105485E-03,1.705909E-03}, EIRFunPLR = {1.353827E-01,1.385983E-02,8.522688E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane CVHE 1484kW/9.96COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YT_1495kW_7_51COP_VSD

ElectricEIRChiller York YT 1495kW/7.51COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YT 1495kW/7.51COP/VSD,  !- Name
        1494500,                 !- Reference Capacity {W}
        7.51,                    !- Reference COP {W/W}
        7.22,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.0429,                  !- Reference Chilled Water Flow Rate {m3/s}
        0.06719,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YT 1495kW/7.51COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YT 1495kW/7.51COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YT 1495kW/7.51COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.11,                    !- Minimum Part Load Ratio
        1.05,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.11,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.05 | Maximum part load ratio
Real | PLRMinUnl | 0.11 | Minimum part unload ratio
Real | PLRMin | 0.11 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1494500 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.51 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.0429 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.06719 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 7.22 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.051921E+00,-1.632255E-01,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {7.106985E-01,-2.087623E-01,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.517470E-01,-1.577252E-01,... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 35.00 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YT_1495kW_7_51COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1494500, COP_nominal = 7.51, PLRMin = 0.11, PLRMinUnl = 0.11, PLRMax = 1.05, mEva_flow_nominal = 1000 * 0.0429, mCon_flow_nominal = 1000 * 0.06719, TEvaLvg_nominal = 273.15 + 7.22, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 35.00, capFunT = {1.051921E+00,-1.632255E-01,1.149042E-02,5.463515E-02,-1.579985E-03,1.628246E-03}, EIRFunT = {7.106985E-01,-2.087623E-01,9.421379E-03,8.491925E-02,-1.260820E-03,1.125512E-03}, EIRFunPLR = {1.517470E-01,-1.577252E-01,1.005197E+00}, etaMotor = 1.0) "ElectricEIRChiller York YT 1495kW/7.51COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_McQuay_WSC_1519kW_7_10COP_Vanes

ElectricEIRChiller McQuay WSC 1519kW/7.10COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller McQuay WSC 1519kW/7.10COP/Vanes,  !- Name
        1519200,                 !- Reference Capacity {W}
        7.10,                    !- Reference COP {W/W}
        8.89,                    !- Reference Leaving Chilled Water Temperature {C}
        26.67,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.03186,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.08139,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller McQuay WSC 1519kW/7.10COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller McQuay WSC 1519kW/7.10COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller McQuay WSC 1519kW/7.10COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.67 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1519200 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.10 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.03186 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.08139 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 8.89 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.265889E+00,3.401563E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {9.981236E-01,-1.060763E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.563837E-01,4.894381E-01,3... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 7.22 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 26.67 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_McQuay_WSC_1519kW_7_10COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1519200, COP_nominal = 7.10, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.03186, mCon_flow_nominal = 1000 * 0.08139, TEvaLvg_nominal = 273.15 + 8.89, TConEnt_nominal = 273.15 + 26.67, TEvaLvgMin = 273.15 + 7.22, TEvaLvgMax = 273.15 + 12.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 26.67, capFunT = {1.265889E+00,3.401563E-02,-6.532621E-03,-6.600960E-03,-2.172017E-03,7.121766E-03}, EIRFunT = {9.981236E-01,-1.060763E-02,-3.921458E-03,-1.206761E-02,-1.398595E-04,3.467199E-03}, EIRFunPLR = {1.563837E-01,4.894381E-01,3.541551E-01}, etaMotor = 1.0) "ElectricEIRChiller McQuay WSC 1519kW/7.10COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_1558kW_5_81COP_VSD

ElectricEIRChiller Carrier 19XR 1558kW/5.81COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 1558kW/5.81COP/VSD,  !- Name
        1557800,                 !- Reference Capacity {W}
        5.81,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        21.11,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.03785,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.05142,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 1558kW/5.81COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1558kW/5.81COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1558kW/5.81COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.19,                    !- Minimum Part Load Ratio
        1.01,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.19,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.01 | Maximum part load ratio
Real | PLRMinUnl | 0.19 | Minimum part unload ratio
Real | PLRMin | 0.19 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 21.11 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1557800 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.81 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.03785 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.05142 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.034307E+00,2.390635E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {1.099343E+00,-3.132676E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.620909E-01,-2.553890E-01,... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 11.94 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_1558kW_5_81COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1557800, COP_nominal = 5.81, PLRMin = 0.19, PLRMinUnl = 0.19, PLRMax = 1.01, mEva_flow_nominal = 1000 * 0.03785, mCon_flow_nominal = 1000 * 0.05142, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 21.11, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 11.94, TConEntMax = 273.15 + 23.89, capFunT = {1.034307E+00,2.390635E-02,-1.222578E-03,-5.346220E-03,-2.183258E-04,6.282331E-04}, EIRFunT = {1.099343E+00,-3.132676E-02,4.108521E-04,-7.377845E-03,5.775048E-04,-3.528472E-04}, EIRFunPLR = {1.620909E-01,-2.553890E-01,1.092232E+00}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 1558kW/5.81COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_1586kW_5_53COP_VSD

ElectricEIRChiller Carrier 19XR 1586kW/5.53COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 1586kW/5.53COP/VSD,  !- Name
        1586000,                 !- Reference Capacity {W}
        5.53,                    !- Reference COP {W/W}
        8.89,                    !- Reference Leaving Chilled Water Temperature {C}
        26.67,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.03388,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.04669,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 1586kW/5.53COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1586kW/5.53COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1586kW/5.53COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.19,                    !- Minimum Part Load Ratio
        1.01,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.19,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.01 | Maximum part load ratio
Real | PLRMinUnl | 0.19 | Minimum part unload ratio
Real | PLRMin | 0.19 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.67 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1586000 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.53 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.03388 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.04669 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 8.89 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.119233E+00,1.130501E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {1.110611E+00,-3.795765E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.996379E-01,-1.612021E-01,... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 7.22 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 26.67 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_1586kW_5_53COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1586000, COP_nominal = 5.53, PLRMin = 0.19, PLRMinUnl = 0.19, PLRMax = 1.01, mEva_flow_nominal = 1000 * 0.03388, mCon_flow_nominal = 1000 * 0.04669, TEvaLvg_nominal = 273.15 + 8.89, TConEnt_nominal = 273.15 + 26.67, TEvaLvgMin = 273.15 + 7.22, TEvaLvgMax = 273.15 + 12.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 26.67, capFunT = {1.119233E+00,1.130501E-02,-6.423802E-04,-5.144512E-03,-3.085995E-04,7.813582E-04}, EIRFunT = {1.110611E+00,-3.795765E-02,2.851444E-04,-4.560404E-03,4.044229E-04,1.407332E-04}, EIRFunPLR = {1.996379E-01,-1.612021E-01,9.608483E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 1586kW/5.53COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_McQuay_PEH_1635kW_7_47COP_Vanes

ElectricEIRChiller McQuay PEH 1635kW/7.47COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller McQuay PEH 1635kW/7.47COP/Vanes,  !- Name
        1635200,                 !- Reference Capacity {W}
        7.47,                    !- Reference COP {W/W}
        4.44,                    !- Reference Leaving Chilled Water Temperature {C}
        12.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.04416,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.06624,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller McQuay PEH 1635kW/7.47COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller McQuay PEH 1635kW/7.47COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller McQuay PEH 1635kW/7.47COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.08,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.08,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.08 | Minimum part unload ratio
Real | PLRMin | 0.08 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 12.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1635200 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.47 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.04416 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.06624 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 4.44 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {9.894188E-01,2.983148E-03,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {1.040733E+00,-7.118888E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.836695E-01,5.781685E-01,2... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_McQuay_PEH_1635kW_7_47COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1635200, COP_nominal = 7.47, PLRMin = 0.08, PLRMinUnl = 0.08, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.04416, mCon_flow_nominal = 1000 * 0.06624, TEvaLvg_nominal = 273.15 + 4.44, TConEnt_nominal = 273.15 + 12.78, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {9.894188E-01,2.983148E-03,-2.484601E-03,5.974984E-03,-1.063988E-03,2.601503E-03}, EIRFunT = {1.040733E+00,-7.118888E-02,2.262395E-03,1.221901E-02,2.152693E-04,7.409943E-04}, EIRFunPLR = {1.836695E-01,5.781685E-01,2.385719E-01}, etaMotor = 1.0) "ElectricEIRChiller McQuay PEH 1635kW/7.47COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_1635kW_6_36COP_Vanes

ElectricEIRChiller Carrier 19XR 1635kW/6.36COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 1635kW/6.36COP/Vanes,  !- Name
        1635200,                 !- Reference Capacity {W}
        6.36,                    !- Reference COP {W/W}
        8.89,                    !- Reference Leaving Chilled Water Temperature {C}
        26.67,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.03432,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.05035,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 1635kW/6.36COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1635kW/6.36COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1635kW/6.36COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.18,                    !- Minimum Part Load Ratio
        1.05,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.18,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.05 | Maximum part load ratio
Real | PLRMinUnl | 0.18 | Minimum part unload ratio
Real | PLRMin | 0.18 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.67 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1635200 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.36 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.03432 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.05035 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 8.89 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {7.639212E-01,1.160405E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {7.355981E-01,-1.083354E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.581595E-01,2.707154E-01,4... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 7.22 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 26.67 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_1635kW_6_36COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1635200, COP_nominal = 6.36, PLRMin = 0.18, PLRMinUnl = 0.18, PLRMax = 1.05, mEva_flow_nominal = 1000 * 0.03432, mCon_flow_nominal = 1000 * 0.05035, TEvaLvg_nominal = 273.15 + 8.89, TConEnt_nominal = 273.15 + 26.67, TEvaLvgMin = 273.15 + 7.22, TEvaLvgMax = 273.15 + 12.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 26.67, capFunT = {7.639212E-01,1.160405E-02,-5.344185E-03,3.306796E-02,-2.100827E-03,4.920586E-03}, EIRFunT = {7.355981E-01,-1.083354E-02,-9.244662E-04,1.458943E-02,8.494647E-06,1.279572E-04}, EIRFunPLR = {2.581595E-01,2.707154E-01,4.707425E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 1635kW/6.36COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_1656kW_8_24COP_VSD

ElectricEIRChiller Carrier 19XR 1656kW/8.24COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 1656kW/8.24COP/VSD,  !- Name
        1656300,                 !- Reference Capacity {W}
        8.24,                    !- Reference COP {W/W}
        6.11,                    !- Reference Leaving Chilled Water Temperature {C}
        12.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.04322,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.06296,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 1656kW/8.24COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1656kW/8.24COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1656kW/8.24COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.17,                    !- Minimum Part Load Ratio
        1.04,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.17,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.04 | Maximum part load ratio
Real | PLRMinUnl | 0.17 | Minimum part unload ratio
Real | PLRMin | 0.17 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 12.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1656300 | Reference capacity (negative number) [W]
Real | COP_nominal | 8.24 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.04322 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.06296 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.11 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {7.611706E-01,-2.867067E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {7.730916E-01,-8.073559E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.982584E-01,4.414042E-02,7... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 6.11 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_1656kW_8_24COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1656300, COP_nominal = 8.24, PLRMin = 0.17, PLRMinUnl = 0.17, PLRMax = 1.04, mEva_flow_nominal = 1000 * 0.04322, mCon_flow_nominal = 1000 * 0.06296, TEvaLvg_nominal = 273.15 + 6.11, TConEnt_nominal = 273.15 + 12.78, TEvaLvgMin = 273.15 + 6.11, TEvaLvgMax = 273.15 + 12.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {7.611706E-01,-2.867067E-02,-2.363358E-03,4.097113E-02,-2.343044E-03,4.547017E-03}, EIRFunT = {7.730916E-01,-8.073559E-02,-2.161313E-03,6.144398E-02,-1.953734E-03,4.056527E-03}, EIRFunPLR = {1.982584E-01,4.414042E-02,7.642946E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 1656kW/8.24COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YT_1663kW_9_34COP_Vanes

ElectricEIRChiller York YT 1663kW/9.34COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YT 1663kW/9.34COP/Vanes,  !- Name
        1663300,                 !- Reference Capacity {W}
        9.34,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        12.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.04139,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.0776,                  !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YT 1663kW/9.34COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YT 1663kW/9.34COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YT 1663kW/9.34COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.17,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.17,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.17 | Minimum part unload ratio
Real | PLRMin | 0.17 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 12.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1663300 | Reference capacity (negative number) [W]
Real | COP_nominal | 9.34 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.04139 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.0776 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {9.112226E-01,-4.546497E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {1.028094E+00,-6.127553E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.127966E-01,3.131004E-01,4... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YT_1663kW_9_34COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1663300, COP_nominal = 9.34, PLRMin = 0.17, PLRMinUnl = 0.17, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.04139, mCon_flow_nominal = 1000 * 0.0776, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 12.78, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {9.112226E-01,-4.546497E-02,4.431126E-03,2.439160E-02,-1.415836E-03,1.877877E-03}, EIRFunT = {1.028094E+00,-6.127553E-02,3.236371E-03,1.656482E-02,2.976850E-04,-4.418361E-04}, EIRFunPLR = {2.127966E-01,3.131004E-01,4.726018E-01}, etaMotor = 1.0) "ElectricEIRChiller York YT 1663kW/9.34COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XL_1674kW_7_89COP_Vanes

ElectricEIRChiller Carrier 19XL 1674kW/7.89COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XL 1674kW/7.89COP/Vanes,  !- Name
        1673900,                 !- Reference Capacity {W}
        7.89,                    !- Reference COP {W/W}
        4.44,                    !- Reference Leaving Chilled Water Temperature {C}
        12.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.07571,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.09085,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XL 1674kW/7.89COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XL 1674kW/7.89COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XL 1674kW/7.89COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.32,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.32,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.32 | Minimum part unload ratio
Real | PLRMin | 0.32 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 12.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1673900 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.89 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.07571 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.09085 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 4.44 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {2.925408E-01,-4.406182E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {9.868510E-01,-6.325526E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {3.386410E-01,2.621224E-01,3... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XL_1674kW_7_89COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1673900, COP_nominal = 7.89, PLRMin = 0.32, PLRMinUnl = 0.32, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.07571, mCon_flow_nominal = 1000 * 0.09085, TEvaLvg_nominal = 273.15 + 4.44, TConEnt_nominal = 273.15 + 12.78, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {2.925408E-01,-4.406182E-02,-1.292074E-03,9.008701E-02,-2.646719E-03,3.388396E-03}, EIRFunT = {9.868510E-01,-6.325526E-02,3.498632E-03,1.699731E-02,2.573490E-04,-4.233553E-04}, EIRFunPLR = {3.386410E-01,2.621224E-01,3.987109E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XL 1674kW/7.89COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_CVHF_1681kW_6_59COP_Vanes

ElectricEIRChiller Trane CVHF 1681kW/6.59COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane CVHF 1681kW/6.59COP/Vanes,  !- Name
        1680900,                 !- Reference Capacity {W}
        6.59,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.04366,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.05142,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane CVHF 1681kW/6.59COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHF 1681kW/6.59COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHF 1681kW/6.59COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1680900 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.59 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.04366 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.05142 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {6.792987E-01,-5.291217E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {4.344630E-01,-5.781149E-03,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.619116E-01,2.362420E-01,6... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 18.33 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_CVHF_1681kW_6_59COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1680900, COP_nominal = 6.59, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.04366, mCon_flow_nominal = 1000 * 0.05142, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 18.33, TConEntMax = 273.15 + 23.89, capFunT = {6.792987E-01,-5.291217E-02,-5.280108E-03,5.252682E-02,-2.523689E-03,7.344940E-03}, EIRFunT = {4.344630E-01,-5.781149E-03,2.852311E-04,2.723246E-02,1.280801E-04,-8.964328E-04}, EIRFunPLR = {1.619116E-01,2.362420E-01,6.032459E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane CVHF 1681kW/6.59COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_1723kW_8_32COP_VSD

ElectricEIRChiller Carrier 19XR 1723kW/8.32COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 1723kW/8.32COP/VSD,  !- Name
        1723100,                 !- Reference Capacity {W}
        8.32,                    !- Reference COP {W/W}
        6.11,                    !- Reference Leaving Chilled Water Temperature {C}
        12.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.04757,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.06934,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 1723kW/8.32COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1723kW/8.32COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1723kW/8.32COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.18,                    !- Minimum Part Load Ratio
        1.04,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.18,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.04 | Maximum part load ratio
Real | PLRMinUnl | 0.18 | Minimum part unload ratio
Real | PLRMin | 0.18 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 12.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1723100 | Reference capacity (negative number) [W]
Real | COP_nominal | 8.32 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.04757 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.06934 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.11 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {4.742518E-01,-5.109937E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {2.950574E-01,-1.036684E-01,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.374010E-01,-1.796745E-01,... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 6.11 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_1723kW_8_32COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1723100, COP_nominal = 8.32, PLRMin = 0.18, PLRMinUnl = 0.18, PLRMax = 1.04, mEva_flow_nominal = 1000 * 0.04757, mCon_flow_nominal = 1000 * 0.06934, TEvaLvg_nominal = 273.15 + 6.11, TConEnt_nominal = 273.15 + 12.78, TEvaLvgMin = 273.15 + 6.11, TEvaLvgMax = 273.15 + 12.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {4.742518E-01,-5.109937E-02,-2.845323E-03,8.257997E-02,-3.404799E-03,5.625321E-03}, EIRFunT = {2.950574E-01,-1.036684E-01,-4.169567E-03,1.256790E-01,-4.004203E-03,6.718687E-03}, EIRFunPLR = {2.374010E-01,-1.796745E-01,9.441507E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 1723kW/8.32COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_1727kW_9_04COP_Vanes

ElectricEIRChiller Carrier 19XR 1727kW/9.04COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 1727kW/9.04COP/Vanes,  !- Name
        1726600,                 !- Reference Capacity {W}
        9.04,                    !- Reference COP {W/W}
        7.78,                    !- Reference Leaving Chilled Water Temperature {C}
        12.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.03912,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.07192,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 1727kW/9.04COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1727kW/9.04COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1727kW/9.04COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.17,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.17,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.17 | Minimum part unload ratio
Real | PLRMin | 0.17 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 12.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1726600 | Reference capacity (negative number) [W]
Real | COP_nominal | 9.04 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.03912 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.07192 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 7.78 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {6.509915E-01,2.567642E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {1.072553E+00,-8.058631E-03,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.465824E-01,4.494453E-01,3... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_1727kW_9_04COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1726600, COP_nominal = 9.04, PLRMin = 0.17, PLRMinUnl = 0.17, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.03912, mCon_flow_nominal = 1000 * 0.07192, TEvaLvg_nominal = 273.15 + 7.78, TConEnt_nominal = 273.15 + 12.78, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {6.509915E-01,2.567642E-02,-5.417815E-03,3.406103E-02,-1.703640E-03,3.336164E-03}, EIRFunT = {1.072553E+00,-8.058631E-03,-2.109608E-03,-1.262910E-03,6.155442E-04,4.796754E-04}, EIRFunPLR = {2.465824E-01,4.494453E-01,3.037680E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 1727kW/9.04COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_McQuay_WSC_1751kW_6_73COP_Vanes

ElectricEIRChiller McQuay WSC 1751kW/6.73COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller McQuay WSC 1751kW/6.73COP/Vanes,  !- Name
        1751300,                 !- Reference Capacity {W}
        6.73,                    !- Reference COP {W/W}
        8.89,                    !- Reference Leaving Chilled Water Temperature {C}
        26.67,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.04145,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.09337,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller McQuay WSC 1751kW/6.73COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller McQuay WSC 1751kW/6.73COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller McQuay WSC 1751kW/6.73COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.06,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.06 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.67 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1751300 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.73 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.04145 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.09337 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 8.89 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {7.923045E-01,1.003672E-01,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {8.089395E-01,2.628482E-02,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.250725E-01,2.648297E-01,5... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 7.22 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 26.67 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_McQuay_WSC_1751kW_6_73COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1751300, COP_nominal = 6.73, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.06, mEva_flow_nominal = 1000 * 0.04145, mCon_flow_nominal = 1000 * 0.09337, TEvaLvg_nominal = 273.15 + 8.89, TConEnt_nominal = 273.15 + 26.67, TEvaLvgMin = 273.15 + 7.22, TEvaLvgMax = 273.15 + 12.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 26.67, capFunT = {7.923045E-01,1.003672E-01,-4.348900E-03,3.755572E-03,-7.675491E-04,6.788600E-04}, EIRFunT = {8.089395E-01,2.628482E-02,-1.773497E-03,-8.118430E-03,7.146809E-04,-6.481705E-04}, EIRFunPLR = {2.250725E-01,2.648297E-01,5.095786E-01}, etaMotor = 1.0) "ElectricEIRChiller McQuay WSC 1751kW/6.73COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_CVHF_1758kW_5_96COP_Vanes

ElectricEIRChiller Trane CVHF 1758kW/5.96COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane CVHF 1758kW/5.96COP/Vanes,  !- Name
        1758300,                 !- Reference Capacity {W}
        5.96,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        24.44,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.06309,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.06309,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane CVHF 1758kW/5.96COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHF 1758kW/5.96COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHF 1758kW/5.96COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 24.44 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1758300 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.96 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.06309 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.06309 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.074211E+00,7.710761E-03,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {4.910329E-01,-9.895115E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {3.694797E-01,9.551656E-02,5... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 24.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_CVHF_1758kW_5_96COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1758300, COP_nominal = 5.96, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.06309, mCon_flow_nominal = 1000 * 0.06309, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 24.44, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 24.44, capFunT = {1.074211E+00,7.710761E-03,-3.166770E-03,-1.868765E-02,1.273866E-04,2.744586E-03}, EIRFunT = {4.910329E-01,-9.895115E-02,4.257871E-03,5.433817E-02,-8.184909E-04,6.178810E-04}, EIRFunPLR = {3.694797E-01,9.551656E-02,5.347291E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane CVHF 1758kW/5.96COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YT_1758kW_5_76COP_VSD

ElectricEIRChiller York YT 1758kW/5.76COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YT 1758kW/5.76COP/VSD,  !- Name
        1758300,                 !- Reference Capacity {W}
        5.76,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        24.44,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.06309,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.06309,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YT 1758kW/5.76COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YT 1758kW/5.76COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YT 1758kW/5.76COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 24.44 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1758300 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.76 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.06309 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.06309 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {4.575085E-01,1.313508E-01,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {6.794525E-01,6.694756E-02,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {7.859908E-02,1.950291E-01,7... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.51 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 24.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YT_1758kW_5_76COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1758300, COP_nominal = 5.76, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.06309, mCon_flow_nominal = 1000 * 0.06309, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 24.44, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.51, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 24.44, capFunT = {4.575085E-01,1.313508E-01,-4.408831E-03,1.930354E-02,-5.479641E-04,-1.376580E-03}, EIRFunT = {6.794525E-01,6.694756E-02,-3.625396E-03,-1.018762E-02,1.066394E-03,-2.113402E-03}, EIRFunPLR = {7.859908E-02,1.950291E-01,7.241581E-01}, etaMotor = 1.0) "ElectricEIRChiller York YT 1758kW/5.76COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YT_1758kW_6_26COP_Vanes

ElectricEIRChiller York YT 1758kW/6.26COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YT 1758kW/6.26COP/Vanes,  !- Name
        1758300,                 !- Reference Capacity {W}
        6.26,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        24.44,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.06309,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.06309,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YT 1758kW/6.26COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YT 1758kW/6.26COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YT 1758kW/6.26COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.14,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.14 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 24.44 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1758300 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.26 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.06309 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.06309 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {8.975936E-01,-1.459740E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {2.311197E-01,9.581517E-02,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.720545E-01,5.598164E-01,2... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 24.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YT_1758kW_6_26COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1758300, COP_nominal = 6.26, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.14, mEva_flow_nominal = 1000 * 0.06309, mCon_flow_nominal = 1000 * 0.06309, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 24.44, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 24.44, capFunT = {8.975936E-01,-1.459740E-02,3.647187E-03,3.202545E-02,-1.190379E-03,3.297810E-04}, EIRFunT = {2.311197E-01,9.581517E-02,-5.672726E-03,2.766035E-02,-1.411214E-04,-1.011216E-03}, EIRFunPLR = {1.720545E-01,5.598164E-01,2.626117E-01}, etaMotor = 1.0) "ElectricEIRChiller York YT 1758kW/6.26COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YT_1758kW_5_96COP_Vanes

ElectricEIRChiller York YT 1758kW/5.96COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YT 1758kW/5.96COP/Vanes,  !- Name
        1758300,                 !- Reference Capacity {W}
        5.96,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        24.44,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.06309,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.06309,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YT 1758kW/5.96COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YT 1758kW/5.96COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YT 1758kW/5.96COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.01,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.01 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 24.44 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1758300 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.96 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.06309 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.06309 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {8.492365E-01,5.551947E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {4.949320E-01,9.099785E-03,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.236154E-01,2.590053E-01,5... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 24.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YT_1758kW_5_96COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1758300, COP_nominal = 5.96, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.01, mEva_flow_nominal = 1000 * 0.06309, mCon_flow_nominal = 1000 * 0.06309, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 24.44, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 24.44, capFunT = {8.492365E-01,5.551947E-02,-2.973138E-04,1.164389E-03,-2.955716E-04,8.464931E-05}, EIRFunT = {4.949320E-01,9.099785E-03,-6.935841E-04,3.277452E-02,-3.895481E-04,-5.524011E-04}, EIRFunPLR = {2.236154E-01,2.590053E-01,5.169137E-01}, etaMotor = 1.0) "ElectricEIRChiller York YT 1758kW/5.96COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_CVHE_1758kW_5_96COP_Vanes

ElectricEIRChiller Trane CVHE 1758kW/5.96COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane CVHE 1758kW/5.96COP/Vanes,  !- Name
        1758300,                 !- Reference Capacity {W}
        5.96,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        29.44,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.07571,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.09464,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane CVHE 1758kW/5.96COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHE 1758kW/5.96COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHE 1758kW/5.96COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 29.44 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1758300 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.96 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.07571 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.09464 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {9.566057E-02,-2.457943E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {1.243313E+00,-3.031784E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.871377E-01,5.849639E-01,2... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 23.89 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 35.00 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_CVHE_1758kW_5_96COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1758300, COP_nominal = 5.96, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.07571, mCon_flow_nominal = 1000 * 0.09464, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 29.44, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 23.89, TConEntMax = 273.15 + 35.00, capFunT = {9.566057E-02,-2.457943E-02,-6.827143E-03,7.119360E-02,-2.047680E-03,5.248800E-03}, EIRFunT = {1.243313E+00,-3.031784E-02,3.452464E-03,-2.739941E-02,9.141695E-04,-1.000080E-03}, EIRFunPLR = {1.871377E-01,5.849639E-01,2.291447E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane CVHE 1758kW/5.96COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YT_1758kW_6_28COP_Vanes

ElectricEIRChiller York YT 1758kW/6.28COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YT 1758kW/6.28COP/Vanes,  !- Name
        1758300,                 !- Reference Capacity {W}
        6.28,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        29.44,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.07571,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.09464,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YT 1758kW/6.28COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YT 1758kW/6.28COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YT 1758kW/6.28COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.06,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.06 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 29.44 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1758300 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.28 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.07571 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.09464 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {7.079149E-01,-2.006276E-03,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.605391E-01,-1.377994E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.861223E-01,5.482049E-01,2... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 15.56 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 35.00 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YT_1758kW_6_28COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1758300, COP_nominal = 6.28, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.06, mEva_flow_nominal = 1000 * 0.07571, mCon_flow_nominal = 1000 * 0.09464, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 29.44, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 15.56, TConEntMax = 273.15 + 35.00, capFunT = {7.079149E-01,-2.006276E-03,-2.596043E-03,3.005922E-02,-1.056423E-03,2.045705E-03}, EIRFunT = {5.605391E-01,-1.377994E-02,6.569542E-05,1.321951E-02,2.686074E-04,-5.011451E-04}, EIRFunPLR = {1.861223E-01,5.482049E-01,2.647377E-01}, etaMotor = 1.0) "ElectricEIRChiller York YT 1758kW/6.28COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_1758kW_5_86COP_VSD

ElectricEIRChiller Carrier 19XR 1758kW/5.86COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 1758kW/5.86COP/VSD,  !- Name
        1758300,                 !- Reference Capacity {W}
        5.86,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        24.44,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.06303,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.07337,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 1758kW/5.86COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1758kW/5.86COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1758kW/5.86COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 24.44 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1758300 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.86 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.06303 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.07337 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {3.677279E-01,-3.175504E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {1.743365E-01,-5.054806E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.784580E-01,-5.498632E-01,... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 24.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_1758kW_5_86COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1758300, COP_nominal = 5.86, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.06303, mCon_flow_nominal = 1000 * 0.07337, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 24.44, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 24.44, capFunT = {3.677279E-01,-3.175504E-02,-4.096383E-03,7.527566E-02,-2.757540E-03,5.359020E-03}, EIRFunT = {1.743365E-01,-5.054806E-02,-5.424748E-03,8.244673E-02,-2.400392E-03,5.078720E-03}, EIRFunPLR = {2.784580E-01,-5.498632E-01,1.269693E+00}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 1758kW/5.86COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_CVHF_1758kW_6_46COP_VSD

ElectricEIRChiller Trane CVHF 1758kW/6.46COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane CVHF 1758kW/6.46COP/VSD,  !- Name
        1758300,                 !- Reference Capacity {W}
        6.46,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        24.44,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.06309,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.06309,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane CVHF 1758kW/6.46COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHF 1758kW/6.46COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHF 1758kW/6.46COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 24.44 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1758300 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.46 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.06309 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.06309 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.066671E+00,5.889240E-03,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {7.989434E-02,2.062907E-02,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {3.268954E-01,3.297771E-01,3... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 24.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_CVHF_1758kW_6_46COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1758300, COP_nominal = 6.46, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.06309, mCon_flow_nominal = 1000 * 0.06309, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 24.44, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 24.44, capFunT = {1.066671E+00,5.889240E-03,-3.155053E-03,-1.591039E-02,1.042897E-04,2.576256E-03}, EIRFunT = {7.989434E-02,2.062907E-02,-4.050827E-04,4.570552E-02,-1.469163E-04,-1.563259E-03}, EIRFunPLR = {3.268954E-01,3.297771E-01,3.423342E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane CVHF 1758kW/6.46COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_CVHF_1758kW_6_87COP_Vanes

ElectricEIRChiller Trane CVHF 1758kW/6.87COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane CVHF 1758kW/6.87COP/Vanes,  !- Name
        1758300,                 !- Reference Capacity {W}
        6.87,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        24.44,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.06309,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.06309,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane CVHF 1758kW/6.87COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHF 1758kW/6.87COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHF 1758kW/6.87COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 24.44 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1758300 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.87 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.06309 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.06309 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {8.085529E-01,3.412026E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {6.329473E-01,5.521802E-03,1... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.401900E-01,5.090345E-01,2... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 24.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_CVHF_1758kW_6_87COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1758300, COP_nominal = 6.87, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.06309, mCon_flow_nominal = 1000 * 0.06309, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 24.44, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 24.44, capFunT = {8.085529E-01,3.412026E-02,-4.184591E-04,4.111323E-03,-1.764627E-04,4.184748E-04}, EIRFunT = {6.329473E-01,5.521802E-03,1.487172E-04,2.433576E-03,7.100129E-04,-1.108627E-03}, EIRFunPLR = {2.401900E-01,5.090345E-01,2.500532E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane CVHF 1758kW/6.87COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_1776kW_8_00COP_Vanes

ElectricEIRChiller Carrier 19XR 1776kW/8.00COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 1776kW/8.00COP/Vanes,  !- Name
        1775900,                 !- Reference Capacity {W}
        8.00,                    !- Reference COP {W/W}
        6.11,                    !- Reference Leaving Chilled Water Temperature {C}
        12.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.04757,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.07003,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 1776kW/8.00COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1776kW/8.00COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1776kW/8.00COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.17,                    !- Minimum Part Load Ratio
        1.04,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.17,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.04 | Maximum part load ratio
Real | PLRMinUnl | 0.17 | Minimum part unload ratio
Real | PLRMin | 0.17 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 12.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1775900 | Reference capacity (negative number) [W]
Real | COP_nominal | 8.00 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.04757 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.07003 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.11 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {4.841535E-01,-3.584260E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {8.006719E-01,-3.137026E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {3.276235E-01,2.787167E-01,3... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 6.11 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_1776kW_8_00COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1775900, COP_nominal = 8.00, PLRMin = 0.17, PLRMinUnl = 0.17, PLRMax = 1.04, mEva_flow_nominal = 1000 * 0.04757, mCon_flow_nominal = 1000 * 0.07003, TEvaLvg_nominal = 273.15 + 6.11, TConEnt_nominal = 273.15 + 12.78, TEvaLvgMin = 273.15 + 6.11, TEvaLvgMax = 273.15 + 12.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {4.841535E-01,-3.584260E-02,-1.467417E-03,7.773868E-02,-3.125809E-03,3.729631E-03}, EIRFunT = {8.006719E-01,-3.137026E-02,4.098888E-04,3.176921E-02,-2.104567E-04,-7.660277E-05}, EIRFunPLR = {3.276235E-01,2.787167E-01,3.952405E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 1776kW/8.00COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XL_1779kW_6_18COP_Vanes

ElectricEIRChiller Carrier 19XL 1779kW/6.18COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XL 1779kW/6.18COP/Vanes,  !- Name
        1779400,                 !- Reference Capacity {W}
        6.18,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        26.11,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.06303,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.08858,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XL 1779kW/6.18COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XL 1779kW/6.18COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XL 1779kW/6.18COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.11 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1779400 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.18 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.06303 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.08858 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {2.703515E-01,-4.051337E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.872331E-01,-3.907248E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {3.090532E-01,2.641442E-01,4... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 15.56 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 26.11 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XL_1779kW_6_18COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1779400, COP_nominal = 6.18, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.06303, mCon_flow_nominal = 1000 * 0.08858, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 26.11, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 15.56, TConEntMax = 273.15 + 26.11, capFunT = {2.703515E-01,-4.051337E-02,-5.968813E-03,8.261488E-02,-3.019425E-03,6.718040E-03}, EIRFunT = {5.872331E-01,-3.907248E-02,3.474913E-04,2.950392E-02,-2.510016E-04,2.481610E-04}, EIRFunPLR = {3.090532E-01,2.641442E-01,4.269265E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XL 1779kW/6.18COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_CVHF_1779kW_6_18COP_Vanes

ElectricEIRChiller Trane CVHF 1779kW/6.18COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane CVHF 1779kW/6.18COP/Vanes,  !- Name
        1779400,                 !- Reference Capacity {W}
        6.18,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.04454,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.05142,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane CVHF 1779kW/6.18COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHF 1779kW/6.18COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHF 1779kW/6.18COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1779400 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.18 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.04454 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.05142 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {3.331346E-01,-5.678656E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {3.137523E-01,-1.879556E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.699409E-01,1.874304E-01,6... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 18.33 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_CVHF_1779kW_6_18COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1779400, COP_nominal = 6.18, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.04454, mCon_flow_nominal = 1000 * 0.05142, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 18.33, TConEntMax = 273.15 + 23.89, capFunT = {3.331346E-01,-5.678656E-02,-1.257764E-03,8.198893E-02,-2.612490E-03,4.226087E-03}, EIRFunT = {3.137523E-01,-1.879556E-02,-1.860907E-03,3.469711E-02,-1.503480E-04,7.641242E-04}, EIRFunPLR = {1.699409E-01,1.874304E-01,6.410385E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane CVHF 1779kW/6.18COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YT_1794kW_8_11COP_Vanes

ElectricEIRChiller York YT 1794kW/8.11COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YT 1794kW/8.11COP/Vanes,  !- Name
        1793500,                 !- Reference Capacity {W}
        8.11,                    !- Reference COP {W/W}
        7.22,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.05148,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.09653,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YT 1794kW/8.11COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YT 1794kW/8.11COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YT 1794kW/8.11COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.08,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.08 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1793500 | Reference capacity (negative number) [W]
Real | COP_nominal | 8.11 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.05148 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.09653 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 7.22 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.536140E+00,-1.630760E-01,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {8.546274E-01,2.456473E-01,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {3.187543E-02,8.272483E-01,1... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YT_1794kW_8_11COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1793500, COP_nominal = 8.11, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.08, mEva_flow_nominal = 1000 * 0.05148, mCon_flow_nominal = 1000 * 0.09653, TEvaLvg_nominal = 273.15 + 7.22, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {1.536140E+00,-1.630760E-01,1.225832E-02,2.148166E-02,-1.654700E-03,2.660568E-03}, EIRFunT = {8.546274E-01,2.456473E-01,-9.770595E-03,-7.386557E-02,2.843499E-03,-5.292981E-03}, EIRFunPLR = {3.187543E-02,8.272483E-01,1.279099E-01}, etaMotor = 1.0) "ElectricEIRChiller York YT 1794kW/8.11COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YT_1794kW_7_90COP_VSD

ElectricEIRChiller York YT 1794kW/7.90COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YT 1794kW/7.90COP/VSD,  !- Name
        1793500,                 !- Reference Capacity {W}
        7.90,                    !- Reference COP {W/W}
        7.22,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.05148,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.09653,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YT 1794kW/7.90COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YT 1794kW/7.90COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YT 1794kW/7.90COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.05,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.05 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1793500 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.90 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.05148 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.09653 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 7.22 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {9.552268E-01,-1.553435E-01,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.984829E-01,-1.552700E-01,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.445880E-01,1.059293E-01,7... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YT_1794kW_7_90COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1793500, COP_nominal = 7.90, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.05, mEva_flow_nominal = 1000 * 0.05148, mCon_flow_nominal = 1000 * 0.09653, TEvaLvg_nominal = 273.15 + 7.22, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {9.552268E-01,-1.553435E-01,7.958834E-03,6.132388E-02,-1.899594E-03,3.323245E-03}, EIRFunT = {5.984829E-01,-1.552700E-01,6.909012E-03,6.801572E-02,-7.450754E-04,5.764600E-04}, EIRFunPLR = {1.445880E-01,1.059293E-01,7.489704E-01}, etaMotor = 1.0) "ElectricEIRChiller York YT 1794kW/7.90COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XL_1797kW_5_69COP_Vanes

ElectricEIRChiller Carrier 19XL 1797kW/5.69COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XL 1797kW/5.69COP/Vanes,  !- Name
        1797000,                 !- Reference Capacity {W}
        5.69,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        29.44,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.07737,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.09672,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XL 1797kW/5.69COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XL 1797kW/5.69COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XL 1797kW/5.69COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.39,                    !- Minimum Part Load Ratio
        1.01,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.39,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.01 | Maximum part load ratio
Real | PLRMinUnl | 0.39 | Minimum part unload ratio
Real | PLRMin | 0.39 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 29.44 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1797000 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.69 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.07737 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.09672 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {9.084596E-01,4.671596E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {1.084290E+00,-4.318103E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {5.926251E-01,-2.657314E-01,... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 6.67 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 21.11 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XL_1797kW_5_69COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1797000, COP_nominal = 5.69, PLRMin = 0.39, PLRMinUnl = 0.39, PLRMax = 1.01, mEva_flow_nominal = 1000 * 0.07737, mCon_flow_nominal = 1000 * 0.09672, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 29.44, TEvaLvgMin = 273.15 + 6.67, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 21.11, TConEntMax = 273.15 + 29.44, capFunT = {9.084596E-01,4.671596E-02,-1.188845E-03,-2.284596E-03,-3.170254E-05,-3.577858E-04}, EIRFunT = {1.084290E+00,-4.318103E-02,1.586113E-03,1.664015E-03,8.043383E-05,5.681056E-05}, EIRFunPLR = {5.926251E-01,-2.657314E-01,6.731751E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XL 1797kW/5.69COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_1801kW_6_34COP_VSD

ElectricEIRChiller Carrier 19XR 1801kW/6.34COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 1801kW/6.34COP/VSD,  !- Name
        1800500,                 !- Reference Capacity {W}
        6.34,                    !- Reference COP {W/W}
        7.22,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.05161,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.06385,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 1801kW/6.34COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1801kW/6.34COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 1801kW/6.34COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1800500 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.34 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.05161 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.06385 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 7.22 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {6.174861E-01,-7.299051E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {6.931082E-01,-1.885558E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.040764E-01,2.818752E-01,6... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 6.67 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.22 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_1801kW_6_34COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1800500, COP_nominal = 6.34, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.05161, mCon_flow_nominal = 1000 * 0.06385, TEvaLvg_nominal = 273.15 + 7.22, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 6.67, TEvaLvgMax = 273.15 + 12.22, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {6.174861E-01,-7.299051E-02,-1.897105E-03,7.003662E-02,-2.852439E-03,5.751931E-03}, EIRFunT = {6.931082E-01,-1.885558E-02,8.345461E-04,1.263879E-02,4.588028E-04,-8.221467E-04}, EIRFunPLR = {1.040764E-01,2.818752E-01,6.144036E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 1801kW/6.34COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YT_1867kW_10_09COP_Vanes

ElectricEIRChiller York YT 1867kW/10.09COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YT 1867kW/10.09COP/Vanes,  !- Name
        1867300,                 !- Reference Capacity {W}
        10.09,                   !- Reference COP {W/W}
        7.78,                    !- Reference Leaving Chilled Water Temperature {C}
        12.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.07571,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.09085,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YT 1867kW/10.09COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YT 1867kW/10.09COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YT 1867kW/10.09COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.09,                    !- Minimum Part Load Ratio
        1.04,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.09,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.04 | Maximum part load ratio
Real | PLRMinUnl | 0.09 | Minimum part unload ratio
Real | PLRMin | 0.09 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 12.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1867300 | Reference capacity (negative number) [W]
Real | COP_nominal | 10.09 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.07571 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.09085 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 7.78 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {4.451516E-01,-1.252382E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {6.668391E-01,1.506485E-02,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.157002E-01,2.251016E-01,5... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 35.00 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YT_1867kW_10_09COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1867300, COP_nominal = 10.09, PLRMin = 0.09, PLRMinUnl = 0.09, PLRMax = 1.04, mEva_flow_nominal = 1000 * 0.07571, mCon_flow_nominal = 1000 * 0.09085, TEvaLvg_nominal = 273.15 + 7.78, TConEnt_nominal = 273.15 + 12.78, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 35.00, capFunT = {4.451516E-01,-1.252382E-02,-2.878042E-03,6.132233E-02,-2.365055E-03,4.514258E-03}, EIRFunT = {6.668391E-01,1.506485E-02,-4.249134E-03,3.588996E-02,-1.681591E-04,7.028459E-04}, EIRFunPLR = {2.157002E-01,2.251016E-01,5.584287E-01}, etaMotor = 1.0) "ElectricEIRChiller York YT 1867kW/10.09COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XL_1871kW_6_49COP_Vanes

ElectricEIRChiller Carrier 19XL 1871kW/6.49COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XL 1871kW/6.49COP/Vanes,  !- Name
        1870800,                 !- Reference Capacity {W}
        6.49,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        26.11,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.06303,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.0877,                  !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XL 1871kW/6.49COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XL 1871kW/6.49COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XL 1871kW/6.49COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.19,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.19,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.19 | Minimum part unload ratio
Real | PLRMin | 0.19 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.11 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1870800 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.49 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.06303 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.0877 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {5.658630E-03,-3.836575E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {1.029608E+00,-7.149045E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.984908E-01,2.906868E-01,4... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 15.56 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XL_1871kW_6_49COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1870800, COP_nominal = 6.49, PLRMin = 0.19, PLRMinUnl = 0.19, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.06303, mCon_flow_nominal = 1000 * 0.0877, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 26.11, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 15.56, TConEntMax = 273.15 + 29.44, capFunT = {5.658630E-03,-3.836575E-02,-5.122195E-03,1.068063E-01,-3.377824E-03,5.650118E-03}, EIRFunT = {1.029608E+00,-7.149045E-02,2.043279E-03,-6.116474E-04,3.908334E-04,6.870233E-04}, EIRFunPLR = {2.984908E-01,2.906868E-01,4.089411E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XL 1871kW/6.49COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YT_1881kW_6_77COP_VSD

ElectricEIRChiller York YT 1881kW/6.77COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YT 1881kW/6.77COP/VSD,  !- Name
        1881400,                 !- Reference Capacity {W}
        6.77,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.07571,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.09464,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YT 1881kW/6.77COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YT 1881kW/6.77COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YT 1881kW/6.77COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.09,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.09,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.09 | Minimum part unload ratio
Real | PLRMin | 0.09 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1881400 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.77 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.07571 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.09464 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {5.065247E-01,-4.158206E-03,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {6.175311E-01,-3.913241E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {6.087656E-02,4.842164E-01,4... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YT_1881kW_6_77COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1881400, COP_nominal = 6.77, PLRMin = 0.09, PLRMinUnl = 0.09, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.07571, mCon_flow_nominal = 1000 * 0.09464, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {5.065247E-01,-4.158206E-03,-2.681976E-03,4.763436E-02,-1.951270E-03,3.994399E-03}, EIRFunT = {6.175311E-01,-3.913241E-02,6.177961E-04,2.775640E-02,-2.151466E-04,5.514895E-04}, EIRFunPLR = {6.087656E-02,4.842164E-01,4.571519E-01}, etaMotor = 1.0) "ElectricEIRChiller York YT 1881kW/6.77COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YK_1881kW_6_53COP_Vanes

ElectricEIRChiller York YK 1881kW/6.53COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YK 1881kW/6.53COP/Vanes,  !- Name
        1881400,                 !- Reference Capacity {W}
        6.53,                    !- Reference COP {W/W}
        8.89,                    !- Reference Leaving Chilled Water Temperature {C}
        26.67,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.04397,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.1041,                  !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YK 1881kW/6.53COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YK 1881kW/6.53COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YK 1881kW/6.53COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.19,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.19,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.19 | Minimum part unload ratio
Real | PLRMin | 0.19 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.67 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1881400 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.53 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.04397 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.1041 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 8.89 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {8.561286E-01,4.130164E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {4.434989E-01,4.361264E-02,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {5.272116E-02,4.176382E-01,5... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 7.22 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 9.44 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 26.67 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YK_1881kW_6_53COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1881400, COP_nominal = 6.53, PLRMin = 0.19, PLRMinUnl = 0.19, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.04397, mCon_flow_nominal = 1000 * 0.1041, TEvaLvg_nominal = 273.15 + 8.89, TConEnt_nominal = 273.15 + 26.67, TEvaLvgMin = 273.15 + 7.22, TEvaLvgMax = 273.15 + 12.78, TConEntMin = 273.15 + 9.44, TConEntMax = 273.15 + 26.67, capFunT = {8.561286E-01,4.130164E-02,-7.109335E-04,4.306273E-03,-6.336613E-04,7.211635E-04}, EIRFunT = {4.434989E-01,4.361264E-02,-1.733337E-03,9.915503E-03,4.312717E-04,-1.122346E-03}, EIRFunPLR = {5.272116E-02,4.176382E-01,5.310870E-01}, etaMotor = 1.0) "ElectricEIRChiller York YK 1881kW/6.53COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_McQuay_PEH_1895kW_6_42COP_Vanes

ElectricEIRChiller McQuay PEH 1895kW/6.42COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller McQuay PEH 1895kW/6.42COP/Vanes,  !- Name
        1895400,                 !- Reference Capacity {W}
        6.42,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.07571,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.09085,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller McQuay PEH 1895kW/6.42COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller McQuay PEH 1895kW/6.42COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller McQuay PEH 1895kW/6.42COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.09,                    !- Minimum Part Load Ratio
        1.09,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.09,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.09 | Maximum part load ratio
Real | PLRMinUnl | 0.09 | Minimum part unload ratio
Real | PLRMin | 0.09 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1895400 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.42 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.07571 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.09085 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {8.573195E-01,-1.131937E-01,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {3.915073E-01,-4.399727E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.592598E-01,1.425462E-01,5... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 35.00 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_McQuay_PEH_1895kW_6_42COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1895400, COP_nominal = 6.42, PLRMin = 0.09, PLRMinUnl = 0.09, PLRMax = 1.09, mEva_flow_nominal = 1000 * 0.07571, mCon_flow_nominal = 1000 * 0.09085, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 35.00, capFunT = {8.573195E-01,-1.131937E-01,3.444205E-03,4.865045E-02,-2.103805E-03,4.986639E-03}, EIRFunT = {3.915073E-01,-4.399727E-02,-3.868294E-06,4.623771E-02,-7.092319E-04,1.372133E-03}, EIRFunPLR = {2.592598E-01,1.425462E-01,5.966041E-01}, etaMotor = 1.0) "ElectricEIRChiller McQuay PEH 1895kW/6.42COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YT_1934kW_7_55COP_Vanes

ElectricEIRChiller York YT 1934kW/7.55COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YT 1934kW/7.55COP/Vanes,  !- Name
        1934100,                 !- Reference Capacity {W}
        7.55,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        13.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.05552,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.08675,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YT 1934kW/7.55COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YT 1934kW/7.55COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YT 1934kW/7.55COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.06,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.06 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 13.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1934100 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.55 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.05552 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.08675 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {4.420318E-02,1.103599E-01,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {1.173674E+00,-1.301647E-01,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.706237E-01,6.063362E-01,2... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YT_1934kW_7_55COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1934100, COP_nominal = 7.55, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.06, mEva_flow_nominal = 1000 * 0.05552, mCon_flow_nominal = 1000 * 0.08675, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 13.89, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {4.420318E-02,1.103599E-01,-2.597752E-03,7.043754E-02,-2.138316E-03,-4.696924E-04}, EIRFunT = {1.173674E+00,-1.301647E-01,5.588446E-03,8.605153E-03,7.234201E-05,1.314581E-03}, EIRFunPLR = {1.706237E-01,6.063362E-01,2.170672E-01}, etaMotor = 1.0) "ElectricEIRChiller York YT 1934kW/7.55COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_McQuay_PEH_1934kW_6_01COP_Vanes

ElectricEIRChiller McQuay PEH 1934kW/6.01COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller McQuay PEH 1934kW/6.01COP/Vanes,  !- Name
        1934100,                 !- Reference Capacity {W}
        6.01,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        22.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.05552,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.07981,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller McQuay PEH 1934kW/6.01COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller McQuay PEH 1934kW/6.01COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller McQuay PEH 1934kW/6.01COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.08,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.08 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 22.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1934100 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.01 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.05552 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.07981 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {2.893111E-01,-3.834949E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {2.885371E-01,-5.877829E-03,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {3.849256E-01,-2.369152E-01,... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_McQuay_PEH_1934kW_6_01COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1934100, COP_nominal = 6.01, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.08, mEva_flow_nominal = 1000 * 0.05552, mCon_flow_nominal = 1000 * 0.07981, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 22.78, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {2.893111E-01,-3.834949E-02,1.757934E-03,8.665805E-02,-2.597243E-03,2.413315E-03}, EIRFunT = {2.885371E-01,-5.877829E-03,-1.807763E-03,5.193076E-02,-7.936373E-04,1.108590E-03}, EIRFunPLR = {3.849256E-01,-2.369152E-01,8.496351E-01}, etaMotor = 1.0) "ElectricEIRChiller McQuay PEH 1934kW/6.01COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_McQuay_WDC_1973kW_6_28COP_Vanes

ElectricEIRChiller McQuay WDC 1973kW/6.28COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller McQuay WDC 1973kW/6.28COP/Vanes,  !- Name
        1972800,                 !- Reference Capacity {W}
        6.28,                    !- Reference COP {W/W}
        8.89,                    !- Reference Leaving Chilled Water Temperature {C}
        26.67,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.04145,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.09337,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller McQuay WDC 1973kW/6.28COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller McQuay WDC 1973kW/6.28COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller McQuay WDC 1973kW/6.28COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.09,                    !- Minimum Part Load Ratio
        1.06,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.09,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.06 | Maximum part load ratio
Real | PLRMinUnl | 0.09 | Minimum part unload ratio
Real | PLRMin | 0.09 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.67 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1972800 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.28 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.04145 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.09337 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 8.89 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.110884E+00,7.376077E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {1.097378E+00,-3.018324E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.282891E-01,2.722981E-01,6... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 7.22 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 26.67 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_McQuay_WDC_1973kW_6_28COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1972800, COP_nominal = 6.28, PLRMin = 0.09, PLRMinUnl = 0.09, PLRMax = 1.06, mEva_flow_nominal = 1000 * 0.04145, mCon_flow_nominal = 1000 * 0.09337, TEvaLvg_nominal = 273.15 + 8.89, TConEnt_nominal = 273.15 + 26.67, TEvaLvgMin = 273.15 + 7.22, TEvaLvgMax = 273.15 + 12.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 26.67, capFunT = {1.110884E+00,7.376077E-02,-5.957719E-03,-2.861037E-02,-2.129104E-04,2.547028E-03}, EIRFunT = {1.097378E+00,-3.018324E-02,-2.792200E-03,-1.252428E-02,2.095232E-04,2.409252E-03}, EIRFunPLR = {1.282891E-01,2.722981E-01,6.012232E-01}, etaMotor = 1.0) "ElectricEIRChiller McQuay WDC 1973kW/6.28COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YK_1997kW_7_24COP_Vanes

ElectricEIRChiller York YK 1997kW/7.24COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YK 1997kW/7.24COP/Vanes,  !- Name
        1997400,                 !- Reference Capacity {W}
        7.24,                    !- Reference COP {W/W}
        8.89,                    !- Reference Leaving Chilled Water Temperature {C}
        26.67,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.04397,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.1041,                  !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YK 1997kW/7.24COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YK 1997kW/7.24COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YK 1997kW/7.24COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.18,                    !- Minimum Part Load Ratio
        1.06,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.18,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.06 | Maximum part load ratio
Real | PLRMinUnl | 0.18 | Minimum part unload ratio
Real | PLRMin | 0.18 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.67 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1997400 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.24 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.04397 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.1041 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 8.89 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {9.058272E-01,1.309175E-01,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {1.188194E-01,8.769791E-02,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {9.359332E-02,5.873752E-01,3... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 7.22 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 26.67 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YK_1997kW_7_24COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1997400, COP_nominal = 7.24, PLRMin = 0.18, PLRMinUnl = 0.18, PLRMax = 1.06, mEva_flow_nominal = 1000 * 0.04397, mCon_flow_nominal = 1000 * 0.1041, TEvaLvg_nominal = 273.15 + 8.89, TConEnt_nominal = 273.15 + 26.67, TEvaLvgMin = 273.15 + 7.22, TEvaLvgMax = 273.15 + 12.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 26.67, capFunT = {9.058272E-01,1.309175E-01,-3.446620E-03,-3.166792E-02,2.325200E-04,-4.892256E-04}, EIRFunT = {1.188194E-01,8.769791E-02,-1.692086E-03,2.209962E-03,1.327958E-03,-3.249833E-03}, EIRFunPLR = {9.359332E-02,5.873752E-01,3.208990E-01}, etaMotor = 1.0) "ElectricEIRChiller York YK 1997kW/7.24COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_McQuay_PFH_2043kW_8_44COP_Vanes

ElectricEIRChiller McQuay PFH 2043kW/8.44COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller McQuay PFH 2043kW/8.44COP/Vanes,  !- Name
        2043100,                 !- Reference Capacity {W}
        8.44,                    !- Reference COP {W/W}
        6.11,                    !- Reference Leaving Chilled Water Temperature {C}
        12.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.04757,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.06814,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller McQuay PFH 2043kW/8.44COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller McQuay PFH 2043kW/8.44COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller McQuay PFH 2043kW/8.44COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.08,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.08,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.08 | Minimum part unload ratio
Real | PLRMin | 0.08 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 12.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -2043100 | Reference capacity (negative number) [W]
Real | COP_nominal | 8.44 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.04757 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.06814 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.11 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {8.383569E-01,4.716323E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {7.891693E-01,1.168677E-02,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.225600E-01,3.070007E-01,5... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 6.11 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_McQuay_PFH_2043kW_8_44COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -2043100, COP_nominal = 8.44, PLRMin = 0.08, PLRMinUnl = 0.08, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.04757, mCon_flow_nominal = 1000 * 0.06814, TEvaLvg_nominal = 273.15 + 6.11, TConEnt_nominal = 273.15 + 12.78, TEvaLvgMin = 273.15 + 6.11, TEvaLvgMax = 273.15 + 12.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {8.383569E-01,4.716323E-02,-2.515385E-03,-3.773603E-03,-9.186324E-04,2.177057E-03}, EIRFunT = {7.891693E-01,1.168677E-02,-1.825470E-03,1.278749E-02,1.521317E-04,2.156746E-04}, EIRFunPLR = {1.225600E-01,3.070007E-01,5.712759E-01}, etaMotor = 1.0) "ElectricEIRChiller McQuay PFH 2043kW/8.44COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_CVHF_2043kW_9_08COP_Vanes

ElectricEIRChiller Trane CVHF 2043kW/9.08COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane CVHF 2043kW/9.08COP/Vanes,  !- Name
        2043100,                 !- Reference Capacity {W}
        9.08,                    !- Reference COP {W/W}
        4.44,                    !- Reference Leaving Chilled Water Temperature {C}
        18.33,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.09085,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.11356,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane CVHF 2043kW/9.08COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHF 2043kW/9.08COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHF 2043kW/9.08COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.28,                    !- Minimum Part Load Ratio
        1.04,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.28,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.04 | Maximum part load ratio
Real | PLRMinUnl | 0.28 | Minimum part unload ratio
Real | PLRMin | 0.28 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 18.33 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -2043100 | Reference capacity (negative number) [W]
Real | COP_nominal | 9.08 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.09085 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.11356 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 4.44 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {-1.340241E+00,7.634284E-03,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {6.065177E-01,1.178669E-02,2... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.173752E-01,4.394720E-01,3... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 18.33 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_CVHF_2043kW_9_08COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -2043100, COP_nominal = 9.08, PLRMin = 0.28, PLRMinUnl = 0.28, PLRMax = 1.04, mEva_flow_nominal = 1000 * 0.09085, mCon_flow_nominal = 1000 * 0.11356, TEvaLvg_nominal = 273.15 + 4.44, TConEnt_nominal = 273.15 + 18.33, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 18.33, TConEntMax = 273.15 + 29.44, capFunT = {-1.340241E+00,7.634284E-03,-3.044184E-03,1.991327E-01,-4.530240E-03,2.700765E-03}, EIRFunT = {6.065177E-01,1.178669E-02,2.098586E-03,1.532536E-02,6.756887E-04,-2.629852E-03}, EIRFunPLR = {2.173752E-01,4.394720E-01,3.431813E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane CVHF 2043kW/9.08COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XL_2057kW_6_05COP_Vanes

ElectricEIRChiller Carrier 19XL 2057kW/6.05COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XL 2057kW/6.05COP/Vanes,  !- Name
        2057200,                 !- Reference Capacity {W}
        6.05,                    !- Reference COP {W/W}
        7.78,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.08322,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.09722,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XL 2057kW/6.05COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XL 2057kW/6.05COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XL 2057kW/6.05COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.28,                    !- Minimum Part Load Ratio
        1.04,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.28,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.04 | Maximum part load ratio
Real | PLRMinUnl | 0.28 | Minimum part unload ratio
Real | PLRMin | 0.28 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -2057200 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.05 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.08322 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.09722 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 7.78 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {7.737452E-01,-1.249478E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {8.623086E-01,-5.844490E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {4.041274E-01,-3.861525E-01,... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XL_2057kW_6_05COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -2057200, COP_nominal = 6.05, PLRMin = 0.28, PLRMinUnl = 0.28, PLRMax = 1.04, mEva_flow_nominal = 1000 * 0.08322, mCon_flow_nominal = 1000 * 0.09722, TEvaLvg_nominal = 273.15 + 7.78, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {7.737452E-01,-1.249478E-02,-3.193419E-03,2.110302E-02,-1.188413E-03,3.820335E-03}, EIRFunT = {8.623086E-01,-5.844490E-02,-2.284745E-03,2.469188E-02,-1.022604E-03,3.996523E-03}, EIRFunPLR = {4.041274E-01,-3.861525E-01,9.804493E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XL 2057kW/6.05COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YT_2110kW_7_15COP_Vanes

ElectricEIRChiller York YT 2110kW/7.15COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YT 2110kW/7.15COP/Vanes,  !- Name
        2110000,                 !- Reference Capacity {W}
        7.15,                    !- Reference COP {W/W}
        7.22,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.06057,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.09464,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YT 2110kW/7.15COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YT 2110kW/7.15COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YT 2110kW/7.15COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.04,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.04 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -2110000 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.15 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.06057 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.09464 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 7.22 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {5.359238E-01,1.785857E-02,1... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {6.270855E-01,-4.119654E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.469187E-01,1.862690E-01,5... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YT_2110kW_7_15COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -2110000, COP_nominal = 7.15, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.04, mEva_flow_nominal = 1000 * 0.06057, mCon_flow_nominal = 1000 * 0.09464, TEvaLvg_nominal = 273.15 + 7.22, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {5.359238E-01,1.785857E-02,1.579272E-03,4.522868E-02,-1.632172E-03,6.008061E-04}, EIRFunT = {6.270855E-01,-4.119654E-02,1.327107E-03,2.661446E-02,-1.856827E-04,5.094942E-04}, EIRFunPLR = {2.469187E-01,1.862690E-01,5.660904E-01}, etaMotor = 1.0) "ElectricEIRChiller York YT 2110kW/7.15COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_McQuay_PFH_2124kW_6_03COP_Vanes

ElectricEIRChiller McQuay PFH 2124kW/6.03COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller McQuay PFH 2124kW/6.03COP/Vanes,  !- Name
        2124000,                 !- Reference Capacity {W}
        6.03,                    !- Reference COP {W/W}
        8.89,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.05552,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.07981,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller McQuay PFH 2124kW/6.03COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller McQuay PFH 2124kW/6.03COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller McQuay PFH 2124kW/6.03COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.09,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.09,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.09 | Minimum part unload ratio
Real | PLRMin | 0.09 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -2124000 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.03 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.05552 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.07981 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 8.89 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.040134E+00,-1.745650E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {1.157799E+00,-3.621524E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.051419E-01,2.033679E-01,6... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_McQuay_PFH_2124kW_6_03COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -2124000, COP_nominal = 6.03, PLRMin = 0.09, PLRMinUnl = 0.09, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.05552, mCon_flow_nominal = 1000 * 0.07981, TEvaLvg_nominal = 273.15 + 8.89, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {1.040134E+00,-1.745650E-02,1.084856E-03,6.629328E-03,-8.008991E-04,1.567769E-03}, EIRFunT = {1.157799E+00,-3.621524E-02,-3.684818E-03,-1.202959E-02,-7.378548E-05,3.787365E-03}, EIRFunPLR = {1.051419E-01,2.033679E-01,6.902026E-01}, etaMotor = 1.0) "ElectricEIRChiller McQuay PFH 2124kW/6.03COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YK_2159kW_6_85COP_Vanes

ElectricEIRChiller York YK 2159kW/6.85COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YK 2159kW/6.85COP/Vanes,  !- Name
        2159200,                 !- Reference Capacity {W}
        6.85,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        26.11,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.07571,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.11356,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YK 2159kW/6.85COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YK 2159kW/6.85COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YK 2159kW/6.85COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.14,                    !- Minimum Part Load Ratio
        1.05,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.14,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.05 | Maximum part load ratio
Real | PLRMinUnl | 0.14 | Minimum part unload ratio
Real | PLRMin | 0.14 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.11 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -2159200 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.85 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.07571 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.11356 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {6.322235E-01,1.553954E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {9.106730E-01,-3.786410E-03,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.595694E-01,1.889684E-01,5... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 15.56 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YK_2159kW_6_85COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -2159200, COP_nominal = 6.85, PLRMin = 0.14, PLRMinUnl = 0.14, PLRMax = 1.05, mEva_flow_nominal = 1000 * 0.07571, mCon_flow_nominal = 1000 * 0.11356, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 26.11, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 15.56, TConEntMax = 273.15 + 29.44, capFunT = {6.322235E-01,1.553954E-02,-9.149770E-03,5.284289E-02,-2.818835E-03,7.074096E-03}, EIRFunT = {9.106730E-01,-3.786410E-03,-1.084261E-03,-7.148246E-03,5.178799E-04,1.818623E-05}, EIRFunPLR = {2.595694E-01,1.889684E-01,5.518450E-01}, etaMotor = 1.0) "ElectricEIRChiller York YK 2159kW/6.85COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_CVHF_2184kW_6_78COP_Vanes

ElectricEIRChiller Trane CVHF 2184kW/6.78COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane CVHF 2184kW/6.78COP/Vanes,  !- Name
        2183800,                 !- Reference Capacity {W}
        6.78,                    !- Reference COP {W/W}
        7.78,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.04883,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.05142,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane CVHF 2184kW/6.78COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHF 2184kW/6.78COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHF 2184kW/6.78COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.09,                    !- Minimum Part Load Ratio
        1.01,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.09,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.01 | Maximum part load ratio
Real | PLRMinUnl | 0.09 | Minimum part unload ratio
Real | PLRMin | 0.09 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -2183800 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.78 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.04883 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.05142 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 7.78 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.235680E+00,2.213527E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {8.877947E-01,-1.334886E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {8.942647E-02,5.249540E-01,3... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 18.33 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_CVHF_2184kW_6_78COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -2183800, COP_nominal = 6.78, PLRMin = 0.09, PLRMinUnl = 0.09, PLRMax = 1.01, mEva_flow_nominal = 1000 * 0.04883, mCon_flow_nominal = 1000 * 0.05142, TEvaLvg_nominal = 273.15 + 7.78, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 18.33, TConEntMax = 273.15 + 23.89, capFunT = {1.235680E+00,2.213527E-02,-1.770186E-03,-1.131594E-02,-5.008696E-04,1.356522E-03}, EIRFunT = {8.877947E-01,-1.334886E-02,1.689581E-03,-1.599710E-03,7.884945E-04,-1.584900E-03}, EIRFunPLR = {8.942647E-02,5.249540E-01,3.850801E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane CVHF 2184kW/6.78COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YK_2201kW_6_69COP_Vanes

ElectricEIRChiller York YK 2201kW/6.69COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YK 2201kW/6.69COP/Vanes,  !- Name
        2201400,                 !- Reference Capacity {W}
        6.69,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        26.11,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.07571,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.11356,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YK 2201kW/6.69COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YK 2201kW/6.69COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YK 2201kW/6.69COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.14,                    !- Minimum Part Load Ratio
        1.05,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.14,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.05 | Maximum part load ratio
Real | PLRMinUnl | 0.14 | Minimum part unload ratio
Real | PLRMin | 0.14 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.11 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -2201400 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.69 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.07571 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.11356 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {5.474968E-01,-4.800356E-03,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {8.234137E-01,1.308264E-02,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.653493E-01,1.444620E-01,5... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 15.56 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YK_2201kW_6_69COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -2201400, COP_nominal = 6.69, PLRMin = 0.14, PLRMinUnl = 0.14, PLRMax = 1.05, mEva_flow_nominal = 1000 * 0.07571, mCon_flow_nominal = 1000 * 0.11356, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 26.11, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 15.56, TConEntMax = 273.15 + 29.44, capFunT = {5.474968E-01,-4.800356E-03,-6.845886E-03,6.302552E-02,-2.911528E-03,6.598690E-03}, EIRFunT = {8.234137E-01,1.308264E-02,-1.147806E-03,-4.071161E-03,5.220869E-04,-6.312495E-04}, EIRFunPLR = {2.653493E-01,1.444620E-01,5.911158E-01}, etaMotor = 1.0) "ElectricEIRChiller York YK 2201kW/6.69COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YT_2233kW_9_54COP_VSD

ElectricEIRChiller York YT 2233kW/9.54COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YT 2233kW/9.54COP/VSD,  !- Name
        2233000,                 !- Reference Capacity {W}
        9.54,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        12.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.06107,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.11451,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YT 2233kW/9.54COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YT 2233kW/9.54COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YT 2233kW/9.54COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.04,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.04 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 12.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -2233000 | Reference capacity (negative number) [W]
Real | COP_nominal | 9.54 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.06107 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.11451 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {7.585741E-01,-5.127829E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {7.563409E-01,-1.966623E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {6.917141E-02,1.743339E-01,7... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YT_2233kW_9_54COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -2233000, COP_nominal = 9.54, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.04, mEva_flow_nominal = 1000 * 0.06107, mCon_flow_nominal = 1000 * 0.11451, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 12.78, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {7.585741E-01,-5.127829E-02,5.848602E-03,4.235544E-02,-1.606561E-03,9.364594E-04}, EIRFunT = {7.563409E-01,-1.966623E-02,-3.927494E-04,2.973607E-02,1.299230E-04,-4.325357E-04}, EIRFunPLR = {6.917141E-02,1.743339E-01,7.524059E-01}, etaMotor = 1.0) "ElectricEIRChiller York YT 2233kW/9.54COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YK_2237kW_6_41COP_Vanes

ElectricEIRChiller York YK 2237kW/6.41COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YK 2237kW/6.41COP/Vanes,  !- Name
        2236600,                 !- Reference Capacity {W}
        6.41,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        26.11,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.07571,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.11356,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YK 2237kW/6.41COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YK 2237kW/6.41COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YK 2237kW/6.41COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.13,                    !- Minimum Part Load Ratio
        1.01,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.13,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.01 | Maximum part load ratio
Real | PLRMinUnl | 0.13 | Minimum part unload ratio
Real | PLRMin | 0.13 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.11 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -2236600 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.41 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.07571 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.11356 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {6.899710E-01,-1.413334E-03,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {8.567950E-01,3.354557E-03,1... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.605354E-01,2.125571E-01,5... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 15.56 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YK_2237kW_6_41COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -2236600, COP_nominal = 6.41, PLRMin = 0.13, PLRMinUnl = 0.13, PLRMax = 1.01, mEva_flow_nominal = 1000 * 0.07571, mCon_flow_nominal = 1000 * 0.11356, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 26.11, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 15.56, TConEntMax = 273.15 + 29.44, capFunT = {6.899710E-01,-1.413334E-03,-1.109323E-03,4.078120E-02,-1.785625E-03,2.977821E-03}, EIRFunT = {8.567950E-01,3.354557E-03,1.047901E-03,-5.217250E-03,6.565310E-04,-1.361740E-03}, EIRFunPLR = {2.605354E-01,2.125571E-01,5.269144E-01}, etaMotor = 1.0) "ElectricEIRChiller York YK 2237kW/6.41COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YK_2275kW_6_32COP_Vanes

ElectricEIRChiller York YK 2275kW/6.32COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YK 2275kW/6.32COP/Vanes,  !- Name
        2275200,                 !- Reference Capacity {W}
        6.32,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        26.11,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.07571,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.11356,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YK 2275kW/6.32COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YK 2275kW/6.32COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YK 2275kW/6.32COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.13,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.13,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.13 | Minimum part unload ratio
Real | PLRMin | 0.13 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.11 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -2275200 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.32 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.07571 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.11356 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.034673E+00,-1.091064E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {8.326094E-01,-6.056615E-03,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.735485E-01,2.163041E-01,5... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YK_2275kW_6_32COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -2275200, COP_nominal = 6.32, PLRMin = 0.13, PLRMinUnl = 0.13, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.07571, mCon_flow_nominal = 1000 * 0.11356, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 26.11, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {1.034673E+00,-1.091064E-02,9.019479E-04,9.686229E-03,-9.160783E-04,2.045641E-03}, EIRFunT = {8.326094E-01,-6.056615E-03,-3.016626E-04,-2.498578E-03,4.933363E-04,-3.125632E-04}, EIRFunPLR = {2.735485E-01,2.163041E-01,5.099054E-01}, etaMotor = 1.0) "ElectricEIRChiller York YK 2275kW/6.32COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_CVHF_2300kW_8_10COP_Vanes

ElectricEIRChiller Trane CVHF 2300kW/8.10COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane CVHF 2300kW/8.10COP/Vanes,  !- Name
        2299900,                 !- Reference Capacity {W}
        8.10,                    !- Reference COP {W/W}
        4.44,                    !- Reference Leaving Chilled Water Temperature {C}
        12.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.07571,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.09085,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane CVHF 2300kW/8.10COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHF 2300kW/8.10COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHF 2300kW/8.10COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.23,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.23,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.23 | Minimum part unload ratio
Real | PLRMin | 0.23 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 12.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -2299900 | Reference capacity (negative number) [W]
Real | COP_nominal | 8.10 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.07571 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.09085 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 4.44 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {6.268137E-01,3.920902E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {7.178121E-01,6.561784E-03,8... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.161399E-01,4.347344E-01,4... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_CVHF_2300kW_8_10COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -2299900, COP_nominal = 8.10, PLRMin = 0.23, PLRMinUnl = 0.23, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.07571, mCon_flow_nominal = 1000 * 0.09085, TEvaLvg_nominal = 273.15 + 4.44, TConEnt_nominal = 273.15 + 12.78, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {6.268137E-01,3.920902E-02,-5.475881E-04,3.072669E-02,-1.474615E-03,8.577783E-04}, EIRFunT = {7.178121E-01,6.561784E-03,8.193740E-06,2.319141E-02,-1.755983E-06,-8.834410E-04}, EIRFunPLR = {1.161399E-01,4.347344E-01,4.486380E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane CVHF 2300kW/8.10COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_CVHF_2317kW_6_33COP_VSD

ElectricEIRChiller Trane CVHF 2317kW/6.33COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane CVHF 2317kW/6.33COP/VSD,  !- Name
        2317400,                 !- Reference Capacity {W}
        6.33,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        29.44,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.09085,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.11356,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane CVHF 2317kW/6.33COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHF 2317kW/6.33COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHF 2317kW/6.33COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.04,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.04 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 29.44 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -2317400 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.33 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.09085 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.11356 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {7.277716E-01,1.018101E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {3.502330E-01,-2.301510E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {9.861441E-02,5.297727E-01,3... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_CVHF_2317kW_6_33COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -2317400, COP_nominal = 6.33, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.04, mEva_flow_nominal = 1000 * 0.09085, mCon_flow_nominal = 1000 * 0.11356, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 29.44, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {7.277716E-01,1.018101E-02,-6.282438E-04,1.337701E-02,-5.050352E-04,1.527259E-03}, EIRFunT = {3.502330E-01,-2.301510E-02,5.749596E-04,1.902421E-02,3.109974E-04,-4.714517E-04}, EIRFunPLR = {9.861441E-02,5.297727E-01,3.707229E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane CVHF 2317kW/6.33COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_2391kW_6_77COP_Vanes

ElectricEIRChiller Carrier 19XR 2391kW/6.77COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 2391kW/6.77COP/Vanes,  !- Name
        2391300,                 !- Reference Capacity {W}
        6.77,                    !- Reference COP {W/W}
        7.22,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.06858,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.0846,                  !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 2391kW/6.77COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 2391kW/6.77COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 2391kW/6.77COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -2391300 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.77 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.06858 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.0846 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 7.22 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {3.676388E-01,-5.087680E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {6.266646E-01,-2.367443E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {3.036386E-01,2.524850E-01,4... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 6.67 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.22 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_2391kW_6_77COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -2391300, COP_nominal = 6.77, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.06858, mCon_flow_nominal = 1000 * 0.0846, TEvaLvg_nominal = 273.15 + 7.22, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 6.67, TEvaLvgMax = 273.15 + 12.22, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {3.676388E-01,-5.087680E-02,-1.772675E-03,9.518123E-02,-3.403878E-03,4.526983E-03}, EIRFunT = {6.266646E-01,-2.367443E-02,4.031296E-04,2.827714E-02,-1.985242E-04,-1.470260E-04}, EIRFunPLR = {3.036386E-01,2.524850E-01,4.429285E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 2391kW/6.77COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19XR_2391kW_6_44COP_VSD

ElectricEIRChiller Carrier 19XR 2391kW/6.44COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19XR 2391kW/6.44COP/VSD,  !- Name
        2391300,                 !- Reference Capacity {W}
        6.44,                    !- Reference COP {W/W}
        7.22,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.06858,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.0846,                  !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19XR 2391kW/6.44COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 2391kW/6.44COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19XR 2391kW/6.44COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -2391300 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.44 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.06858 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.0846 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 7.22 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {3.676388E-01,-5.087680E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {6.230142E-01,-2.371649E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {9.774812E-02,2.490111E-01,6... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 6.67 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.22 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19XR_2391kW_6_44COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -2391300, COP_nominal = 6.44, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.06858, mCon_flow_nominal = 1000 * 0.0846, TEvaLvg_nominal = 273.15 + 7.22, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 6.67, TEvaLvgMax = 273.15 + 12.22, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {3.676388E-01,-5.087680E-02,-1.772675E-03,9.518123E-02,-3.403878E-03,4.526983E-03}, EIRFunT = {6.230142E-01,-2.371649E-02,3.996265E-04,2.874515E-02,-2.115103E-04,-1.526191E-04}, EIRFunPLR = {9.774812E-02,2.490111E-01,6.539378E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19XR 2391kW/6.44COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YK_2412kW_5_58COP_Vanes

ElectricEIRChiller York YK 2412kW/5.58COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YK 2412kW/5.58COP/Vanes,  !- Name
        2412400,                 !- Reference Capacity {W}
        5.58,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        26.11,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.09085,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.11356,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YK 2412kW/5.58COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YK 2412kW/5.58COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YK 2412kW/5.58COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.12,                    !- Minimum Part Load Ratio
        1.01,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.12,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.01 | Maximum part load ratio
Real | PLRMinUnl | 0.12 | Minimum part unload ratio
Real | PLRMin | 0.12 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.11 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -2412400 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.58 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.09085 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.11356 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {7.473817E-01,8.069214E-03,8... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {4.626807E-01,-2.305674E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.472427E-01,7.531481E-01,8... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 15.56 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YK_2412kW_5_58COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -2412400, COP_nominal = 5.58, PLRMin = 0.12, PLRMinUnl = 0.12, PLRMax = 1.01, mEva_flow_nominal = 1000 * 0.09085, mCon_flow_nominal = 1000 * 0.11356, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 26.11, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 15.56, TConEntMax = 273.15 + 29.44, capFunT = {7.473817E-01,8.069214E-03,8.433986E-05,1.925706E-02,-7.505775E-04,1.174526E-03}, EIRFunT = {4.626807E-01,-2.305674E-02,1.169126E-03,3.431185E-02,-3.396938E-04,-7.381352E-05}, EIRFunPLR = {2.472427E-01,7.531481E-01,8.643617E-04}, etaMotor = 1.0) "ElectricEIRChiller York YK 2412kW/5.58COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_McQuay_PFH_2462kW_6_67COP_Vanes

ElectricEIRChiller McQuay PFH 2462kW/6.67COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller McQuay PFH 2462kW/6.67COP/Vanes,  !- Name
        2461600,                 !- Reference Capacity {W}
        6.67,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        22.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.07066,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.10157,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller McQuay PFH 2462kW/6.67COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller McQuay PFH 2462kW/6.67COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller McQuay PFH 2462kW/6.67COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 22.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -2461600 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.67 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.07066 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.10157 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {9.561527E-01,5.742999E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.462893E-01,2.854651E-02,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {9.222135E-02,5.830980E-01,3... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_McQuay_PFH_2462kW_6_67COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -2461600, COP_nominal = 6.67, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.07066, mCon_flow_nominal = 1000 * 0.10157, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 22.78, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {9.561527E-01,5.742999E-02,-4.868087E-03,1.799507E-02,-1.793848E-03,3.194186E-03}, EIRFunT = {5.462893E-01,2.854651E-02,-5.770782E-03,1.634571E-02,-2.645314E-04,2.138325E-03}, EIRFunPLR = {9.222135E-02,5.830980E-01,3.250019E-01}, etaMotor = 1.0) "ElectricEIRChiller McQuay PFH 2462kW/6.67COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_CVHF_2567kW_11_77COP_VSD

ElectricEIRChiller Trane CVHF 2567kW/11.77COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane CVHF 2567kW/11.77COP/VSD,  !- Name
        2567100,                 !- Reference Capacity {W}
        11.77,                   !- Reference COP {W/W}
        4.44,                    !- Reference Leaving Chilled Water Temperature {C}
        12.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.12113,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.15142,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane CVHF 2567kW/11.77COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHF 2567kW/11.77COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHF 2567kW/11.77COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.11,                    !- Minimum Part Load Ratio
        1.04,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.11,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.04 | Maximum part load ratio
Real | PLRMinUnl | 0.11 | Minimum part unload ratio
Real | PLRMin | 0.11 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 12.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -2567100 | Reference capacity (negative number) [W]
Real | COP_nominal | 11.77 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.12113 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.15142 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 4.44 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {4.549428E-01,2.748161E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {4.561990E-01,-3.333063E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.039419E-01,4.184975E-01,4... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_CVHF_2567kW_11_77COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -2567100, COP_nominal = 11.77, PLRMin = 0.11, PLRMinUnl = 0.11, PLRMax = 1.04, mEva_flow_nominal = 1000 * 0.12113, mCon_flow_nominal = 1000 * 0.15142, TEvaLvg_nominal = 273.15 + 4.44, TConEnt_nominal = 273.15 + 12.78, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {4.549428E-01,2.748161E-02,-4.298342E-03,4.363928E-02,-1.352509E-03,2.964225E-03}, EIRFunT = {4.561990E-01,-3.333063E-02,-1.763576E-03,5.624520E-02,-8.535085E-05,3.567604E-04}, EIRFunPLR = {1.039419E-01,4.184975E-01,4.774210E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane CVHF 2567kW/11.77COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YK_2771kW_6_84COP_VSD

ElectricEIRChiller York YK 2771kW/6.84COP/VSD

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YK 2771kW/6.84COP/VSD,  !- Name
        2771100,                 !- Reference Capacity {W}
        6.84,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.10094,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.15142,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YK 2771kW/6.84COP/VSD CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YK 2771kW/6.84COP/VSD EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YK 2771kW/6.84COP/VSD EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -2771100 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.84 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.10094 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.15142 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {7.734286E-01,4.848829E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {7.203736E-01,1.030460E-02,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {8.653354E-02,1.737382E-01,7... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YK_2771kW_6_84COP_VSD = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -2771100, COP_nominal = 6.84, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.10094, mCon_flow_nominal = 1000 * 0.15142, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {7.734286E-01,4.848829E-02,-1.859209E-03,2.611971E-02,-1.243562E-03,7.210181E-04}, EIRFunT = {7.203736E-01,1.030460E-02,-7.854237E-04,-1.206349E-03,8.210060E-04,-1.455414E-03}, EIRFunPLR = {8.653354E-02,1.737382E-01,7.403679E-01}, etaMotor = 1.0) "ElectricEIRChiller York YK 2771kW/6.84COP/VSD";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_CVHF_2799kW_6_40COP_Vanes

ElectricEIRChiller Trane CVHF 2799kW/6.40COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane CVHF 2799kW/6.40COP/Vanes,  !- Name
        2799200,                 !- Reference Capacity {W}
        6.40,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        26.11,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.09893,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.13761,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane CVHF 2799kW/6.40COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHF 2799kW/6.40COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHF 2799kW/6.40COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.04,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.04 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.11 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -2799200 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.40 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.09893 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.13761 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {2.210324E-01,-2.752320E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {2.267558E-01,-7.615857E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {3.023576E-01,-2.893592E-02,... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 15.56 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_CVHF_2799kW_6_40COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -2799200, COP_nominal = 6.40, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.04, mEva_flow_nominal = 1000 * 0.09893, mCon_flow_nominal = 1000 * 0.13761, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 26.11, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 15.56, TConEntMax = 273.15 + 29.44, capFunT = {2.210324E-01,-2.752320E-02,4.903763E-04,7.337449E-02,-1.919426E-03,1.935659E-03}, EIRFunT = {2.267558E-01,-7.615857E-02,2.140583E-03,7.088812E-02,-1.124968E-03,6.089843E-04}, EIRFunPLR = {3.023576E-01,-2.893592E-02,7.262269E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane CVHF 2799kW/6.40COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YT_3133kW_9_16COP_Vanes

ElectricEIRChiller York YT 3133kW/9.16COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YT 3133kW/9.16COP/Vanes,  !- Name
        3133300,                 !- Reference Capacity {W}
        9.16,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        12.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.08076,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.12618,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YT 3133kW/9.16COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YT 3133kW/9.16COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YT 3133kW/9.16COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.07,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.07,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.07 | Minimum part unload ratio
Real | PLRMin | 0.07 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 12.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -3133300 | Reference capacity (negative number) [W]
Real | COP_nominal | 9.16 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.08076 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.12618 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {7.607419E-01,1.323998E-02,6... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {9.150153E-01,-3.956395E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.387579E-01,6.435208E-01,2... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YT_3133kW_9_16COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -3133300, COP_nominal = 9.16, PLRMin = 0.07, PLRMinUnl = 0.07, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.08076, mCon_flow_nominal = 1000 * 0.12618, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 12.78, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {7.607419E-01,1.323998E-02,6.902287E-04,1.510969E-02,-9.443341E-04,1.484396E-03}, EIRFunT = {9.150153E-01,-3.956395E-02,1.865473E-03,1.810633E-02,2.900613E-04,-4.199110E-04}, EIRFunPLR = {1.387579E-01,6.435208E-01,2.155990E-01}, etaMotor = 1.0) "ElectricEIRChiller York YT 3133kW/9.16COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_McQuay_PFH_3165kW_6_48COP_Vanes

ElectricEIRChiller McQuay PFH 3165kW/6.48COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller McQuay PFH 3165kW/6.48COP/Vanes,  !- Name
        3165000,                 !- Reference Capacity {W}
        6.48,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        22.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.09085,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.13627,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller McQuay PFH 3165kW/6.48COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller McQuay PFH 3165kW/6.48COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller McQuay PFH 3165kW/6.48COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 22.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -3165000 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.48 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.09085 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.13627 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.342558E+00,7.520735E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {9.347904E-01,6.551597E-02,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.054110E-01,4.090646E-01,4... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_McQuay_PFH_3165kW_6_48COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -3165000, COP_nominal = 6.48, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.09085, mCon_flow_nominal = 1000 * 0.13627, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 22.78, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {1.342558E+00,7.520735E-02,-8.988936E-03,-3.340001E-02,-6.065934E-04,4.684791E-03}, EIRFunT = {9.347904E-01,6.551597E-02,-1.242676E-02,-2.799974E-02,3.323287E-04,4.803491E-03}, EIRFunPLR = {1.054110E-01,4.090646E-01,4.838839E-01}, etaMotor = 1.0) "ElectricEIRChiller McQuay PFH 3165kW/6.48COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_McQuay_PFH_4020kW_7_35COP_Vanes

ElectricEIRChiller McQuay PFH 4020kW/7.35COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller McQuay PFH 4020kW/7.35COP/Vanes,  !- Name
        4019500,                 !- Reference Capacity {W}
        7.35,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        12.78,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.07874,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.09842,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller McQuay PFH 4020kW/7.35COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller McQuay PFH 4020kW/7.35COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller McQuay PFH 4020kW/7.35COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.14,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.14,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.14 | Minimum part unload ratio
Real | PLRMin | 0.14 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 12.78 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -4019500 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.35 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.07874 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.09842 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {8.958422E-01,3.762768E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {9.322623E-01,-2.157964E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {5.763566E-02,5.964012E-01,3... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 6.67 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.22 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_McQuay_PFH_4020kW_7_35COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -4019500, COP_nominal = 7.35, PLRMin = 0.14, PLRMinUnl = 0.14, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.07874, mCon_flow_nominal = 1000 * 0.09842, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 12.78, TEvaLvgMin = 273.15 + 6.67, TEvaLvgMax = 273.15 + 12.22, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {8.958422E-01,3.762768E-02,-3.550080E-03,-4.322645E-03,-1.194933E-03,3.006034E-03}, EIRFunT = {9.322623E-01,-2.157964E-02,-1.435883E-03,1.379036E-02,-1.491048E-04,1.302075E-03}, EIRFunPLR = {5.763566E-02,5.964012E-01,3.473613E-01}, etaMotor = 1.0) "ElectricEIRChiller McQuay PFH 4020kW/7.35COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YK_4396kW_6_63COP_Vanes

ElectricEIRChiller York YK 4396kW/6.63COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YK 4396kW/6.63COP/Vanes,  !- Name
        4395800,                 !- Reference Capacity {W}
        6.63,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        26.67,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.19558,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.24605,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YK 4396kW/6.63COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YK 4396kW/6.63COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YK 4396kW/6.63COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.41,                    !- Minimum Part Load Ratio
        1.06,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.41,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.06 | Maximum part load ratio
Real | PLRMinUnl | 0.41 | Minimum part unload ratio
Real | PLRMin | 0.41 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.67 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -4395800 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.63 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.19558 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.24605 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {3.693621E-01,-7.284715E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.913358E-01,-5.974145E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {3.021070E-01,3.103971E-02,6... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 7.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 26.67 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YK_4396kW_6_63COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -4395800, COP_nominal = 6.63, PLRMin = 0.41, PLRMinUnl = 0.41, PLRMax = 1.06, mEva_flow_nominal = 1000 * 0.19558, mCon_flow_nominal = 1000 * 0.24605, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 26.67, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 7.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 26.67, capFunT = {3.693621E-01,-7.284715E-02,-4.871930E-03,1.223355E-01,-5.368259E-03,1.035036E-02}, EIRFunT = {5.913358E-01,-5.974145E-02,8.176561E-04,3.987353E-02,-8.176694E-04,1.457994E-03}, EIRFunPLR = {3.021070E-01,3.103971E-02,6.669726E-01}, etaMotor = 1.0) "ElectricEIRChiller York YK 4396kW/6.63COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YK_4477kW_6_64COP_Vanes

ElectricEIRChiller York YK 4477kW/6.64COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YK 4477kW/6.64COP/Vanes,  !- Name
        4476700,                 !- Reference Capacity {W}
        6.64,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        26.67,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.19558,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.24605,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YK 4477kW/6.64COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YK 4477kW/6.64COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YK 4477kW/6.64COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.41,                    !- Minimum Part Load Ratio
        1.06,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.41,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.06 | Maximum part load ratio
Real | PLRMinUnl | 0.41 | Minimum part unload ratio
Real | PLRMin | 0.41 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.67 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -4476700 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.64 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.19558 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.24605 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {4.844230E-01,-9.879643E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {4.264570E-01,-3.391606E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.767206E-01,1.074393E-01,6... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 7.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 26.67 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YK_4477kW_6_64COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -4476700, COP_nominal = 6.64, PLRMin = 0.41, PLRMinUnl = 0.41, PLRMax = 1.06, mEva_flow_nominal = 1000 * 0.19558, mCon_flow_nominal = 1000 * 0.24605, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 26.67, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 7.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 26.67, capFunT = {4.844230E-01,-9.879643E-02,-2.516527E-03,1.144722E-01,-5.101526E-03,1.022861E-02}, EIRFunT = {4.264570E-01,-3.391606E-02,-1.991396E-03,5.032090E-02,-1.140771E-03,1.814692E-03}, EIRFunPLR = {2.767206E-01,1.074393E-01,6.145706E-01}, etaMotor = 1.0) "ElectricEIRChiller York YK 4477kW/6.64COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YK_4515kW_6_22COP_Vanes

ElectricEIRChiller York YK 4515kW/6.22COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YK 4515kW/6.22COP/Vanes,  !- Name
        4515400,                 !- Reference Capacity {W}
        6.22,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        26.67,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.19558,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.24605,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YK 4515kW/6.22COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YK 4515kW/6.22COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YK 4515kW/6.22COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.40,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.40,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.40 | Minimum part unload ratio
Real | PLRMin | 0.40 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.67 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -4515400 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.22 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.19558 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.24605 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {3.732405E-01,-7.176618E-03,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.908290E-01,1.028668E-02,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.870815E-01,3.951784E-01,3... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 7.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 26.67 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YK_4515kW_6_22COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -4515400, COP_nominal = 6.22, PLRMin = 0.40, PLRMinUnl = 0.40, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.19558, mCon_flow_nominal = 1000 * 0.24605, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 26.67, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 7.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 26.67, capFunT = {3.732405E-01,-7.176618E-03,-2.588788E-03,5.381225E-02,-1.773937E-03,3.509721E-03}, EIRFunT = {5.908290E-01,1.028668E-02,-4.718838E-04,1.220347E-02,4.166971E-04,-1.484327E-03}, EIRFunPLR = {2.870815E-01,3.951784E-01,3.177735E-01}, etaMotor = 1.0) "ElectricEIRChiller York YK 4515kW/6.22COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YK_4537kW_6_28COP_Vanes

ElectricEIRChiller York YK 4537kW/6.28COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YK 4537kW/6.28COP/Vanes,  !- Name
        4536500,                 !- Reference Capacity {W}
        6.28,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        26.67,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.19558,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.24605,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YK 4537kW/6.28COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YK 4537kW/6.28COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YK 4537kW/6.28COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.40,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.40,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.40 | Minimum part unload ratio
Real | PLRMin | 0.40 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.67 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -4536500 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.28 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.19558 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.24605 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {9.418253E-01,8.142292E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {7.709829E-01,-2.257680E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.528426E-01,2.920280E-01,4... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 7.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 26.67 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YK_4537kW_6_28COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -4536500, COP_nominal = 6.28, PLRMin = 0.40, PLRMinUnl = 0.40, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.19558, mCon_flow_nominal = 1000 * 0.24605, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 26.67, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 7.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 26.67, capFunT = {9.418253E-01,8.142292E-02,-9.532713E-03,3.185018E-02,-2.583116E-03,5.294716E-03}, EIRFunT = {7.709829E-01,-2.257680E-02,2.492708E-04,7.635418E-03,3.376522E-04,-3.614203E-04}, EIRFunPLR = {2.528426E-01,2.920280E-01,4.533447E-01}, etaMotor = 1.0) "ElectricEIRChiller York YK 4537kW/6.28COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_CVHF_4610kW_6_34COP_Vanes

ElectricEIRChiller Trane CVHF 4610kW/6.34COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane CVHF 4610kW/6.34COP/Vanes,  !- Name
        4610300,                 !- Reference Capacity {W}
        6.34,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        26.11,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.19129,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.24757,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane CVHF 4610kW/6.34COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHF 4610kW/6.34COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHF 4610kW/6.34COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.11 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -4610300 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.34 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.19129 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.24757 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {8.614836E-01,-3.988130E-03,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {7.415078E-01,-4.779029E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.026691E-01,2.922585E-01,5... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 18.33 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_CVHF_4610kW_6_34COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -4610300, COP_nominal = 6.34, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.19129, mCon_flow_nominal = 1000 * 0.24757, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 26.11, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 18.33, TConEntMax = 273.15 + 29.44, capFunT = {8.614836E-01,-3.988130E-03,-1.643579E-03,8.882312E-03,-3.930474E-04,1.593969E-03}, EIRFunT = {7.415078E-01,-4.779029E-02,-1.028085E-03,1.423650E-02,1.304315E-04,9.170177E-04}, EIRFunPLR = {2.026691E-01,2.922585E-01,5.044422E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane CVHF 4610kW/6.34COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19EX_4667kW_6_16COP_Vanes

ElectricEIRChiller Carrier 19EX 4667kW/6.16COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19EX 4667kW/6.16COP/Vanes,  !- Name
        4666600,                 !- Reference Capacity {W}
        6.16,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        26.67,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.19558,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.24605,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19EX 4667kW/6.16COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19EX 4667kW/6.16COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19EX 4667kW/6.16COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.40,                    !- Minimum Part Load Ratio
        1.04,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.40,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.04 | Maximum part load ratio
Real | PLRMinUnl | 0.40 | Minimum part unload ratio
Real | PLRMin | 0.40 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.67 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -4666600 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.16 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.19558 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.24605 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {4.084496E-01,-4.396326E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.214788E-01,-8.218594E-03,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {3.771252E-01,2.854188E-02,5... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 7.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 26.67 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19EX_4667kW_6_16COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -4666600, COP_nominal = 6.16, PLRMin = 0.40, PLRMinUnl = 0.40, PLRMax = 1.04, mEva_flow_nominal = 1000 * 0.19558, mCon_flow_nominal = 1000 * 0.24605, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 26.67, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 7.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 26.67, capFunT = {4.084496E-01,-4.396326E-02,-2.112120E-03,8.225310E-02,-3.066058E-03,5.257550E-03}, EIRFunT = {5.214788E-01,-8.218594E-03,-3.068358E-05,2.152332E-02,1.203908E-04,-7.167755E-04}, EIRFunPLR = {3.771252E-01,2.854188E-02,5.928670E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19EX 4667kW/6.16COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_CVHF_4677kW_6_27COP_Vanes

ElectricEIRChiller Trane CVHF 4677kW/6.27COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane CVHF 4677kW/6.27COP/Vanes,  !- Name
        4677100,                 !- Reference Capacity {W}
        6.27,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        26.67,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.20138,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.24605,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane CVHF 4677kW/6.27COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHF 4677kW/6.27COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane CVHF 4677kW/6.27COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.41,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.41,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.41 | Minimum part unload ratio
Real | PLRMin | 0.41 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.67 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -4677100 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.27 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.20138 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.24605 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {8.449416E-01,-2.116553E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {8.283132E-01,-3.030491E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {3.531562E-01,-2.126229E-01,... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 7.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 26.67 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_CVHF_4677kW_6_27COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -4677100, COP_nominal = 6.27, PLRMin = 0.41, PLRMinUnl = 0.41, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.20138, mCon_flow_nominal = 1000 * 0.24605, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 26.67, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 7.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 26.67, capFunT = {8.449416E-01,-2.116553E-02,6.121458E-03,7.120879E-03,-1.798959E-04,-1.349219E-04}, EIRFunT = {8.283132E-01,-3.030491E-02,4.164965E-03,-3.278448E-03,6.762508E-04,-1.107762E-03}, EIRFunPLR = {3.531562E-01,-2.126229E-01,8.597400E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane CVHF 4677kW/6.27COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YK_4966kW_6_05COP_Vanes

ElectricEIRChiller York YK 4966kW/6.05COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YK 4966kW/6.05COP/Vanes,  !- Name
        4965500,                 !- Reference Capacity {W}
        6.05,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        26.11,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.21198,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.26498,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YK 4966kW/6.05COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YK 4966kW/6.05COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YK 4966kW/6.05COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.12,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.12,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.12 | Minimum part unload ratio
Real | PLRMin | 0.12 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.11 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -4965500 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.05 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.21198 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.26498 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {5.746486E-01,-3.051134E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {8.229769E-01,-8.128614E-03,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {3.416463E-01,1.947185E-01,4... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 15.56 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YK_4966kW_6_05COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -4965500, COP_nominal = 6.05, PLRMin = 0.12, PLRMinUnl = 0.12, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.21198, mCon_flow_nominal = 1000 * 0.26498, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 26.11, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 15.56, TConEntMax = 273.15 + 29.44, capFunT = {5.746486E-01,-3.051134E-02,-1.964984E-04,3.309783E-02,-9.174714E-04,2.287276E-03}, EIRFunT = {8.229769E-01,-8.128614E-03,1.110212E-03,-3.521351E-03,6.129803E-04,-9.170063E-04}, EIRFunPLR = {3.416463E-01,1.947185E-01,4.640804E-01}, etaMotor = 1.0) "ElectricEIRChiller York YK 4966kW/6.05COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YK_4969kW_7_14COP_Vanes

ElectricEIRChiller York YK 4969kW/7.14COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YK 4969kW/7.14COP/Vanes,  !- Name
        4969000,                 !- Reference Capacity {W}
        7.14,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        26.11,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.17665,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.26498,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YK 4969kW/7.14COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YK 4969kW/7.14COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YK 4969kW/7.14COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.16,                    !- Minimum Part Load Ratio
        1.07,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.16,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.07 | Maximum part load ratio
Real | PLRMinUnl | 0.16 | Minimum part unload ratio
Real | PLRMin | 0.16 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.11 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -4969000 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.14 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.17665 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.26498 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {7.817577E-01,-1.012013E-01,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {7.382162E-01,-5.847442E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.259512E-01,2.320151E-01,5... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YK_4969kW_7_14COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -4969000, COP_nominal = 7.14, PLRMin = 0.16, PLRMinUnl = 0.16, PLRMax = 1.07, mEva_flow_nominal = 1000 * 0.17665, mCon_flow_nominal = 1000 * 0.26498, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 26.11, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {7.817577E-01,-1.012013E-01,-1.584389E-03,7.928475E-02,-3.674093E-03,7.999392E-03}, EIRFunT = {7.382162E-01,-5.847442E-02,1.117191E-03,2.168089E-02,-2.189722E-04,1.036877E-03}, EIRFunPLR = {2.259512E-01,2.320151E-01,5.423771E-01}, etaMotor = 1.0) "ElectricEIRChiller York YK 4969kW/7.14COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YK_4969kW_7_07COP_Vanes

ElectricEIRChiller York YK 4969kW/7.07COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YK 4969kW/7.07COP/Vanes,  !- Name
        4969000,                 !- Reference Capacity {W}
        7.07,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        26.11,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.17665,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.26498,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YK 4969kW/7.07COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YK 4969kW/7.07COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YK 4969kW/7.07COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.16,                    !- Minimum Part Load Ratio
        1.06,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.16,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.06 | Maximum part load ratio
Real | PLRMinUnl | 0.16 | Minimum part unload ratio
Real | PLRMin | 0.16 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.11 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -4969000 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.07 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.17665 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.26498 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.803605E-01,-9.685535E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {7.220087E-01,-4.480691E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.308102E-01,1.802734E-01,5... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 15.56 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YK_4969kW_7_07COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -4969000, COP_nominal = 7.07, PLRMin = 0.16, PLRMinUnl = 0.16, PLRMax = 1.06, mEva_flow_nominal = 1000 * 0.17665, mCon_flow_nominal = 1000 * 0.26498, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 26.11, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 15.56, TConEntMax = 273.15 + 29.44, capFunT = {1.803605E-01,-9.685535E-02,-5.831135E-03,1.341596E-01,-5.279908E-03,1.045372E-02}, EIRFunT = {7.220087E-01,-4.480691E-02,9.621038E-06,2.084835E-02,-2.615973E-04,1.188407E-03}, EIRFunPLR = {2.308102E-01,1.802734E-01,5.894894E-01}, etaMotor = 1.0) "ElectricEIRChiller York YK 4969kW/7.07COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19EX_4997kW_6_40COP_Vanes

ElectricEIRChiller Carrier 19EX 4997kW/6.40COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19EX 4997kW/6.40COP/Vanes,  !- Name
        4997200,                 !- Reference Capacity {W}
        6.40,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        26.67,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.19558,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.24605,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19EX 4997kW/6.40COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19EX 4997kW/6.40COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19EX 4997kW/6.40COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.40,                    !- Minimum Part Load Ratio
        1.05,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.40,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.05 | Maximum part load ratio
Real | PLRMinUnl | 0.40 | Minimum part unload ratio
Real | PLRMin | 0.40 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.67 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -4997200 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.40 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.19558 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.24605 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {7.122762E-02,2.550937E-03,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {6.685097E-01,-2.541433E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {3.364887E-01,2.122607E-01,4... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 7.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 26.67 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19EX_4997kW_6_40COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -4997200, COP_nominal = 6.40, PLRMin = 0.40, PLRMinUnl = 0.40, PLRMax = 1.05, mEva_flow_nominal = 1000 * 0.19558, mCon_flow_nominal = 1000 * 0.24605, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 26.67, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 7.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 26.67, capFunT = {7.122762E-02,2.550937E-03,-9.679482E-03,9.391204E-02,-3.505261E-03,7.309943E-03}, EIRFunT = {6.685097E-01,-2.541433E-02,3.334144E-03,1.002578E-02,5.753780E-04,-1.801340E-03}, EIRFunPLR = {3.364887E-01,2.122607E-01,4.486522E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19EX 4997kW/6.40COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19EX_5148kW_6_34COP_Vanes

ElectricEIRChiller Carrier 19EX 5148kW/6.34COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19EX 5148kW/6.34COP/Vanes,  !- Name
        5148400,                 !- Reference Capacity {W}
        6.34,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        26.11,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.18283,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.25526,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19EX 5148kW/6.34COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19EX 5148kW/6.34COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19EX 5148kW/6.34COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.11 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -5148400 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.34 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.18283 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.25526 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {3.564454E-01,2.020689E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.426449E-01,3.961314E-03,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.883602E-01,5.018646E-01,3... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 15.56 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19EX_5148kW_6_34COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -5148400, COP_nominal = 6.34, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.18283, mCon_flow_nominal = 1000 * 0.25526, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 26.11, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 15.56, TConEntMax = 273.15 + 29.44, capFunT = {3.564454E-01,2.020689E-02,-6.286899E-03,5.760425E-02,-2.102376E-03,4.126650E-03}, EIRFunT = {5.426449E-01,3.961314E-03,-1.195821E-04,1.609421E-02,3.089258E-04,-1.129525E-03}, EIRFunPLR = {1.883602E-01,5.018646E-01,3.089569E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19EX 5148kW/6.34COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YK_5170kW_7_15COP_Vanes

ElectricEIRChiller York YK 5170kW/7.15COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YK 5170kW/7.15COP/Vanes,  !- Name
        5169500,                 !- Reference Capacity {W}
        7.15,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        26.11,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.17665,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.26498,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YK 5170kW/7.15COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YK 5170kW/7.15COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YK 5170kW/7.15COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.15,                    !- Minimum Part Load Ratio
        1.08,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.15,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.08 | Maximum part load ratio
Real | PLRMinUnl | 0.15 | Minimum part unload ratio
Real | PLRMin | 0.15 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.11 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -5169500 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.15 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.17665 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.26498 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.675697E-01,-1.191228E-01,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.894383E-01,-2.926530E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.497273E-01,1.011288E-01,6... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 15.56 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YK_5170kW_7_15COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -5169500, COP_nominal = 7.15, PLRMin = 0.15, PLRMinUnl = 0.15, PLRMax = 1.08, mEva_flow_nominal = 1000 * 0.17665, mCon_flow_nominal = 1000 * 0.26498, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 26.11, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 15.56, TConEntMax = 273.15 + 29.44, capFunT = {1.675697E-01,-1.191228E-01,-4.328384E-03,1.355905E-01,-5.171251E-03,1.039840E-02}, EIRFunT = {5.894383E-01,-2.926530E-02,-1.900238E-03,2.849479E-02,-5.105015E-04,1.702334E-03}, EIRFunPLR = {2.497273E-01,1.011288E-01,6.499847E-01}, etaMotor = 1.0) "ElectricEIRChiller York YK 5170kW/7.15COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19EX_5208kW_6_88COP_Vanes

ElectricEIRChiller Carrier 19EX 5208kW/6.88COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19EX 5208kW/6.88COP/Vanes,  !- Name
        5208200,                 !- Reference Capacity {W}
        6.88,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        26.11,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.18283,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.25293,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19EX 5208kW/6.88COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19EX 5208kW/6.88COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19EX 5208kW/6.88COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.11 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -5208200 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.88 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.18283 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.25293 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {5.563516E-01,-4.106264E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.198204E-01,-1.523340E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.334262E-01,3.926783E-01,3... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 15.56 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19EX_5208kW_6_88COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -5208200, COP_nominal = 6.88, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.18283, mCon_flow_nominal = 1000 * 0.25293, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 26.11, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 15.56, TConEntMax = 273.15 + 29.44, capFunT = {5.563516E-01,-4.106264E-02,-3.164992E-03,5.722234E-02,-2.313857E-03,5.377616E-03}, EIRFunT = {5.198204E-01,-1.523340E-02,-6.391523E-04,2.170049E-02,2.423693E-05,1.432604E-04}, EIRFunPLR = {2.334262E-01,3.926783E-01,3.731320E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19EX 5208kW/6.88COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YK_5465kW_6_94COP_Vanes

ElectricEIRChiller York YK 5465kW/6.94COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YK 5465kW/6.94COP/Vanes,  !- Name
        5464900,                 !- Reference Capacity {W}
        6.94,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        26.11,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.18296,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.27444,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YK 5465kW/6.94COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YK 5465kW/6.94COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YK 5465kW/6.94COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.14,                    !- Minimum Part Load Ratio
        1.07,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.14,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.07 | Maximum part load ratio
Real | PLRMinUnl | 0.14 | Minimum part unload ratio
Real | PLRMin | 0.14 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.11 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -5464900 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.94 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.18296 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.27444 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.092441E-01,-1.225892E-01,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {6.396022E-01,-5.954060E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.795792E-01,7.872758E-02,6... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 15.56 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YK_5465kW_6_94COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -5464900, COP_nominal = 6.94, PLRMin = 0.14, PLRMinUnl = 0.14, PLRMax = 1.07, mEva_flow_nominal = 1000 * 0.18296, mCon_flow_nominal = 1000 * 0.27444, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 26.11, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 15.56, TConEntMax = 273.15 + 29.44, capFunT = {1.092441E-01,-1.225892E-01,-2.802873E-03,1.324138E-01,-4.714937E-03,9.205744E-03}, EIRFunT = {6.396022E-01,-5.954060E-02,5.884523E-04,3.170651E-02,-5.088216E-04,1.460759E-03}, EIRFunPLR = {2.795792E-01,7.872758E-02,6.424321E-01}, etaMotor = 1.0) "ElectricEIRChiller York YK 5465kW/6.94COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YK_5549kW_6_50COP_Vanes

ElectricEIRChiller York YK 5549kW/6.50COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YK 5549kW/6.50COP/Vanes,  !- Name
        5549300,                 !- Reference Capacity {W}
        6.50,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        26.11,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.18296,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.27444,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YK 5549kW/6.50COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YK 5549kW/6.50COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YK 5549kW/6.50COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.14,                    !- Minimum Part Load Ratio
        1.05,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.14,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.05 | Maximum part load ratio
Real | PLRMinUnl | 0.14 | Minimum part unload ratio
Real | PLRMin | 0.14 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.11 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -5549300 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.50 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.18296 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.27444 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {-1.402079E-01,1.836029E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {4.989980E-01,-8.246157E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.336623E-01,1.901320E-01,5... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 26.11 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YK_5549kW_6_50COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -5549300, COP_nominal = 6.50, PLRMin = 0.14, PLRMinUnl = 0.14, PLRMax = 1.05, mEva_flow_nominal = 1000 * 0.18296, mCon_flow_nominal = 1000 * 0.27444, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 26.11, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 26.11, capFunT = {-1.402079E-01,1.836029E-02,-2.390588E-03,1.207956E-01,-3.563147E-03,2.024532E-03}, EIRFunT = {4.989980E-01,-8.246157E-02,6.047523E-03,5.168793E-02,-8.552445E-04,6.275326E-05}, EIRFunPLR = {2.336623E-01,1.901320E-01,5.749473E-01}, etaMotor = 1.0) "ElectricEIRChiller York YK 5549kW/6.50COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_19FA_5651kW_5_50COP_Vanes

ElectricEIRChiller Carrier 19FA 5651kW/5.50COP/Vanes

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 19FA 5651kW/5.50COP/Vanes,  !- Name
        5651300,                 !- Reference Capacity {W}
        5.50,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        29.44,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.18927,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.18927,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 19FA 5651kW/5.50COP/Vanes CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19FA 5651kW/5.50COP/Vanes EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 19FA 5651kW/5.50COP/Vanes EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.19,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.19,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.19 | Minimum part unload ratio
Real | PLRMin | 0.19 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 29.44 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -5651300 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.50 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.18927 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.18927 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.299676E+00,1.790645E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {7.853207E-01,-1.652255E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.629327E-01,5.709336E-01,2... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 15.56 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_19FA_5651kW_5_50COP_Vanes = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -5651300, COP_nominal = 5.50, PLRMin = 0.19, PLRMinUnl = 0.19, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.18927, mCon_flow_nominal = 1000 * 0.18927, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 29.44, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 15.56, TConEntMax = 273.15 + 29.44, capFunT = {1.299676E+00,1.790645E-02,-2.522300E-03,2.536423E-03,-1.128041E-03,3.003265E-03}, EIRFunT = {7.853207E-01,-1.652255E-02,-3.294526E-04,4.569179E-03,1.964013E-04,1.761497E-04}, EIRFunPLR = {1.629327E-01,5.709336E-01,2.659304E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 19FA 5651kW/5.50COP/Vanes";

## Buildings.Fluid.Chillers.Data.ElectricEIR.DOE_2_Centrifugal_5_50COP

DOE-2 Centrifugal/5.50COP

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        DOE-2 Centrifugal/5.50COP,  !- Name
        Autosize,                !- Reference Capacity {W}
        5.5,                     !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        29.4,                    !- Reference Entering Condenser Fluid Temperature {C}
        Autosize,                !- Reference Chilled Water Flow Rate {m3/s}
        Autosize,                !- Reference Condenser Water Flow Rate {m3/s}
        DOE-2 Centrifugal/5.50COP CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        DOE-2 Centrifugal/5.50COP EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        DOE-2 Centrifugal/5.50COP EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.1,                     !- Minimum Part Load Ratio
        1.0,                     !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.2,                     !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow;            !- Chiller Flow Mode

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.0 | Maximum part load ratio
Real | PLRMinUnl | 0.2 | Minimum part unload ratio
Real | PLRMin | 0.1 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 29.4 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -100000.0 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.5 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.0022 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.0041 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {0.257896E+00,0.389016E-01,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {0.933884E+00,-0.582120E-01,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {0.222903,0.313387,0.463710} | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.0 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.0 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 24.0 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 35.0 | Maximum value for entering condenser temperature [K]

### Modelica definition

record DOE_2_Centrifugal_5_50COP = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -100000.0, COP_nominal = 5.5, PLRMin = 0.1, PLRMinUnl = 0.2, PLRMax = 1.0, mEva_flow_nominal = 1000 * 0.0022, mCon_flow_nominal = 1000 * 0.0041, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 29.4, TEvaLvgMin = 273.15 + 5.0, TEvaLvgMax = 273.15 + 10.0, TConEntMin = 273.15 + 24.0, TConEntMax = 273.15 + 35.0, capFunT = {0.257896E+00,0.389016E-01,-0.217080E-03,0.468684E-01,-0.942840E-03,-0.343440E-03}, EIRFunT = {0.933884E+00,-0.582120E-01,0.450036E-02,0.243000E-02,0.486000E-03,-0.121500E-02}, EIRFunPLR = {0.222903,0.313387,0.463710}, etaMotor = 1.0) "DOE-2 Centrifugal/5.50COP";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Multistack_MS_172kW_3_67COP_None

ElectricEIRChiller Multistack MS 172kW/3.67COP/None

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Multistack MS 172kW/3.67COP/None,  !- Name
        172300,                  !- Reference Capacity {W}
        3.67,                    !- Reference COP {W/W}
        4.44,                    !- Reference Leaving Chilled Water Temperature {C}
        18.33,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.00738,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.00959,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Multistack MS 172kW/3.67COP/None CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Multistack MS 172kW/3.67COP/None EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Multistack MS 172kW/3.67COP/None EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.40,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.40,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.40 | Minimum part unload ratio
Real | PLRMin | 0.40 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 18.33 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -172300 | Reference capacity (negative number) [W]
Real | COP_nominal | 3.67 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.00738 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.00959 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 4.44 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {9.839419E-01,1.094957E-01,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {9.396181E-01,-5.754225E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {4.747786E-03,1.072374E+00,-... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 18.33 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 35.00 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Multistack_MS_172kW_3_67COP_None = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -172300, COP_nominal = 3.67, PLRMin = 0.40, PLRMinUnl = 0.40, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.00738, mCon_flow_nominal = 1000 * 0.00959, TEvaLvg_nominal = 273.15 + 4.44, TConEnt_nominal = 273.15 + 18.33, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 18.33, TConEntMax = 273.15 + 35.00, capFunT = {9.839419E-01,1.094957E-01,-4.547595E-03,-2.311886E-02,2.595943E-04,-5.093307E-04}, EIRFunT = {9.396181E-01,-5.754225E-02,2.561677E-03,1.081450E-02,1.839935E-04,5.269319E-05}, EIRFunPLR = {4.747786E-03,1.072374E+00,-7.758317E-02}, etaMotor = 1.0) "ElectricEIRChiller Multistack MS 172kW/3.67COP/None";

## Buildings.Fluid.Chillers.Data.ElectricEIR.DOE_2_Reciprocating_3_67COP

DOE-2 Reciprocating/3.67COP

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        DOE-2 Reciprocating/3.67COP,  !- Name
        Autosize,                !- Reference Capacity {W}
        3.67,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        29.4,                    !- Reference Entering Condenser Fluid Temperature {C}
        Autosize,                !- Reference Chilled Water Flow Rate {m3/s}
        Autosize,                !- Reference Condenser Water Flow Rate {m3/s}
        DOE-2 Reciprocating/3.67COP CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        DOE-2 Reciprocating/3.67COP EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        DOE-2 Reciprocating/3.67COP EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.1,                     !- Minimum Part Load Ratio
        1.0,                     !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.2,                     !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow;            !- Chiller Flow Mode

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.0 | Maximum part load ratio
Real | PLRMinUnl | 0.2 | Minimum part unload ratio
Real | PLRMin | 0.1 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 29.4 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -100000.0 | Reference capacity (negative number) [W]
Real | COP_nominal | 3.67 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.0022 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.0044 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {0.507883E+00,0.145228E+00,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {0.103076E+01,-0.103536E+00,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {0.088065,1.137742,-0.225806} | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.0 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.0 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 24.0 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 35.0 | Maximum value for entering condenser temperature [K]

### Modelica definition

record DOE_2_Reciprocating_3_67COP = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -100000.0, COP_nominal = 3.67, PLRMin = 0.1, PLRMinUnl = 0.2, PLRMax = 1.0, mEva_flow_nominal = 1000 * 0.0022, mCon_flow_nominal = 1000 * 0.0044, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 29.4, TEvaLvgMin = 273.15 + 5.0, TEvaLvgMax = 273.15 + 10.0, TConEntMin = 273.15 + 24.0, TConEntMax = 273.15 + 35.0, capFunT = {0.507883E+00,0.145228E+00,-0.625644E-02,-0.111780E-02,-0.129600E-03,-0.281880E-03}, EIRFunT = {0.103076E+01,-0.103536E+00,0.710208E-02,0.931860E-02,0.317520E-03,-0.104328E-02}, EIRFunPLR = {0.088065,1.137742,-0.225806}, etaMotor = 1.0) "DOE-2 Reciprocating/3.67COP";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_RTWA_383kW_4_17COP_Valve

ElectricEIRChiller Trane RTWA 383kW/4.17COP/Valve

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane RTWA 383kW/4.17COP/Valve,  !- Name
        383300,                  !- Reference Capacity {W}
        4.17,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        29.44,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.0165,                  !- Reference Chilled Water Flow Rate {m3/s}
        0.02063,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane RTWA 383kW/4.17COP/Valve CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane RTWA 383kW/4.17COP/Valve EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane RTWA 383kW/4.17COP/Valve EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.25,                    !- Minimum Part Load Ratio
        1.01,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.25,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.01 | Maximum part load ratio
Real | PLRMinUnl | 0.25 | Minimum part unload ratio
Real | PLRMin | 0.25 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 29.44 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -383300 | Reference capacity (negative number) [W]
Real | COP_nominal | 4.17 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.0165 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.02063 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {9.830684E-01,3.676199E-02,5... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {6.228513E-01,-8.700783E-03,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {3.295553E-02,9.114398E-01,5... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 23.89 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 35.00 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_RTWA_383kW_4_17COP_Valve = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -383300, COP_nominal = 4.17, PLRMin = 0.25, PLRMinUnl = 0.25, PLRMax = 1.01, mEva_flow_nominal = 1000 * 0.0165, mCon_flow_nominal = 1000 * 0.02063, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 29.44, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 23.89, TConEntMax = 273.15 + 35.00, capFunT = {9.830684E-01,3.676199E-02,5.307995E-05,-4.828624E-03,-4.755963E-05,-2.377982E-04}, EIRFunT = {6.228513E-01,-8.700783E-03,9.719796E-04,5.184584E-03,4.951699E-04,-9.632370E-04}, EIRFunPLR = {3.295553E-02,9.114398E-01,5.565265E-02}, etaMotor = 1.0) "ElectricEIRChiller Trane RTWA 383kW/4.17COP/Valve";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_RTHB_531kW_4_83COP_Valve

ElectricEIRChiller Trane RTHB 531kW/4.83COP/Valve

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane RTHB 531kW/4.83COP/Valve,  !- Name
        531000,                  !- Reference Capacity {W}
        4.83,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.0135,                  !- Reference Chilled Water Flow Rate {m3/s}
        0.01577,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane RTHB 531kW/4.83COP/Valve CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane RTHB 531kW/4.83COP/Valve EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane RTHB 531kW/4.83COP/Valve EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.30,                    !- Minimum Part Load Ratio
        1.01,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.30,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.01 | Maximum part load ratio
Real | PLRMinUnl | 0.30 | Minimum part unload ratio
Real | PLRMin | 0.30 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -531000 | Reference capacity (negative number) [W]
Real | COP_nominal | 4.83 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.0135 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.01577 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {9.434012E-01,1.630729E-02,8... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {4.524778E-01,1.045156E-04,6... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.980020E-01,2.733157E-01,5... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 15.56 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_RTHB_531kW_4_83COP_Valve = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -531000, COP_nominal = 4.83, PLRMin = 0.30, PLRMinUnl = 0.30, PLRMax = 1.01, mEva_flow_nominal = 1000 * 0.0135, mCon_flow_nominal = 1000 * 0.01577, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 15.56, TConEntMax = 273.15 + 23.89, capFunT = {9.434012E-01,1.630729E-02,8.621098E-04,3.242384E-03,-3.003973E-04,1.931126E-04}, EIRFunT = {4.524778E-01,1.045156E-04,6.932509E-05,2.044980E-02,3.672953E-04,-1.099051E-03}, EIRFunPLR = {1.980020E-01,2.733157E-01,5.277318E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane RTHB 531kW/4.83COP/Valve";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_RTHB_538kW_5_12COP_Valve

ElectricEIRChiller Trane RTHB 538kW/5.12COP/Valve

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane RTHB 538kW/5.12COP/Valve,  !- Name
        538000,                  !- Reference Capacity {W}
        5.12,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.01375,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.01956,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane RTHB 538kW/5.12COP/Valve CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane RTHB 538kW/5.12COP/Valve EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane RTHB 538kW/5.12COP/Valve EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.30,                    !- Minimum Part Load Ratio
        1.01,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.30,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.01 | Maximum part load ratio
Real | PLRMinUnl | 0.30 | Minimum part unload ratio
Real | PLRMin | 0.30 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -538000 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.12 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.01375 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.01956 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {9.344780E-01,2.760000E-02,3... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.455087E-01,-9.301201E-03,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.816950E-01,3.731838E-01,4... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 15.56 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_RTHB_538kW_5_12COP_Valve = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -538000, COP_nominal = 5.12, PLRMin = 0.30, PLRMinUnl = 0.30, PLRMax = 1.01, mEva_flow_nominal = 1000 * 0.01375, mCon_flow_nominal = 1000 * 0.01956, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 15.56, TConEntMax = 273.15 + 23.89, capFunT = {9.344780E-01,2.760000E-02,3.781512E-04,-9.176470E-04,-1.270588E-04,-4.235294E-05}, EIRFunT = {5.455087E-01,-9.301201E-03,5.012361E-04,1.432870E-02,4.719381E-04,-8.937669E-04}, EIRFunPLR = {1.816950E-01,3.731838E-01,4.448009E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane RTHB 538kW/5.12COP/Valve";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_RTHB_542kW_5_26COP_Valve

ElectricEIRChiller Trane RTHB 542kW/5.26COP/Valve

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane RTHB 542kW/5.26COP/Valve,  !- Name
        541500,                  !- Reference Capacity {W}
        5.26,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        21.11,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.01363,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.01577,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane RTHB 542kW/5.26COP/Valve CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane RTHB 542kW/5.26COP/Valve EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane RTHB 542kW/5.26COP/Valve EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.30,                    !- Minimum Part Load Ratio
        1.01,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.30,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.01 | Maximum part load ratio
Real | PLRMinUnl | 0.30 | Minimum part unload ratio
Real | PLRMin | 0.30 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 21.11 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -541500 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.26 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.01363 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.01577 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {9.226438E-01,2.878831E-02,3... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {4.953775E-01,-1.359340E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {3.057645E-01,-1.548084E-01,... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 15.56 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_RTHB_542kW_5_26COP_Valve = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -541500, COP_nominal = 5.26, PLRMin = 0.30, PLRMinUnl = 0.30, PLRMax = 1.01, mEva_flow_nominal = 1000 * 0.01363, mCon_flow_nominal = 1000 * 0.01577, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 21.11, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 15.56, TConEntMax = 273.15 + 23.89, capFunT = {9.226438E-01,2.878831E-02,3.756957E-04,-1.963636E-03,-8.415584E-05,-1.262338E-04}, EIRFunT = {4.953775E-01,-1.359340E-02,5.784637E-04,2.778142E-02,1.747259E-04,-8.590768E-04}, EIRFunPLR = {3.057645E-01,-1.548084E-01,8.484536E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane RTHB 542kW/5.26COP/Valve";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YS_672kW_7_90COP_Valve

ElectricEIRChiller York YS 672kW/7.90COP/Valve

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YS 672kW/7.90COP/Valve,  !- Name
        671600,                  !- Reference Capacity {W}
        7.90,                    !- Reference COP {W/W}
        6.11,                    !- Reference Leaving Chilled Water Temperature {C}
        15.56,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.01514,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.0241,                  !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YS 672kW/7.90COP/Valve CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YS 672kW/7.90COP/Valve EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YS 672kW/7.90COP/Valve EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.09,                    !- Minimum Part Load Ratio
        1.01,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.09,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.01 | Maximum part load ratio
Real | PLRMinUnl | 0.09 | Minimum part unload ratio
Real | PLRMin | 0.09 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 15.56 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -671600 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.90 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.01514 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.0241 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.11 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {9.274375E-01,2.846559E-02,4... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {4.069331E-01,-6.420922E-03,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.936152E-01,3.375574E-01,4... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 6.11 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 15.56 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YS_672kW_7_90COP_Valve = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -671600, COP_nominal = 7.90, PLRMin = 0.09, PLRMinUnl = 0.09, PLRMax = 1.01, mEva_flow_nominal = 1000 * 0.01514, mCon_flow_nominal = 1000 * 0.0241, TEvaLvg_nominal = 273.15 + 6.11, TConEnt_nominal = 273.15 + 15.56, TEvaLvgMin = 273.15 + 6.11, TEvaLvgMax = 273.15 + 12.78, TConEntMin = 273.15 + 15.56, TConEntMax = 273.15 + 23.89, capFunT = {9.274375E-01,2.846559E-02,4.024428E-04,-5.932730E-03,-1.067418E-05,-2.199015E-04}, EIRFunT = {4.069331E-01,-6.420922E-03,2.689257E-04,4.500373E-02,1.583981E-04,-1.284532E-03}, EIRFunPLR = {1.936152E-01,3.375574E-01,4.704892E-01}, etaMotor = 1.0) "ElectricEIRChiller York YS 672kW/7.90COP/Valve";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_23XL_686kW_5_91COP_Valve

ElectricEIRChiller Carrier 23XL 686kW/5.91COP/Valve

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 23XL 686kW/5.91COP/Valve,  !- Name
        685700,                  !- Reference Capacity {W}
        5.91,                    !- Reference COP {W/W}
        6.11,                    !- Reference Leaving Chilled Water Temperature {C}
        23.74,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.0571,                  !- Reference Chilled Water Flow Rate {m3/s}
        0.03255,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 23XL 686kW/5.91COP/Valve CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 23XL 686kW/5.91COP/Valve EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 23XL 686kW/5.91COP/Valve EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.04,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.04 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.74 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -685700 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.91 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.0571 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.03255 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.11 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {2.903523E-01,-2.676742E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.014060E-01,1.561000E-03,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.113934E-01,4.190226E-01,3... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_23XL_686kW_5_91COP_Valve = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -685700, COP_nominal = 5.91, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.04, mEva_flow_nominal = 1000 * 0.0571, mCon_flow_nominal = 1000 * 0.03255, TEvaLvg_nominal = 273.15 + 6.11, TConEnt_nominal = 273.15 + 23.74, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {2.903523E-01,-2.676742E-02,-4.771695E-03,8.162394E-02,-3.028217E-03,5.712524E-03}, EIRFunT = {5.014060E-01,1.561000E-03,-1.347980E-04,1.525028E-02,5.701374E-04,-1.221374E-03}, EIRFunPLR = {2.113934E-01,4.190226E-01,3.686143E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 23XL 686kW/5.91COP/Valve";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_RTHC_707kW_7_77COP_Valve

ElectricEIRChiller Trane RTHC 707kW/7.77COP/Valve

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane RTHC 707kW/7.77COP/Valve,  !- Name
        706800,                  !- Reference Capacity {W}
        7.77,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        15.56,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.04921,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.03268,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane RTHC 707kW/7.77COP/Valve CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane RTHC 707kW/7.77COP/Valve EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane RTHC 707kW/7.77COP/Valve EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.28,                    !- Minimum Part Load Ratio
        1.01,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.28,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.01 | Maximum part load ratio
Real | PLRMinUnl | 0.28 | Minimum part unload ratio
Real | PLRMin | 0.28 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 15.56 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -706800 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.77 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.04921 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.03268 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {9.362925E-01,2.940722E-02,5... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {6.497944E-01,6.883157E-03,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.997099E-01,6.754676E-01,1... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 11.11 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 15.56 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_RTHC_707kW_7_77COP_Valve = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -706800, COP_nominal = 7.77, PLRMin = 0.28, PLRMinUnl = 0.28, PLRMax = 1.01, mEva_flow_nominal = 1000 * 0.04921, mCon_flow_nominal = 1000 * 0.03268, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 15.56, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 11.11, TConEntMin = 273.15 + 15.56, TConEntMax = 273.15 + 23.89, capFunT = {9.362925E-01,2.940722E-02,5.726999E-04,-5.696483E-03,-5.569609E-05,-1.708132E-04}, EIRFunT = {6.497944E-01,6.883157E-03,-5.277681E-04,1.725788E-02,6.779317E-04,-1.244055E-03}, EIRFunPLR = {1.997099E-01,6.754676E-01,1.243767E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane RTHC 707kW/7.77COP/Valve";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YS_756kW_7_41COP_Valve

ElectricEIRChiller York YS 756kW/7.41COP/Valve

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YS 756kW/7.41COP/Valve,  !- Name
        756000,                  !- Reference Capacity {W}
        7.41,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        16.06,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.06782,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.05142,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YS 756kW/7.41COP/Valve CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YS 756kW/7.41COP/Valve EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YS 756kW/7.41COP/Valve EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.11,                    !- Minimum Part Load Ratio
        1.01,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.11,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.01 | Maximum part load ratio
Real | PLRMinUnl | 0.11 | Minimum part unload ratio
Real | PLRMin | 0.11 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 16.06 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -756000 | Reference capacity (negative number) [W]
Real | COP_nominal | 7.41 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.06782 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.05142 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {9.432455E-01,2.794778E-02,2... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {6.917947E-01,-1.929936E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.929778E-01,1.673799E-02,6... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 16.06 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YS_756kW_7_41COP_Valve = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -756000, COP_nominal = 7.41, PLRMin = 0.11, PLRMinUnl = 0.11, PLRMax = 1.01, mEva_flow_nominal = 1000 * 0.06782, mCon_flow_nominal = 1000 * 0.05142, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 16.06, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 16.06, TConEntMax = 273.15 + 23.89, capFunT = {9.432455E-01,2.794778E-02,2.937753E-04,-5.818549E-03,-3.764392E-05,-5.777607E-05}, EIRFunT = {6.917947E-01,-1.929936E-02,1.450011E-03,1.795987E-02,9.301685E-04,-1.755165E-03}, EIRFunPLR = {2.929778E-01,1.673799E-02,6.881229E-01}, etaMotor = 1.0) "ElectricEIRChiller York YS 756kW/7.41COP/Valve";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YS_781kW_5_42COP_Valve

ElectricEIRChiller York YS 781kW/5.42COP/Valve

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YS 781kW/5.42COP/Valve,  !- Name
        780700,                  !- Reference Capacity {W}
        5.42,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        29.44,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.01893,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.03785,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YS 781kW/5.42COP/Valve CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YS 781kW/5.42COP/Valve EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YS 781kW/5.42COP/Valve EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.09,                    !- Minimum Part Load Ratio
        1.01,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.09,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.01 | Maximum part load ratio
Real | PLRMinUnl | 0.09 | Minimum part unload ratio
Real | PLRMin | 0.09 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 29.44 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -780700 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.42 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.01893 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.03785 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.002148E+00,3.300191E-02,3... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {4.475957E-01,-1.054652E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.519108E-01,2.756914E-01,4... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 15.56 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 35.00 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YS_781kW_5_42COP_Valve = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -780700, COP_nominal = 5.42, PLRMin = 0.09, PLRMinUnl = 0.09, PLRMax = 1.01, mEva_flow_nominal = 1000 * 0.01893, mCon_flow_nominal = 1000 * 0.03785, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 29.44, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 15.56, TConEntMax = 273.15 + 35.00, capFunT = {1.002148E+00,3.300191E-02,3.741670E-04,-5.925358E-03,-2.599267E-05,-2.172126E-04}, EIRFunT = {4.475957E-01,-1.054652E-02,7.126870E-04,1.158632E-02,5.151510E-04,-9.831355E-04}, EIRFunPLR = {2.519108E-01,2.756914E-01,4.725826E-01}, etaMotor = 1.0) "ElectricEIRChiller York YS 781kW/5.42COP/Valve";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_23XL_830kW_6_97COP_Valve

ElectricEIRChiller Carrier 23XL 830kW/6.97COP/Valve

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 23XL 830kW/6.97COP/Valve,  !- Name
        829900,                  !- Reference Capacity {W}
        6.97,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.03186,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.04744,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 23XL 830kW/6.97COP/Valve CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 23XL 830kW/6.97COP/Valve EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 23XL 830kW/6.97COP/Valve EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.01,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.01 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -829900 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.97 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.03186 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.04744 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {8.198506E-01,4.299516E-03,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {4.610959E-01,-1.560459E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.307464E-01,7.784162E-01,-... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 14.17 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_23XL_830kW_6_97COP_Valve = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -829900, COP_nominal = 6.97, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.01, mEva_flow_nominal = 1000 * 0.03186, mCon_flow_nominal = 1000 * 0.04744, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 14.17, TConEntMax = 273.15 + 23.89, capFunT = {8.198506E-01,4.299516E-03,-2.451574E-04,1.431034E-02,-3.586302E-04,2.510412E-04}, EIRFunT = {4.610959E-01,-1.560459E-02,-2.737454E-04,2.650593E-02,-7.789498E-05,1.855843E-04}, EIRFunPLR = {2.307464E-01,7.784162E-01,-7.516503E-03}, etaMotor = 1.0) "ElectricEIRChiller Carrier 23XL 830kW/6.97COP/Valve";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_23XL_862kW_6_11COP_Valve

ElectricEIRChiller Carrier 23XL 862kW/6.11COP/Valve

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 23XL 862kW/6.11COP/Valve,  !- Name
        861500,                  !- Reference Capacity {W}
        6.11,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.06782,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.04296,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 23XL 862kW/6.11COP/Valve CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 23XL 862kW/6.11COP/Valve EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 23XL 862kW/6.11COP/Valve EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.04,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.04 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -861500 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.11 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.06782 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.04296 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {-3.646458E-02,-6.061334E-02... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.420642E-01,-2.110032E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.292819E-01,3.662723E-01,4... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_23XL_862kW_6_11COP_Valve = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -861500, COP_nominal = 6.11, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.04, mEva_flow_nominal = 1000 * 0.06782, mCon_flow_nominal = 1000 * 0.04296, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {-3.646458E-02,-6.061334E-02,-3.708583E-03,1.197997E-01,-3.723397E-03,5.368766E-03}, EIRFunT = {5.420642E-01,-2.110032E-02,1.513908E-03,2.067897E-02,5.287518E-04,-1.630330E-03}, EIRFunPLR = {2.292819E-01,3.662723E-01,4.032019E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 23XL 862kW/6.11COP/Valve";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_23XL_862kW_6_84COP_Valve

ElectricEIRChiller Carrier 23XL 862kW/6.84COP/Valve

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 23XL 862kW/6.84COP/Valve,  !- Name
        861500,                  !- Reference Capacity {W}
        6.84,                    !- Reference COP {W/W}
        9.69,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.06782,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.04296,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 23XL 862kW/6.84COP/Valve CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 23XL 862kW/6.84COP/Valve EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 23XL 862kW/6.84COP/Valve EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.30,                    !- Minimum Part Load Ratio
        1.04,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.30,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.04 | Maximum part load ratio
Real | PLRMinUnl | 0.30 | Minimum part unload ratio
Real | PLRMin | 0.30 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -861500 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.84 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.06782 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.04296 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 9.69 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {-4.535842E-02,-6.253871E-02... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.930611E-01,-2.082914E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.145826E-01,7.340475E-01,1... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_23XL_862kW_6_84COP_Valve = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -861500, COP_nominal = 6.84, PLRMin = 0.30, PLRMinUnl = 0.30, PLRMax = 1.04, mEva_flow_nominal = 1000 * 0.06782, mCon_flow_nominal = 1000 * 0.04296, TEvaLvg_nominal = 273.15 + 9.69, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {-4.535842E-02,-6.253871E-02,-3.623064E-03,1.218299E-01,-3.793440E-03,5.404739E-03}, EIRFunT = {5.930611E-01,-2.082914E-02,1.600282E-03,2.352564E-02,5.992247E-04,-1.907335E-03}, EIRFunPLR = {1.145826E-01,7.340475E-01,1.507744E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 23XL 862kW/6.84COP/Valve";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_23XL_865kW_6_05COP_Valve

ElectricEIRChiller Carrier 23XL 865kW/6.05COP/Valve

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 23XL 865kW/6.05COP/Valve,  !- Name
        865100,                  !- Reference Capacity {W}
        6.05,                    !- Reference COP {W/W}
        4.44,                    !- Reference Leaving Chilled Water Temperature {C}
        26.11,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.03716,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.04366,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 23XL 865kW/6.05COP/Valve CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 23XL 865kW/6.05COP/Valve EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 23XL 865kW/6.05COP/Valve EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.11 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -865100 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.05 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.03716 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.04366 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 4.44 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {5.079758E-01,-2.344768E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.437328E-01,7.625344E-03,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.545235E-01,3.104981E-01,4... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 3.33 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 7.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_23XL_865kW_6_05COP_Valve = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -865100, COP_nominal = 6.05, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.03716, mCon_flow_nominal = 1000 * 0.04366, TEvaLvg_nominal = 273.15 + 4.44, TConEnt_nominal = 273.15 + 26.11, TEvaLvgMin = 273.15 + 3.33, TEvaLvgMax = 273.15 + 7.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {5.079758E-01,-2.344768E-02,-3.296630E-03,3.508384E-02,-8.359630E-04,2.585294E-03}, EIRFunT = {5.437328E-01,7.625344E-03,-9.201579E-05,1.339616E-03,8.286757E-04,-1.543530E-03}, EIRFunPLR = {2.545235E-01,3.104981E-01,4.347781E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 23XL 865kW/6.05COP/Valve";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YS_879kW_5_82COP_Valve

ElectricEIRChiller York YS 879kW/5.82COP/Valve

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YS 879kW/5.82COP/Valve,  !- Name
        879100,                  !- Reference Capacity {W}
        5.82,                    !- Reference COP {W/W}
        4.44,                    !- Reference Leaving Chilled Water Temperature {C}
        26.11,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.03785,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.04732,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YS 879kW/5.82COP/Valve CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YS 879kW/5.82COP/Valve EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YS 879kW/5.82COP/Valve EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 26.11 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -879100 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.82 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.03785 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.04732 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 4.44 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.031429E+00,3.364723E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.595308E-01,-1.087985E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {3.029493E-01,3.223124E-01,3... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 3.33 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 7.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YS_879kW_5_82COP_Valve = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -879100, COP_nominal = 5.82, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.03785, mCon_flow_nominal = 1000 * 0.04732, TEvaLvg_nominal = 273.15 + 4.44, TConEnt_nominal = 273.15 + 26.11, TEvaLvgMin = 273.15 + 3.33, TEvaLvgMax = 273.15 + 7.78, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 29.44, capFunT = {1.031429E+00,3.364723E-02,-2.735093E-04,-3.789167E-03,-1.553912E-04,2.782117E-04}, EIRFunT = {5.595308E-01,-1.087985E-02,8.721022E-04,1.010347E-02,5.087454E-04,-1.211319E-03}, EIRFunPLR = {3.029493E-01,3.223124E-01,3.751948E-01}, etaMotor = 1.0) "ElectricEIRChiller York YS 879kW/5.82COP/Valve";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_RTHC_1009kW_5_37COP_Valve

ElectricEIRChiller Trane RTHC 1009kW/5.37COP/Valve

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane RTHC 1009kW/5.37COP/Valve,  !- Name
        1009200,                 !- Reference Capacity {W}
        5.37,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        24.86,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.03186,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.04618,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane RTHC 1009kW/5.37COP/Valve CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane RTHC 1009kW/5.37COP/Valve EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane RTHC 1009kW/5.37COP/Valve EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.30,                    !- Minimum Part Load Ratio
        1.01,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.30,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.01 | Maximum part load ratio
Real | PLRMinUnl | 0.30 | Minimum part unload ratio
Real | PLRMin | 0.30 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 24.86 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1009200 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.37 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.03186 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.04618 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.134633E+00,3.267210E-02,5... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {4.383883E-01,7.754235E-03,6... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.316727E-01,1.013111E+00,-... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 19.97 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 24.86 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_RTHC_1009kW_5_37COP_Valve = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1009200, COP_nominal = 5.37, PLRMin = 0.30, PLRMinUnl = 0.30, PLRMax = 1.01, mEva_flow_nominal = 1000 * 0.03186, mCon_flow_nominal = 1000 * 0.04618, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 24.86, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 19.97, TConEntMax = 273.15 + 24.86, capFunT = {1.134633E+00,3.267210E-02,5.266344E-04,-1.076173E-02,-4.853769E-05,-2.569325E-04}, EIRFunT = {4.383883E-01,7.754235E-03,6.353809E-04,-2.951880E-03,1.270756E-03,-1.541831E-03}, EIRFunPLR = {1.316727E-01,1.013111E+00,-1.413213E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane RTHC 1009kW/5.37COP/Valve";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_RTHB_1051kW_5_05COP_Valve

ElectricEIRChiller Trane RTHB 1051kW/5.05COP/Valve

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane RTHB 1051kW/5.05COP/Valve,  !- Name
        1051400,                 !- Reference Capacity {W}
        5.05,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        29.44,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.04527,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.05659,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane RTHB 1051kW/5.05COP/Valve CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane RTHB 1051kW/5.05COP/Valve EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane RTHB 1051kW/5.05COP/Valve EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.01,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.01 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 29.44 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1051400 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.05 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.04527 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.05659 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {9.482157E-01,3.306737E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {4.904181E-01,-5.530317E-03,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.590465E-01,2.148987E-01,5... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 23.89 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 35.00 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_RTHB_1051kW_5_05COP_Valve = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1051400, COP_nominal = 5.05, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.01, mEva_flow_nominal = 1000 * 0.04527, mCon_flow_nominal = 1000 * 0.05659, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 29.44, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 23.89, TConEntMax = 273.15 + 35.00, capFunT = {9.482157E-01,3.306737E-02,-6.450072E-05,-3.756522E-03,-6.501672E-05,2.517986E-15}, EIRFunT = {4.904181E-01,-5.530317E-03,1.209907E-03,9.122333E-03,5.923591E-04,-1.469958E-03}, EIRFunPLR = {2.590465E-01,2.148987E-01,5.265039E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane RTHB 1051kW/5.05COP/Valve";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_23XL_1062kW_5_50COP_Valve

ElectricEIRChiller Carrier 23XL 1062kW/5.50COP/Valve

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 23XL 1062kW/5.50COP/Valve,  !- Name
        1062000,                 !- Reference Capacity {W}
        5.50,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        29.44,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.04573,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.05716,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 23XL 1062kW/5.50COP/Valve CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 23XL 1062kW/5.50COP/Valve EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 23XL 1062kW/5.50COP/Valve EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.01,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.01 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 29.44 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1062000 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.50 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.04573 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.05716 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.025695E+00,2.327484E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {2.634070E-01,-7.025220E-03,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {2.576261E-01,3.416910E-01,4... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 6.67 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 21.11 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 29.44 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_23XL_1062kW_5_50COP_Valve = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1062000, COP_nominal = 5.50, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.01, mEva_flow_nominal = 1000 * 0.04573, mCon_flow_nominal = 1000 * 0.05716, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 29.44, TEvaLvgMin = 273.15 + 6.67, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 21.11, TConEntMax = 273.15 + 29.44, capFunT = {1.025695E+00,2.327484E-02,-4.693708E-03,-7.092715E-03,-3.754967E-04,2.843046E-03}, EIRFunT = {2.634070E-01,-7.025220E-03,-4.942613E-04,2.516931E-02,1.712769E-04,-4.309735E-04}, EIRFunPLR = {2.576261E-01,3.416910E-01,4.007672E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 23XL 1062kW/5.50COP/Valve";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_RTHC_1066kW_5_73COP_Valve

ElectricEIRChiller Trane RTHC 1066kW/5.73COP/Valve

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane RTHC 1066kW/5.73COP/Valve,  !- Name
        1065500,                 !- Reference Capacity {W}
        5.73,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        25.28,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.05142,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.04416,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane RTHC 1066kW/5.73COP/Valve CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane RTHC 1066kW/5.73COP/Valve EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane RTHC 1066kW/5.73COP/Valve EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.30,                    !- Minimum Part Load Ratio
        1.01,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.30,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.01 | Maximum part load ratio
Real | PLRMinUnl | 0.30 | Minimum part unload ratio
Real | PLRMin | 0.30 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 25.28 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1065500 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.73 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.05142 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.04416 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.062396E+00,4.575299E-02,2... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {9.003080E-01,3.783201E-03,9... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.007344E-01,1.119205E+00,-... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 20.07 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 25.28 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_RTHC_1066kW_5_73COP_Valve = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1065500, COP_nominal = 5.73, PLRMin = 0.30, PLRMinUnl = 0.30, PLRMax = 1.01, mEva_flow_nominal = 1000 * 0.05142, mCon_flow_nominal = 1000 * 0.04416, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 25.28, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 20.07, TConEntMax = 273.15 + 25.28, capFunT = {1.062396E+00,4.575299E-02,2.802795E-04,-8.802343E-03,-3.127891E-05,-5.937227E-04}, EIRFunT = {9.003080E-01,3.783201E-03,9.815780E-04,-4.051727E-02,2.037095E-03,-1.619326E-03}, EIRFunPLR = {1.007344E-01,1.119205E+00,-2.173230E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane RTHC 1066kW/5.73COP/Valve";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_RTHC_1094kW_6_55COP_Valve

ElectricEIRChiller Trane RTHC 1094kW/6.55COP/Valve

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane RTHC 1094kW/6.55COP/Valve,  !- Name
        1093600,                 !- Reference Capacity {W}
        6.55,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        23.33,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.04921,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.04524,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane RTHC 1094kW/6.55COP/Valve CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane RTHC 1094kW/6.55COP/Valve EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane RTHC 1094kW/6.55COP/Valve EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.25,                    !- Minimum Part Load Ratio
        1.01,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.25,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.01 | Maximum part load ratio
Real | PLRMinUnl | 0.25 | Minimum part unload ratio
Real | PLRMin | 0.25 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.33 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1093600 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.55 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.04921 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.04524 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {9.643756E-01,3.820069E-02,4... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {6.579136E-01,-1.133448E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.626466E-01,7.903550E-01,4... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 15.56 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_RTHC_1094kW_6_55COP_Valve = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1093600, COP_nominal = 6.55, PLRMin = 0.25, PLRMinUnl = 0.25, PLRMax = 1.01, mEva_flow_nominal = 1000 * 0.04921, mCon_flow_nominal = 1000 * 0.04524, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 23.33, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 15.56, TConEntMax = 273.15 + 23.89, capFunT = {9.643756E-01,3.820069E-02,4.611891E-04,-5.174840E-03,-5.784404E-05,-2.944185E-04}, EIRFunT = {6.579136E-01,-1.133448E-02,6.497057E-04,7.318160E-03,6.167738E-04,-9.553369E-04}, EIRFunPLR = {1.626466E-01,7.903550E-01,4.770888E-02}, etaMotor = 1.0) "ElectricEIRChiller Trane RTHC 1094kW/6.55COP/Valve";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_23XL_1108kW_6_92COP_Valve

ElectricEIRChiller Carrier 23XL 1108kW/6.92COP/Valve

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 23XL 1108kW/6.92COP/Valve,  !- Name
        1107700,                 !- Reference Capacity {W}
        6.92,                    !- Reference COP {W/W}
        8.97,                    !- Reference Leaving Chilled Water Temperature {C}
        23.74,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.0571,                  !- Reference Chilled Water Flow Rate {m3/s}
        0.05142,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 23XL 1108kW/6.92COP/Valve CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 23XL 1108kW/6.92COP/Valve EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 23XL 1108kW/6.92COP/Valve EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.74 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1107700 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.92 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.0571 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.05142 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 8.97 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {6.631328E-01,-1.027433E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.668296E-01,-2.800906E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.370745E-01,8.374817E-01,2... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_23XL_1108kW_6_92COP_Valve = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1107700, COP_nominal = 6.92, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.0571, mCon_flow_nominal = 1000 * 0.05142, TEvaLvg_nominal = 273.15 + 8.97, TConEnt_nominal = 273.15 + 23.74, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {6.631328E-01,-1.027433E-02,-5.388040E-04,3.320295E-02,-1.304714E-03,2.169498E-03}, EIRFunT = {5.668296E-01,-2.800906E-02,9.362408E-04,2.210818E-02,4.660373E-04,-7.989601E-04}, EIRFunPLR = {1.370745E-01,8.374817E-01,2.534280E-02}, etaMotor = 1.0) "ElectricEIRChiller Carrier 23XL 1108kW/6.92COP/Valve";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YS_1171kW_9_15COP_Valve

ElectricEIRChiller York YS 1171kW/9.15COP/Valve

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YS 1171kW/9.15COP/Valve,  !- Name
        1171000,                 !- Reference Capacity {W}
        9.15,                    !- Reference COP {W/W}
        6.11,                    !- Reference Leaving Chilled Water Temperature {C}
        15.56,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.03249,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.05173,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YS 1171kW/9.15COP/Valve CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YS 1171kW/9.15COP/Valve EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YS 1171kW/9.15COP/Valve EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.09,                    !- Minimum Part Load Ratio
        1.01,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.09,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.01 | Maximum part load ratio
Real | PLRMinUnl | 0.09 | Minimum part unload ratio
Real | PLRMin | 0.09 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 15.56 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1171000 | Reference capacity (negative number) [W]
Real | COP_nominal | 9.15 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.03249 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.05173 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.11 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {9.299045E-01,2.350383E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.325834E-01,-2.611733E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.889392E-01,4.684305E-01,3... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 6.11 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.78 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 15.56 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YS_1171kW_9_15COP_Valve = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1171000, COP_nominal = 9.15, PLRMin = 0.09, PLRMinUnl = 0.09, PLRMax = 1.01, mEva_flow_nominal = 1000 * 0.03249, mCon_flow_nominal = 1000 * 0.05173, TEvaLvg_nominal = 273.15 + 6.11, TConEnt_nominal = 273.15 + 15.56, TEvaLvgMin = 273.15 + 6.11, TEvaLvgMax = 273.15 + 12.78, TConEntMin = 273.15 + 15.56, TConEntMax = 273.15 + 23.89, capFunT = {9.299045E-01,2.350383E-02,-4.649409E-04,-4.367237E-03,-2.040112E-04,6.430038E-04}, EIRFunT = {5.325834E-01,-2.611733E-02,1.365012E-03,4.099324E-02,3.401995E-04,-1.514251E-03}, EIRFunPLR = {1.889392E-01,4.684305E-01,3.451545E-01}, etaMotor = 1.0) "ElectricEIRChiller York YS 1171kW/9.15COP/Valve";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Carrier_23XL_1196kW_6_39COP_Valve

ElectricEIRChiller Carrier 23XL 1196kW/6.39COP/Valve

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Carrier 23XL 1196kW/6.39COP/Valve,  !- Name
        1195600,                 !- Reference Capacity {W}
        6.39,                    !- Reference COP {W/W}
        7.22,                    !- Reference Leaving Chilled Water Temperature {C}
        23.89,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.03653,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.04271,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Carrier 23XL 1196kW/6.39COP/Valve CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Carrier 23XL 1196kW/6.39COP/Valve EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Carrier 23XL 1196kW/6.39COP/Valve EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.03,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.03 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 23.89 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1195600 | Reference capacity (negative number) [W]
Real | COP_nominal | 6.39 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.03653 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.04271 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 7.22 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {5.775948E-01,2.206074E-02,-... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.077824E-01,-1.608447E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.061065E-01,7.305514E-01,1... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 6.67 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 12.22 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 23.89 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Carrier_23XL_1196kW_6_39COP_Valve = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1195600, COP_nominal = 6.39, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.03, mEva_flow_nominal = 1000 * 0.03653, mCon_flow_nominal = 1000 * 0.04271, TEvaLvg_nominal = 273.15 + 7.22, TConEnt_nominal = 273.15 + 23.89, TEvaLvgMin = 273.15 + 6.67, TEvaLvgMax = 273.15 + 12.22, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 23.89, capFunT = {5.775948E-01,2.206074E-02,-3.342365E-03,3.970188E-02,-1.669877E-03,2.762827E-03}, EIRFunT = {5.077824E-01,-1.608447E-02,1.742121E-04,2.093857E-02,4.160938E-04,-7.169668E-04}, EIRFunPLR = {1.061065E-01,7.305514E-01,1.632883E-01}, etaMotor = 1.0) "ElectricEIRChiller Carrier 23XL 1196kW/6.39COP/Valve";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YS_1554kW_9_31COP_Valve

ElectricEIRChiller York YS 1554kW/9.31COP/Valve

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YS 1554kW/9.31COP/Valve,  !- Name
        1554300,                 !- Reference Capacity {W}
        9.31,                    !- Reference COP {W/W}
        5.56,                    !- Reference Leaving Chilled Water Temperature {C}
        15.56,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.0424,                  !- Reference Chilled Water Flow Rate {m3/s}
        0.07949,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YS 1554kW/9.31COP/Valve CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YS 1554kW/9.31COP/Valve EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YS 1554kW/9.31COP/Valve EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.10,                    !- Minimum Part Load Ratio
        1.02,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.10,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.02 | Maximum part load ratio
Real | PLRMinUnl | 0.10 | Minimum part unload ratio
Real | PLRMin | 0.10 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 15.56 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1554300 | Reference capacity (negative number) [W]
Real | COP_nominal | 9.31 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.0424 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.07949 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 5.56 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {1.083027E+00,9.278069E-03,1... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {5.099117E-01,1.379553E-02,-... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {1.720219E-01,5.084848E-01,3... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 15.56 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 35.00 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YS_1554kW_9_31COP_Valve = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1554300, COP_nominal = 9.31, PLRMin = 0.10, PLRMinUnl = 0.10, PLRMax = 1.02, mEva_flow_nominal = 1000 * 0.0424, mCon_flow_nominal = 1000 * 0.07949, TEvaLvg_nominal = 273.15 + 5.56, TConEnt_nominal = 273.15 + 15.56, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 15.56, TConEntMax = 273.15 + 35.00, capFunT = {1.083027E+00,9.278069E-03,1.175024E-03,-1.395851E-02,9.301303E-05,6.968115E-05}, EIRFunT = {5.099117E-01,1.379553E-02,-2.069529E-04,2.846021E-02,7.189977E-04,-2.027317E-03}, EIRFunPLR = {1.720219E-01,5.084848E-01,3.212462E-01}, etaMotor = 1.0) "ElectricEIRChiller York YS 1554kW/9.31COP/Valve";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_York_YS_1758kW_5_84COP_Valve

ElectricEIRChiller York YS 1758kW/5.84COP/Valve

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller York YS 1758kW/5.84COP/Valve,  !- Name
        1758300,                 !- Reference Capacity {W}
        5.84,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        29.44,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.07571,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.09464,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller York YS 1758kW/5.84COP/Valve CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller York YS 1758kW/5.84COP/Valve EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller York YS 1758kW/5.84COP/Valve EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.20,                    !- Minimum Part Load Ratio
        1.04,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.20,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.04 | Maximum part load ratio
Real | PLRMinUnl | 0.20 | Minimum part unload ratio
Real | PLRMin | 0.20 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 29.44 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -1758300 | Reference capacity (negative number) [W]
Real | COP_nominal | 5.84 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.07571 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.09464 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {8.130185E-01,-1.425368E-02,... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {6.381264E-01,6.304193E-03,9... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {3.149879E-01,3.171267E-01,3... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 4.44 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 8.89 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 12.78 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 35.00 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_York_YS_1758kW_5_84COP_Valve = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -1758300, COP_nominal = 5.84, PLRMin = 0.20, PLRMinUnl = 0.20, PLRMax = 1.04, mEva_flow_nominal = 1000 * 0.07571, mCon_flow_nominal = 1000 * 0.09464, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 29.44, TEvaLvgMin = 273.15 + 4.44, TEvaLvgMax = 273.15 + 8.89, TConEntMin = 273.15 + 12.78, TConEntMax = 273.15 + 35.00, capFunT = {8.130185E-01,-1.425368E-02,-1.618007E-03,2.638417E-02,-9.154379E-04,1.696015E-03}, EIRFunT = {6.381264E-01,6.304193E-03,9.233511E-04,-4.552881E-03,8.256904E-04,-1.561533E-03}, EIRFunPLR = {3.149879E-01,3.171267E-01,3.709077E-01}, etaMotor = 1.0) "ElectricEIRChiller York YS 1758kW/5.84COP/Valve";

## Buildings.Fluid.Chillers.Data.ElectricEIR.ElectricEIRChiller_Trane_CGWD_207kW_3_99COP_None

ElectricEIRChiller Trane CGWD 207kW/3.99COP/None

### Information

Performance data for chiller model. This data corresponds to the following EnergyPlus model:

    Chiller:Electric:EIR,
        ElectricEIRChiller Trane CGWD 207kW/3.99COP/None,  !- Name
        207400,                  !- Reference Capacity {W}
        3.99,                    !- Reference COP {W/W}
        6.67,                    !- Reference Leaving Chilled Water Temperature {C}
        29.44,                   !- Reference Entering Condenser Fluid Temperature {C}
        0.00898,                 !- Reference Chilled Water Flow Rate {m3/s}
        0.01122,                 !- Reference Condenser Water Flow Rate {m3/s}
        ElectricEIRChiller Trane CGWD 207kW/3.99COP/None CAPFT,  !- Cooling Capacity Function of Temperature Curve Name
        ElectricEIRChiller Trane CGWD 207kW/3.99COP/None EIRFT,  !- Electric Input to Cooling Output Ratio Function of Temperature Curve Name
        ElectricEIRChiller Trane CGWD 207kW/3.99COP/None EIRFPLR,  !- Electric Input to Cooling Output Ratio Function of Part Load Ratio Curve Name
        0.25,                    !- Minimum Part Load Ratio
        1.01,                    !- Maximum Part Load Ratio
        1.0,                     !- Optimum Part Load Ratio
        0.25,                    !- Minimum Unloading Ratio
        Chilled Water Side Inlet Node,  !- Chilled Water Inlet Node Name
        Chilled Water Side Outlet Node,  !- Chilled Water Outlet Node Name
        Condenser Side Inlet Node,  !- Condenser Inlet Node Name
        Condenser Side Outlet Node,  !- Condenser Outlet Node Name
        WaterCooled,             !- Condenser Type
        ,                        !- Condenser Fan Power Ratio {W/W}
        1.0,                     !- Compressor Motor Efficiency
        2.0,                     !- Leaving Chilled Water Lower Temperature Limit {C}
        ConstantFlow,            !- Chiller Flow Mode
        0.0;                     !- Design Heat Recovery Water Flow Rate {m3/s}

Extends from Buildings.Fluid.Chillers.Data.ElectricEIR.Generic (Generic data record for chiller ElectricEIR).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | PLRMax | 1.01 | Maximum part load ratio
Real | PLRMinUnl | 0.25 | Minimum part unload ratio
Real | PLRMin | 0.25 | Minimum part load ratio
Real | etaMotor | 1.0 | Fraction of compressor motor heat entering refrigerant
Temperature | TConEnt_nominal | 273.15 + 29.44 | Temperature of fluid entering condenser at nominal condition [K]
Nominal condition
HeatFlowRate | QEva_flow_nominal | -207400 | Reference capacity (negative number) [W]
Real | COP_nominal | 3.99 | Reference coefficient of performance
MassFlowRate | mEva_flow_nominal | 1000*0.00898 | Nominal mass flow at evaporator [kg/s]
MassFlowRate | mCon_flow_nominal | 1000*0.01122 | Nominal mass flow at condenser [kg/s]
Temperature | TEvaLvg_nominal | 273.15 + 6.67 | Temperature of fluid leaving evaporator at nominal condition [K]
Performance curves
Real | capFunT[nCapFunT] | {9.441897E-01,3.371079E-02,9... | Biquadratic coefficients for capFunT
Real | EIRFunT[nEIRFunT] | {7.273870E-01,-1.189276E-02,... | Biquadratic coefficients for EIRFunT
Real | EIRFunPLR[nEIRFunPLR] | {4.146742E-02,6.543795E-01,3... | Coefficients for EIRFunPLR
Temperature | TEvaLvgMin | 273.15 + 5.56 | Minimum value for leaving evaporator temperature [K]
Temperature | TEvaLvgMax | 273.15 + 10.00 | Maximum value for leaving evaporator temperature [K]
Temperature | TConEntMin | 273.15 + 23.89 | Minimum value for entering condenser temperature [K]
Temperature | TConEntMax | 273.15 + 35.00 | Maximum value for entering condenser temperature [K]

### Modelica definition

record ElectricEIRChiller_Trane_CGWD_207kW_3_99COP_None = Buildings.Fluid.Chillers.Data.ElectricEIR.Generic ( QEva_flow_nominal = -207400, COP_nominal = 3.99, PLRMin = 0.25, PLRMinUnl = 0.25, PLRMax = 1.01, mEva_flow_nominal = 1000 * 0.00898, mCon_flow_nominal = 1000 * 0.01122, TEvaLvg_nominal = 273.15 + 6.67, TConEnt_nominal = 273.15 + 29.44, TEvaLvgMin = 273.15 + 5.56, TEvaLvgMax = 273.15 + 10.00, TConEntMin = 273.15 + 23.89, TConEntMax = 273.15 + 35.00, capFunT = {9.441897E-01,3.371079E-02,9.756685E-05,-3.220573E-03,-4.917369E-05,-1.775717E-04}, EIRFunT = {7.273870E-01,-1.189276E-02,5.411677E-04,1.879294E-03,4.734664E-04,-7.114850E-04}, EIRFunPLR = {4.146742E-02,6.543795E-01,3.044125E-01}, etaMotor = 1.0) "ElectricEIRChiller Trane CGWD 207kW/3.99COP/None";