Description: "Performance data for SingleSpeed DXCoils"

- Home > Modelica

## Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed

Performance data for SingleSpeed DXCoils

### Information

Package with performance data for DX coils.

Extends from Modelica.Icons.MaterialPropertiesPackage (Icon for package containing property classes).

### Package Content

Name | Description
--- | ---
Generic | Generic data record for SingleSpeed DXCoils
Lennox_KCA060S4 | Lennox KCA060S4
Lennox_SCA060H4B | Lennox SCA060H4B
Lennox_TCA060S2 | Lennox TCA060S2
Carrier_Centurion_50PG06 | Carrier Centurion 50PG06
Carrier_Centurion_50PG12 | Carrier Centurion 50PG12
Carrier_Centurion_50PG24 | Carrier Centurion 50PG24
Carrier_Comfort_50ES060 | Carrier Comfort 50ES060
Carrier_Weathermaster_50HJ006 | Carrier Weathermaster 50HJ006
Carrier_Weathermaster_50HJ012 | Carrier Weathermaster 50HJ012
Carrier_Weathermaster_50HJ024 | Carrier Weathermaster 50HJ024
Goodman_CPC060 | Goodman CPC060
York_Affinity_DNP060 | York Affinity DNP060
York_Affinity_DNZ060 | York Affinity DNZ060
York_Lattitude_SJ060 | York Lattitude SJ060
York_Lattitude_NM060 | York Lattitude NM060
York_Predator_ZF120 | York Predator ZF120
York_Sunline_ZR060 | York Sunline ZR060
York_Sunline_DR060 | York Sunline DR060
York_Sunline_ZF240 | York Sunline ZF240
York_Sunline_DJ240 | York Sunline DJ240

## Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic

Generic data record for SingleSpeed DXCoils

### Information

This record is used as a template for performance data for SingleSpeed DXCoils Buildings.Fluid.HeatExchangers.DXCoils.SingleSpeed.

Extends from Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.DXCoil (Performance record for a DX Cooling Coil with one or multiple stages).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Integer | nSta | 1 | Number of stages
Real | minSpeRat | 0.2 | Minimum speed ratio
Stage | sta[nSta] |  | Data record for coil performance at each stage
Minimum conditions
MassFlowRate | m_flow_small | 0.0001*sta[1].nomVal.m_flow_... | Small mass flow rate for regularization near zero flow [kg/s]

### Modelica definition

record Generic "Generic data record for SingleSpeed DXCoils" extends Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.DXCoil(final nSta=1); end Generic;

## Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Lennox_KCA060S4

Lennox KCA060S4

### Information

Performance data for DX single speed cooling coil model. This data corresponds to the following EnergyPlus model:

    Coil:Cooling:DX:SingleSpeed,
        Lennox KCA060S4,         !- Name
        CoolingCoilAvailSched,   !- Availability Schedule Name
        18101.22,                !- Rated Total Cooling Capacity {W}
        0.72,                    !- Rated Sensible Heat Ratio
        4.07,                    !- Rated COP
        0.944,                   !- Rated Air Flow Rate {m3/s}
        ,                        !- Rated Evaporator Fan Power Per Volume Flow Rate {W/(m3/s)}
        DXCoilAirInletNode,      !- Air Inlet Node Name
        DXCoilAirOutletNode,     !- Air Outlet Node Name
        Lennox KCA060S4 CapFT,   !- Total Cooling Capacity Function of Temperature Curve Name
        Lennox KCA060S4 CapFFF,  !- Total Cooling Capacity Function of Flow Fraction Curve Name
        Lennox KCA060S4 EIRFT,   !- Energy Input Ratio Function of Temperature Curve Name
        Lennox KCA060S4 EIRFFF,  !- Energy Input Ratio Function of Flow Fraction Curve Name
        Lennox KCA060S4 PLFFPLR; !- Part Load Fraction Correlation Curve Name

Extends from Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic (Generic data record for SingleSpeed DXCoils).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | minSpeRat | 0.2 | Minimum speed ratio
Stage | sta[nSta] | {Buildings.Fluid.HeatExchang... | Data record for coil performance at each stage
Minimum conditions
MassFlowRate | m_flow_small | 0.0001*sta[1].nomVal.m_flow_... | Small mass flow rate for regularization near zero flow [kg/s]

### Modelica definition

record Lennox_KCA060S4 = Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic(sta = { Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.Stage(spe=1800, nomVal= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.NominalValues( Q_flow_nominal= -18101.22, COP_nominal= 4.07, SHR_nominal= 0.72, m_flow_nominal= 1.2*0.944), perCur= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.PerformanceCurve( capFunT= {0.9600147,-0.0106038,0.0013516,0.0039357,-0.0000568,-0.0004915}, capFunFF= {0.7491909,0.3721683,-0.1213592}, EIRFunT= {0.2484029,0.0610633,-0.0017081,-0.0102658,0.0007028,-0.0004237}, EIRFunFF= {1.2094575,-0.3165036,0.1070461}, TConInMin= 273.15 + 18.33, TConInMax= 273.15 + 35, TEvaInMin= 273.15 + 17.22, TEvaInMax= 273.15 + 29.44, ffMin= 0.8, ffMax= 1.2))}) "Lennox KCA060S4";

## Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Lennox_SCA060H4B

Lennox SCA060H4B

### Information

Performance data for DX single speed cooling coil model. This data corresponds to the following EnergyPlus model:

    Coil:Cooling:DX:SingleSpeed,
        Lennox SCA060H4B,              !- Name
        CoolingCoilAvailSched,         !- Availability Schedule Name
        18452.7,                       !- Rated Total Cooling Capacity {W}
        0.73,                          !- Rated Sensible Heat Ratio
        4.48,                          !- Rated COP
        0.944,                         !- Rated Air Flow Rate {m3/s}
        ,                              !- Rated Evaporator Fan Power Per Volume Flow Rate {W/(m3/s)}
        DXCoilAirInletNode,            !- Air Inlet Node Name
        DXCoilAirOutletNode,           !- Air Outlet Node Name
        Lennox SCA060H4B CapFT,        !- Total Cooling Capacity Function of Temperature Curve Name
        Lennox SCA060H4B CapFFF,       !- Total Cooling Capacity Function of Flow Fraction Curve Name
        Lennox SCA060H4B EIRFT,        !- Energy Input Ratio Function of Temperature Curve Name
        Lennox SCA060H4B EIRFFF,       !- Energy Input Ratio Function of Flow Fraction Curve Name
        Lennox SCA060H4B PLFFPLR;      !- Part Load Fraction Correlation Curve Name

Extends from Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic (Generic data record for SingleSpeed DXCoils).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | minSpeRat | 0.2 | Minimum speed ratio
Stage | sta[nSta] | {Buildings.Fluid.HeatExchang... | Data record for coil performance at each stage
Minimum conditions
MassFlowRate | m_flow_small | 0.0001*sta[1].nomVal.m_flow_... | Small mass flow rate for regularization near zero flow [kg/s]

### Modelica definition

record Lennox_SCA060H4B = Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic(sta = { Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.Stage(spe=1800, nomVal= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.NominalValues( Q_flow_nominal= -18452.7, COP_nominal= 4.48, SHR_nominal= 0.73, m_flow_nominal= 1.2*0.944), perCur= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.PerformanceCurve( capFunT= {1.0671319,-0.0218036,0.0016875,0.0054500,-0.0000643,-0.0005786}, capFunFF= {0.8174603,0.2420635,-0.0595238}, EIRFunT= {0.4618717,0.0448432,-0.0012979,-0.0158459,0.0007680,-0.0003382}, EIRFunFF= {0.9342105,0.0986842,-0.0328947}, TConInMin= 273.15 + 29.44, TConInMax= 273.15 + 46.11, TEvaInMin= 273.15 + 17.22, TEvaInMax= 273.15 + 21.67, ffMin= 0.8, ffMax= 1.2))}) "Lennox SCA060H4B";

## Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Lennox_TCA060S2

Lennox TCA060S2

### Information

Performance data for DX single speed cooling coil model. This data corresponds to the following EnergyPlus model:

    Coil:Cooling:DX:SingleSpeed,
        Lennox TCA060S2,               !- Name
        CoolingCoilAvailSched,         !- Availability Schedule Name
        18452.7,                       !- Rated Total Cooling Capacity {W}
        0.75,                          !- Rated Sensible Heat Ratio
        4.07,                          !- Rated COP
        0.944,                         !- Rated Air Flow Rate {m3/s}
        ,                              !- Rated Evaporator Fan Power Per Volume Flow Rate {W/(m3/s)}
        DXCoilAirInletNode,            !- Air Inlet Node Name
        DXCoilAirOutletNode,           !- Air Outlet Node Name
        Lennox TCA060S2 CapFT,         !- Total Cooling Capacity Function of Temperature Curve Name
        Lennox TCA060S2 CapFFF,        !- Total Cooling Capacity Function of Flow Fraction Curve Name
        Lennox TCA060S2 EIRFT,         !- Energy Input Ratio Function of Temperature Curve Name
        Lennox TCA060S2 EIRFFF,        !- Energy Input Ratio Function of Flow Fraction Curve Name
        Lennox TCA060S2 PLFFPLR;       !- Part Load Fraction Correlation Curve Name

Extends from Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic (Generic data record for SingleSpeed DXCoils).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | minSpeRat | 0.2 | Minimum speed ratio
Stage | sta[nSta] | {Buildings.Fluid.HeatExchang... | Data record for coil performance at each stage
Minimum conditions
MassFlowRate | m_flow_small | 0.0001*sta[1].nomVal.m_flow_... | Small mass flow rate for regularization near zero flow [kg/s]

### Modelica definition

record Lennox_TCA060S2 = Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic(sta = { Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.Stage(spe=1800, nomVal= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.NominalValues( Q_flow_nominal= -18452.7, COP_nominal= 4.07, SHR_nominal= 0.75, m_flow_nominal= 1.2*0.944), perCur= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.PerformanceCurve( capFunT= {0.9274018,-0.0049893,0.0010446,0.0003500,-0.0000300,-0.0002957}, capFunFF= {0.7539683,0.3650794,-0.1190476}, EIRFunT= {0.5480534,0.0256216,-0.0006559,-0.0031147,0.0006074,-0.0006367}, EIRFunFF= {1.0120192,-0.0420673,0.0300481}, TConInMin= 273.15 + 29.44, TConInMax= 273.15 + 46.11, TEvaInMin= 273.15 + 17.22, TEvaInMax= 273.15 + 21.67, ffMin= 0.8, ffMax= 1.2))}) "Lennox TCA060S2";

## Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Carrier_Centurion_50PG06

Carrier Centurion 50PG06

### Information

Performance data for DX single speed cooling coil model. This data corresponds to the following EnergyPlus model:

    Coil:Cooling:DX:SingleSpeed,
        Carrier Centurion 50PG06,              !- Name
        CoolingCoilAvailSched,                 !- Availability Schedule Name
        18276.96,                              !- Rated Total Cooling Capacity {W}
        0.74,                                  !- Rated Sensible Heat Ratio
        4.15,                                  !- Rated COP
        0.944,                                 !- Rated Air Flow Rate {m3/s}
        ,                                      !- Rated Evaporator Fan Power Per Volume Flow Rate {W/(m3/s)}
        DXCoilAirInletNode,                    !- Air Inlet Node Name
        DXCoilAirOutletNode,                   !- Air Outlet Node Name
        Carrier Centurion 50PG06 CapFT,        !- Total Cooling Capacity Function of Temperature Curve Name
        Carrier Centurion 50PG06 CapFFF,       !- Total Cooling Capacity Function of Flow Fraction Curve Name
        Carrier Centurion 50PG06 EIRFT,        !- Energy Input Ratio Function of Temperature Curve Name
        Carrier Centurion 50PG06 EIRFFF,       !- Energy Input Ratio Function of Flow Fraction Curve Name
        Carrier Centurion 50PG06 PLFFPLR;      !- Part Load Fraction Correlation Curve Name

Extends from Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic (Generic data record for SingleSpeed DXCoils).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | minSpeRat | 0.2 | Minimum speed ratio
Stage | sta[nSta] | {Buildings.Fluid.HeatExchang... | Data record for coil performance at each stage
Minimum conditions
MassFlowRate | m_flow_small | 0.0001*sta[1].nomVal.m_flow_... | Small mass flow rate for regularization near zero flow [kg/s]

### Modelica definition

record Carrier_Centurion_50PG06 = Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic(sta = { Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.Stage(spe=1800, nomVal= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.NominalValues( Q_flow_nominal= -18276.96, COP_nominal= 4.15, SHR_nominal= 0.74, m_flow_nominal= 1.2*0.944), perCur= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.PerformanceCurve( capFunT= {0.9953455,-0.0118418,0.0012277,0.0030246,-0.0000702,-0.0003685}, capFunFF= {0.7705358,0.2848007,-0.0580891}, EIRFunT= {0.3802131,0.0199468,-0.0006682,0.0058933,0.0004646,-0.0004072}, EIRFunFF= {1.3439758,-0.5111244,0.1732549}, TConInMin= 273.15 + 15.56, TConInMax= 273.15 + 51.67, TEvaInMin= 273.15 + 12.22, TEvaInMax= 273.15 + 26.67, ffMin= 0.75, ffMax= 1.25))}) "Carrier Centurion 50PG06";

## Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Carrier_Centurion_50PG12

Carrier Centurion 50PG12

### Information

Performance data for DX single speed cooling coil model. This data corresponds to the following EnergyPlus model:

    Coil:Cooling:DX:SingleSpeed,
        Carrier Centurion 50PG12,               !- Name
        CoolingCoilAvailSched,                  !- Availability Schedule Name
        36788.24,                               !- Rated Total Cooling Capacity {W}
        0.76,                                   !- Rated Sensible Heat Ratio
        4.05,                                   !- Rated COP
        1.888,                                  !- Rated Air Flow Rate {m3/s}
        ,                                       !- Rated Evaporator Fan Power Per Volume Flow Rate {W/(m3/s)}
        DXCoilAirInletNode,                     !- Air Inlet Node Name
        DXCoilAirOutletNode,                    !- Air Outlet Node Name
        Carrier Centurion 50PG12 CapFT,         !- Total Cooling Capacity Function of Temperature Curve Name
        Carrier Centurion 50PG12 CapFFF,        !- Total Cooling Capacity Function of Flow Fraction Curve Name
        Carrier Centurion 50PG12 EIRFT,         !- Energy Input Ratio Function of Temperature Curve Name
        Carrier Centurion 50PG12 EIRFFF,        !- Energy Input Ratio Function of Flow Fraction Curve Name
        Carrier Centurion 50PG12 PLFFPLR;       !- Part Load Fraction Correlation Curve Name

Extends from Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic (Generic data record for SingleSpeed DXCoils).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | minSpeRat | 0.2 | Minimum speed ratio
Stage | sta[nSta] | {Buildings.Fluid.HeatExchang... | Data record for coil performance at each stage
Minimum conditions
MassFlowRate | m_flow_small | 0.0001*sta[1].nomVal.m_flow_... | Small mass flow rate for regularization near zero flow [kg/s]

### Modelica definition

record Carrier_Centurion_50PG12 = Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic(sta = { Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.Stage(spe=1800, nomVal= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.NominalValues( Q_flow_nominal= -36788.24, COP_nominal= 4.05, SHR_nominal= 0.76, m_flow_nominal= 1.2*1.888), perCur= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.PerformanceCurve( capFunT= {1.0013476,-0.0187754,0.0015312,0.0054931,-0.0000901,-0.0004408}, capFunFF= {0.6460191,0.5455414,-0.1910828}, EIRFunT= {0.3037085,0.0310288,-0.0009543,0.0053687,0.0004729,-0.0004469}, EIRFunFF= {1.3637624,-0.5775338,0.2130374}, TConInMin= 273.15 + 15.56, TConInMax= 273.15 + 51.67, TEvaInMin= 273.15 + 12.22, TEvaInMax= 273.15 + 26.67, ffMin= 0.75, ffMax= 1.25))}) "Carrier Centurion 50PG12";

## Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Carrier_Centurion_50PG24

Carrier Centurion 50PG24

### Information

Performance data for DX single speed cooling coil model. This data corresponds to the following EnergyPlus model:

    Coil:Cooling:DX:SingleSpeed,
        Carrier Centurion 50PG24,              !- Name
        CoolingCoilAvailSched,                 !- Availability Schedule Name
        73810.8,                               !- Rated Total Cooling Capacity {W}
        0.71,                                  !- Rated Sensible Heat Ratio
        3.95,                                  !- Rated COP
        3.776,                                 !- Rated Air Flow Rate {m3/s}
        ,                                      !- Rated Evaporator Fan Power Per Volume Flow Rate {W/(m3/s)}
        DXCoilAirInletNode,                    !- Air Inlet Node Name
        DXCoilAirOutletNode,                   !- Air Outlet Node Name
        Carrier Centurion 50PG24 CapFT,        !- Total Cooling Capacity Function of Temperature Curve Name
        Carrier Centurion 50PG24 CapFFF,       !- Total Cooling Capacity Function of Flow Fraction Curve Name
        Carrier Centurion 50PG24 EIRFT,        !- Energy Input Ratio Function of Temperature Curve Name
        Carrier Centurion 50PG24 EIRFFF,       !- Energy Input Ratio Function of Flow Fraction Curve Name
        Carrier Centurion 50PG24 PLFFPLR;      !- Part Load Fraction Correlation Curve Name

Extends from Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic (Generic data record for SingleSpeed DXCoils).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | minSpeRat | 0.2 | Minimum speed ratio
Stage | sta[nSta] | {Buildings.Fluid.HeatExchang... | Data record for coil performance at each stage
Minimum conditions
MassFlowRate | m_flow_small | 0.0001*sta[1].nomVal.m_flow_... | Small mass flow rate for regularization near zero flow [kg/s]

### Modelica definition

record Carrier_Centurion_50PG24 = Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic(sta = { Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.Stage(spe=1800, nomVal= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.NominalValues( Q_flow_nominal= -73810.8, COP_nominal= 3.95, SHR_nominal= 0.71, m_flow_nominal= 1.2*3.776), perCur= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.PerformanceCurve( capFunT= {0.5781158,0.0405917,0.0000113,-0.0095022,0.0000001,-0.0000573}, capFunFF= {0.8328798,0.2403628,-0.0725624}, EIRFunT= {0.5909553,-0.0496529,0.0016569,0.0397786,0.0003938,-0.0016575}, EIRFunFF= {1.0440554,-0.0701720,0.0258826}, TConInMin= 273.15 + 15.56, TConInMax= 273.15 + 51.67, TEvaInMin= 273.15 + 12.22, TEvaInMax= 273.15 + 26.67, ffMin= 0.75, ffMax= 1.25))}) "Carrier Centurion 50PG24";

## Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Carrier_Comfort_50ES060

Carrier Comfort 50ES060

### Information

Performance data for DX single speed cooling coil model. This data corresponds to the following EnergyPlus model:

    Coil:Cooling:DX:SingleSpeed,
        Carrier Comfort 50ES060,              !- Name
        CoolingCoilAvailSched,                !- Availability Schedule Name
        17500.95,                             !- Rated Total Cooling Capacity {W}
        0.78,                                 !- Rated Sensible Heat Ratio
        3.9,                                  !- Rated COP
        0.944,                                !- Rated Air Flow Rate {m3/s}
        ,                                     !- Rated Evaporator Fan Power Per Volume Flow Rate {W/(m3/s)}
        DXCoilAirInletNode,                   !- Air Inlet Node Name
        DXCoilAirOutletNode,                  !- Air Outlet Node Name
        Carrier Comfort 50ES060 CapFT,        !- Total Cooling Capacity Function of Temperature Curve Name
        Carrier Comfort 50ES060 CapFFF,       !- Total Cooling Capacity Function of Flow Fraction Curve Name
        Carrier Comfort 50ES060 EIRFT,        !- Energy Input Ratio Function of Temperature Curve Name
        Carrier Comfort 50ES060 EIRFFF,       !- Energy Input Ratio Function of Flow Fraction Curve Name
        Carrier Comfort 50ES060 PLFFPLR;      !- Part Load Fraction Correlation Curve Name

Extends from Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic (Generic data record for SingleSpeed DXCoils).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | minSpeRat | 0.2 | Minimum speed ratio
Stage | sta[nSta] | {Buildings.Fluid.HeatExchang... | Data record for coil performance at each stage
Minimum conditions
MassFlowRate | m_flow_small | 0.0001*sta[1].nomVal.m_flow_... | Small mass flow rate for regularization near zero flow [kg/s]

### Modelica definition

record Carrier_Comfort_50ES060 = Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic(sta = { Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.Stage(spe=1800, nomVal= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.NominalValues( Q_flow_nominal= -17500.95, COP_nominal= 3.9, SHR_nominal= 0.78, m_flow_nominal= 1.2*0.944), perCur= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.PerformanceCurve( capFunT= {1.6380187,-0.0747347,0.0029747,0.0015201,-0.0000519,-0.0004509}, capFunFF= {0.8185792,0.2831771,-0.1017563}, EIRFunT= {-0.2209648,0.1033303,-0.0030061,-0.0070657,0.0006322,-0.0002496}, EIRFunFF= {1.0380778,-0.2013868,0.1633090}, TConInMin= 273.15 + 23.89, TConInMax= 273.15 + 51.67, TEvaInMin= 273.15 + 13.89, TEvaInMax= 273.15 + 22.22, ffMin= 0.875, ffMax= 1.125))}) "Carrier Comfort 50ES060";

## Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Carrier_Weathermaster_50HJ006

Carrier Weathermaster 50HJ006

### Information

Performance data for DX single speed cooling coil model. This data corresponds to the following EnergyPlus model:

    Coil:Cooling:DX:SingleSpeed,
        Carrier Weathermaster 50HJ006,              !- Name
        CoolingCoilAvailSched,                      !- Availability Schedule Name
        18687,                                      !- Rated Total Cooling Capacity {W}
        0.73,                                       !- Rated Sensible Heat Ratio
        3.9,                                        !- Rated COP
        0.944,                                      !- Rated Air Flow Rate {m3/s}
        ,                                           !- Rated Evaporator Fan Power Per Volume Flow Rate {W/(m3/s)}
        DXCoilAirInletNode,                         !- Air Inlet Node Name
        DXCoilAirOutletNode,                        !- Air Outlet Node Name
        Carrier Weathermaster 50HJ006 CapFT,        !- Total Cooling Capacity Function of Temperature Curve Name
        Carrier Weathermaster 50HJ006 CapFFF,       !- Total Cooling Capacity Function of Flow Fraction Curve Name
        Carrier Weathermaster 50HJ006 EIRFT,        !- Energy Input Ratio Function of Temperature Curve Name
        Carrier Weathermaster 50HJ006 EIRFFF,       !- Energy Input Ratio Function of Flow Fraction Curve Name
        Carrier Weathermaster 50HJ006 PLFFPLR;      !- Part Load Fraction Correlation Curve Name

Extends from Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic (Generic data record for SingleSpeed DXCoils).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | minSpeRat | 0.2 | Minimum speed ratio
Stage | sta[nSta] | {Buildings.Fluid.HeatExchang... | Data record for coil performance at each stage
Minimum conditions
MassFlowRate | m_flow_small | 0.0001*sta[1].nomVal.m_flow_... | Small mass flow rate for regularization near zero flow [kg/s]

### Modelica definition

record Carrier_Weathermaster_50HJ006 = Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic(sta = { Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.Stage(spe=1800, nomVal= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.NominalValues( Q_flow_nominal= -18687, COP_nominal= 3.9, SHR_nominal= 0.73, m_flow_nominal= 1.2*0.944), perCur= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.PerformanceCurve( capFunT= {0.3116765,0.0622847,-0.0008633,-0.0066556,-0.0000462,0.0001349}, capFunFF= {0.6583072,0.5294956,-0.1869478}, EIRFunT= {1.0505234,-0.0653230,0.0021068,0.0235557,0.0004542,-0.0014092}, EIRFunFF= {1.3293472,-0.5218591,0.1918220}, TConInMin= 273.15 + 23.89, TConInMax= 273.15 + 51.67, TEvaInMin= 273.15 + 16.67, TEvaInMax= 273.15 + 22.22, ffMin= 0.75, ffMax= 1.25))}) "Carrier Weathermaster 50HJ006";

## Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Carrier_Weathermaster_50HJ012

Carrier Weathermaster 50HJ012

### Information

Performance data for DX single speed cooling coil model. This data corresponds to the following EnergyPlus model:

    Coil:Cooling:DX:SingleSpeed,
        Carrier Weathermaster 50HJ012,               !- Name
        CoolingCoilAvailSched,                       !- Availability Schedule Name
        36846.82,                                    !- Rated Total Cooling Capacity {W}
        0.73,                                        !- Rated Sensible Heat Ratio
        3.71,                                        !- Rated COP
        1.888,                                       !- Rated Air Flow Rate {m3/s}
        ,                                            !- Rated Evaporator Fan Power Per Volume Flow Rate {W/(m3/s)}
        DXCoilAirInletNode,                          !- Air Inlet Node Name
        DXCoilAirOutletNode,                         !- Air Outlet Node Name
        Carrier Weathermaster 50HJ012 CapFT,         !- Total Cooling Capacity Function of Temperature Curve Name
        Carrier Weathermaster 50HJ012 CapFFF,        !- Total Cooling Capacity Function of Flow Fraction Curve Name
        Carrier Weathermaster 50HJ012 EIRFT,         !- Energy Input Ratio Function of Temperature Curve Name
        Carrier Weathermaster 50HJ012 EIRFFF,        !- Energy Input Ratio Function of Flow Fraction Curve Name
        Carrier Weathermaster 50HJ012 PLFFPLR;       !- Part Load Fraction Correlation Curve Name

Extends from Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic (Generic data record for SingleSpeed DXCoils).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | minSpeRat | 0.2 | Minimum speed ratio
Stage | sta[nSta] | {Buildings.Fluid.HeatExchang... | Data record for coil performance at each stage
Minimum conditions
MassFlowRate | m_flow_small | 0.0001*sta[1].nomVal.m_flow_... | Small mass flow rate for regularization near zero flow [kg/s]

### Modelica definition

record Carrier_Weathermaster_50HJ012 = Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic(sta = { Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.Stage(spe=1800, nomVal= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.NominalValues( Q_flow_nominal= -36846.82, COP_nominal= 3.71, SHR_nominal= 0.73, m_flow_nominal= 1.2*1.888), perCur= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.PerformanceCurve( capFunT= {0.5878544,0.0247382,0.0001631,-0.0034960,-0.0000889,0.0001450}, capFunFF= {0.7232943,0.4292712,-0.1525863}, EIRFunT= {0.6445678,-0.0198276,0.0010284,0.0222812,0.0004996,-0.0015296}, EIRFunFF= {1.2158796,-0.3411366,0.1251095}, TConInMin= 273.15 + 23.89, TConInMax= 273.15 + 51.67, TEvaInMin= 273.15 + 16.67, TEvaInMax= 273.15 + 22.22, ffMin= 0.75, ffMax= 1.25))}) "Carrier Weathermaster 50HJ012";

## Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Carrier_Weathermaster_50HJ024

Carrier Weathermaster 50HJ024

### Information

Performance data for DX single speed cooling coil model. This data corresponds to the following EnergyPlus model:

    Coil:Cooling:DX:SingleSpeed,
        Carrier Weathermaster 50HJ024,              !- Name
        CoolingCoilAvailSched,                      !- Availability Schedule Name
        73517.9,                                    !- Rated Total Cooling Capacity {W}
        0.76,                                       !- Rated Sensible Heat Ratio
        3.73,                                       !- Rated COP
        3.776,                                      !- Rated Air Flow Rate {m3/s}
        ,                                           !- Rated Evaporator Fan Power Per Volume Flow Rate {W/(m3/s)}
        DXCoilAirInletNode,                         !- Air Inlet Node Name
        DXCoilAirOutletNode,                        !- Air Outlet Node Name
        Carrier Weathermaster 50HJ024 CapFT,        !- Total Cooling Capacity Function of Temperature Curve Name
        Carrier Weathermaster 50HJ024 CapFFF,       !- Total Cooling Capacity Function of Flow Fraction Curve Name
        Carrier Weathermaster 50HJ024 EIRFT,        !- Energy Input Ratio Function of Temperature Curve Name
        Carrier Weathermaster 50HJ024 EIRFFF,       !- Energy Input Ratio Function of Flow Fraction Curve Name
        Carrier Weathermaster 50HJ024 PLFFPLR;      !- Part Load Fraction Correlation Curve Name

Extends from Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic (Generic data record for SingleSpeed DXCoils).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | minSpeRat | 0.2 | Minimum speed ratio
Stage | sta[nSta] | {Buildings.Fluid.HeatExchang... | Data record for coil performance at each stage
Minimum conditions
MassFlowRate | m_flow_small | 0.0001*sta[1].nomVal.m_flow_... | Small mass flow rate for regularization near zero flow [kg/s]

### Modelica definition

record Carrier_Weathermaster_50HJ024 = Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic(sta = { Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.Stage(spe=1800, nomVal= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.NominalValues( Q_flow_nominal= -73517.9, COP_nominal= 3.73, SHR_nominal= 0.76, m_flow_nominal= 1.2*3.776), perCur= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.PerformanceCurve( capFunT= {1.1345120,-0.0239764,0.0012836,0.0023642,-0.0000802,-0.0001980}, capFunFF= {0.7578828,0.3524189,-0.1092772}, EIRFunT= {0.3439210,0.0215041,-0.0006539,0.0073217,0.0003160,-0.0002297}, EIRFunFF= {1.2167653,-0.3411749,0.1233570}, TConInMin= 273.15 + 15.56, TConInMax= 273.15 + 51.67, TEvaInMin= 273.15 + 12.22, TEvaInMax= 273.15 + 26.67, ffMin= 0.75, ffMax= 1.25))}) "Carrier Weathermaster 50HJ024";

## Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Goodman_CPC060

Goodman CPC060

### Information

Performance data for DX single speed cooling coil model. This data corresponds to the following EnergyPlus model:

    Coil:Cooling:DX:SingleSpeed,
        Goodman CPC060,              !- Name
        CoolingCoilAvailSched,       !- Availability Schedule Name
        17427.55,                    !- Rated Total Cooling Capacity {W}
        0.72,                        !- Rated Sensible Heat Ratio
        3.95,                        !- Rated COP
        0.944,                       !- Rated Air Flow Rate {m3/s}
        ,                            !- Rated Evaporator Fan Power Per Volume Flow Rate {W/(m3/s)}
        DXCoilAirInletNode,          !- Air Inlet Node Name
        DXCoilAirOutletNode,         !- Air Outlet Node Name
        Goodman CPC060 CapFT,        !- Total Cooling Capacity Function of Temperature Curve Name
        Goodman CPC060 CapFFF,       !- Total Cooling Capacity Function of Flow Fraction Curve Name
        Goodman CPC060 EIRFT,        !- Energy Input Ratio Function of Temperature Curve Name
        Goodman CPC060 EIRFFF,       !- Energy Input Ratio Function of Flow Fraction Curve Name
        Goodman CPC060 PLFFPLR;      !- Part Load Fraction Correlation Curve Name

Extends from Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic (Generic data record for SingleSpeed DXCoils).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | minSpeRat | 0.2 | Minimum speed ratio
Stage | sta[nSta] | {Buildings.Fluid.HeatExchang... | Data record for coil performance at each stage
Minimum conditions
MassFlowRate | m_flow_small | 0.0001*sta[1].nomVal.m_flow_... | Small mass flow rate for regularization near zero flow [kg/s]

### Modelica definition

record Goodman_CPC060 = Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic(sta = { Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.Stage(spe=1800, nomVal= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.NominalValues( Q_flow_nominal= -17427.55, COP_nominal= 3.95, SHR_nominal= 0.72, m_flow_nominal= 1.2*0.944), perCur= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.PerformanceCurve( capFunT= {1.3045870,-0.0618386,0.0024674,0.0081572,-0.0001826,-0.0001610}, capFunFF= {-0.9361345,3.4420168,-1.5058824}, EIRFunT= {0.1618862,0.0531671,-0.0015621,0.0077612,0.0001864,-0.0001388}, EIRFunFF= {2.2905751,-2.2915498,1.0009747}, TConInMin= 273.15 + 18.33, TConInMax= 273.15 + 46.11, TEvaInMin= 273.15 + 15, TEvaInMax= 273.15 + 21.67, ffMin= 0.875, ffMax= 1.125))}) "Goodman CPC060";

## Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.York_Affinity_DNP060

York Affinity DNP060

### Information

Performance data for DX single speed cooling coil model. This data corresponds to the following EnergyPlus model:

    Coil:Cooling:DX:SingleSpeed,
        York Affinity DNP060,               !- Name
        CoolingCoilAvailSched,              !- Availability Schedule Name
        17200,                              !- Rated Total Cooling Capacity {W}
        0.71,                               !- Rated Sensible Heat Ratio
        3.88,                               !- Rated COP
        0.8496,                             !- Rated Air Flow Rate {m3/s}
        ,                                   !- Rated Evaporator Fan Power Per Volume Flow Rate {W/(m3/s)}
        DXCoilAirInletNode,                 !- Air Inlet Node Name
        DXCoilAirOutletNode,                !- Air Outlet Node Name
        York Affinity DNP060 CapFT,         !- Total Cooling Capacity Function of Temperature Curve Name
        York Affinity DNP060 CapFFF,        !- Total Cooling Capacity Function of Flow Fraction Curve Name
        York Affinity DNP060 EIRFT,         !- Energy Input Ratio Function of Temperature Curve Name
        York Affinity DNP060 EIRFFF,        !- Energy Input Ratio Function of Flow Fraction Curve Name
        York Affinity DNP060 PLFFPLR;       !- Part Load Fraction Correlation Curve Name

Extends from Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic (Generic data record for SingleSpeed DXCoils).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | minSpeRat | 0.2 | Minimum speed ratio
Stage | sta[nSta] | {Buildings.Fluid.HeatExchang... | Data record for coil performance at each stage
Minimum conditions
MassFlowRate | m_flow_small | 0.0001*sta[1].nomVal.m_flow_... | Small mass flow rate for regularization near zero flow [kg/s]

### Modelica definition

record York_Affinity_DNP060 = Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic(sta = { Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.Stage(spe=1800, nomVal= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.NominalValues( Q_flow_nominal= -17200, COP_nominal= 3.88, SHR_nominal= 0.71, m_flow_nominal= 1.2*0.8496), perCur= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.PerformanceCurve( capFunT= {0.9829911,-0.0197231,0.0016341,0.0058106,-0.0000309,-0.0005776}, capFunFF= {0.9268752,0.0902018,-0.0175149}, EIRFunT= {0.2246908,0.0390385,-0.0010832,0.0080036,0.0003449,-0.0004327}, EIRFunFF= {2.0004106,-2.4070885,1.3922562}, TConInMin= 273.15 + 23.89, TConInMax= 273.15 + 51.67, TEvaInMin= 273.15 + 13.89, TEvaInMax= 273.15 + 25, ffMin= 0.833, ffMax= 1.167))}) "York Affinity DNP060";

## Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.York_Affinity_DNZ060

York Affinity DNZ060

### Information

Performance data for DX single speed cooling coil model. This data corresponds to the following EnergyPlus model:

    Coil:Cooling:DX:SingleSpeed,
        York Affinity DNZ060,               !- Name
        CoolingCoilAvailSched,              !- Availability Schedule Name
        17395.3,                            !- Rated Total Cooling Capacity {W}
        0.68,                               !- Rated Sensible Heat Ratio
        4.24,                               !- Rated COP
        0.826,                              !- Rated Air Flow Rate {m3/s}
        ,                                   !- Rated Evaporator Fan Power Per Volume Flow Rate {W/(m3/s)}
        DXCoilAirInletNode,                 !- Air Inlet Node Name
        DXCoilAirOutletNode,                !- Air Outlet Node Name
        York Affinity DNZ060 CapFT,         !- Total Cooling Capacity Function of Temperature Curve Name
        York Affinity DNZ060 CapFFF,        !- Total Cooling Capacity Function of Flow Fraction Curve Name
        York Affinity DNZ060 EIRFT,         !- Energy Input Ratio Function of Temperature Curve Name
        York Affinity DNZ060 EIRFFF,        !- Energy Input Ratio Function of Flow Fraction Curve Name
        York Affinity DNZ060 PLFFPLR;       !- Part Load Fraction Correlation Curve Name

Extends from Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic (Generic data record for SingleSpeed DXCoils).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | minSpeRat | 0.2 | Minimum speed ratio
Stage | sta[nSta] | {Buildings.Fluid.HeatExchang... | Data record for coil performance at each stage
Minimum conditions
MassFlowRate | m_flow_small | 0.0001*sta[1].nomVal.m_flow_... | Small mass flow rate for regularization near zero flow [kg/s]

### Modelica definition

record York_Affinity_DNZ060 = Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic(sta = { Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.Stage(spe=1800, nomVal= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.NominalValues( Q_flow_nominal= -17395.3, COP_nominal= 4.24, SHR_nominal= 0.68, m_flow_nominal= 1.2*0.826), perCur= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.PerformanceCurve( capFunT= {1.2343140,-0.0398816,0.0019354,0.0062114,-0.0001247,-0.0003619}, capFunFF= {1.2527302,-0.7182445,0.4623738}, EIRFunT= {-0.1272387,0.0848124,-0.0021062,-0.0085792,0.0007783,-0.0005585}, EIRFunFF= {0.6529892,0.8193151,-0.4617716}, TConInMin= 273.15 + 23.89, TConInMax= 273.15 + 51.67, TEvaInMin= 273.15 + 13.89, TEvaInMax= 273.15 + 25, ffMin= 0.714, ffMax= 1.2))}) "York Affinity DNZ060";

## Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.York_Lattitude_SJ060

York Lattitude SJ060

### Information

Performance data for DX single speed cooling coil model. This data corresponds to the following EnergyPlus model:

    Coil:Cooling:DX:SingleSpeed,
        York Lattitude SJ060,              !- Name
        CoolingCoilAvailSched,             !- Availability Schedule Name
        17427.55,                          !- Rated Total Cooling Capacity {W}
        0.70,                              !- Rated Sensible Heat Ratio
        4.25,                              !- Rated COP
        0.944,                             !- Rated Air Flow Rate {m3/s}
        ,                                  !- Rated Evaporator Fan Power Per Volume Flow Rate {W/(m3/s)}
        DXCoilAirInletNode,                !- Air Inlet Node Name
        DXCoilAirOutletNode,               !- Air Outlet Node Name
        York Lattitude SJ060 CapFT,        !- Total Cooling Capacity Function of Temperature Curve Name
        York Lattitude SJ060 CapFFF,       !- Total Cooling Capacity Function of Flow Fraction Curve Name
        York Lattitude SJ060 EIRFT,        !- Energy Input Ratio Function of Temperature Curve Name
        York Lattitude SJ060 EIRFFF,       !- Energy Input Ratio Function of Flow Fraction Curve Name
        York Lattitude SJ060 PLFFPLR;      !- Part Load Fraction Correlation Curve Name

Extends from Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic (Generic data record for SingleSpeed DXCoils).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | minSpeRat | 0.2 | Minimum speed ratio
Stage | sta[nSta] | {Buildings.Fluid.HeatExchang... | Data record for coil performance at each stage
Minimum conditions
MassFlowRate | m_flow_small | 0.0001*sta[1].nomVal.m_flow_... | Small mass flow rate for regularization near zero flow [kg/s]

### Modelica definition

record York_Lattitude_SJ060 = Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic(sta = { Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.Stage(spe=1800, nomVal= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.NominalValues( Q_flow_nominal= -17427.55, COP_nominal= 4.25, SHR_nominal= 0.70, m_flow_nominal= 1.2*0.944), perCur= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.PerformanceCurve( capFunT= {0.8277321,-0.0496772,0.0021600,0.0350767,-0.0004860,-0.0004331}, capFunFF= {1.3022329,-0.7346939,0.4379352}, EIRFunT= {0.1643011,0.0818978,-0.0021640,-0.0183702,0.0007849,-0.0003855}, EIRFunFF= {0.7757255,0.5279901,-0.3030465}, TConInMin= 273.15 + 23.89, TConInMax= 273.15 + 51.67, TEvaInMin= 273.15 + 13.89, TEvaInMax= 273.15 + 22.22, ffMin= 0.75, ffMax= 1.25))}) "York Lattitude SJ060";

## Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.York_Lattitude_NM060

York Lattitude NM060

### Information

Performance data for DX single speed cooling coil model. This data corresponds to the following EnergyPlus model:

    Coil:Cooling:DX:SingleSpeed,
        York Lattitude NM060,               !- Name
        CoolingCoilAvailSched,              !- Availability Schedule Name
        17100,                              !- Rated Total Cooling Capacity {W}
        0.70,                               !- Rated Sensible Heat Ratio
        3.85,                               !- Rated COP
        0.8024,                             !- Rated Air Flow Rate {m3/s}
        ,                                   !- Rated Evaporator Fan Power Per Volume Flow Rate {W/(m3/s)}
        DXCoilAirInletNode,                 !- Air Inlet Node Name
        DXCoilAirOutletNode,                !- Air Outlet Node Name
        York Lattitude NM060 CapFT,         !- Total Cooling Capacity Function of Temperature Curve Name
        York Lattitude NM060 CapFFF,        !- Total Cooling Capacity Function of Flow Fraction Curve Name
        York Lattitude NM060 EIRFT,         !- Energy Input Ratio Function of Temperature Curve Name
        York Lattitude NM060 EIRFFF,        !- Energy Input Ratio Function of Flow Fraction Curve Name
        York Lattitude NM060 PLFFPLR;       !- Part Load Fraction Correlation Curve Name

Extends from Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic (Generic data record for SingleSpeed DXCoils).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | minSpeRat | 0.2 | Minimum speed ratio
Stage | sta[nSta] | {Buildings.Fluid.HeatExchang... | Data record for coil performance at each stage
Minimum conditions
MassFlowRate | m_flow_small | 0.0001*sta[1].nomVal.m_flow_... | Small mass flow rate for regularization near zero flow [kg/s]

### Modelica definition

record York_Lattitude_NM060 = Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic(sta = { Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.Stage(spe=1800, nomVal= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.NominalValues( Q_flow_nominal= -17100, COP_nominal= 3.85, SHR_nominal= 0.70, m_flow_nominal= 1.2*0.8024), perCur= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.PerformanceCurve( capFunT= {1.1028912,-0.0119627,0.0014640,-0.0041312,-0.0000388,-0.0003520}, capFunFF= {0.7060647,0.3967112,-0.1059134}, EIRFunT= {0.0281200,0.0456536,-0.0006039,0.0145030,0.0006477,-0.0014811}, EIRFunFF= {0.4662994,0.2484568,-0.0381443}, TConInMin= 273.15 + 23.89, TConInMax= 273.15 + 51.67, TEvaInMin= 273.15 + 13.89, TEvaInMax= 273.15 + 25, ffMin= 0.824, ffMax= 1.47))}) "York Lattitude NM060";

## Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.York_Predator_ZF120

York Predator ZF120

### Information

Performance data for DX single speed cooling coil model. This data corresponds to the following EnergyPlus model:

    Coil:Cooling:DX:SingleSpeed,
        York Predator ZF120,               !- Name
        CoolingCoilAvailSched,             !- Availability Schedule Name
        36905.4,                           !- Rated Total Cooling Capacity {W}
        0.734,                             !- Rated Sensible Heat Ratio
        4.06,                              !- Rated COP
        1.888,                             !- Rated Air Flow Rate {m3/s}
        ,                                  !- Rated Evaporator Fan Power Per Volume Flow Rate {W/(m3/s)}
        DXCoilAirInletNode,                !- Air Inlet Node Name
        DXCoilAirOutletNode,               !- Air Outlet Node Name
        York Predator ZF120 CapFT,         !- Total Cooling Capacity Function of Temperature Curve Name
        York Predator ZF120 CapFFF,        !- Total Cooling Capacity Function of Flow Fraction Curve Name
        York Predator ZF120 EIRFT,         !- Energy Input Ratio Function of Temperature Curve Name
        York Predator ZF120 EIRFFF,        !- Energy Input Ratio Function of Flow Fraction Curve Name
        York Predator ZF120 PLFFPLR;       !- Part Load Fraction Correlation Curve Name

Extends from Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic (Generic data record for SingleSpeed DXCoils).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | minSpeRat | 0.2 | Minimum speed ratio
Stage | sta[nSta] | {Buildings.Fluid.HeatExchang... | Data record for coil performance at each stage
Minimum conditions
MassFlowRate | m_flow_small | 0.0001*sta[1].nomVal.m_flow_... | Small mass flow rate for regularization near zero flow [kg/s]

### Modelica definition

record York_Predator_ZF120 = Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic(sta = { Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.Stage(spe=1800, nomVal= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.NominalValues( Q_flow_nominal= -36905.4, COP_nominal= 4.06, SHR_nominal= 0.734, m_flow_nominal= 1.2*1.888), perCur= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.PerformanceCurve( capFunT= {1.2083456,-0.0287633,0.0022322,0.0019731,-0.0000541,-0.0007392}, capFunFF= {0.6735828,0.4697959,-0.1469388}, EIRFunT= {0.4822073,0.0401530,-0.0015820,-0.0116025,0.0006758,-0.0001198}, EIRFunFF= {1.3074459,-0.4421330,0.1377204}, TConInMin= 273.15 + 23.89, TConInMax= 273.15 + 51.67, TEvaInMin= 273.15 + 13.89, TEvaInMax= 273.15 + 25, ffMin= 0.625, ffMax= 1.25))}) "York Predator ZF120";

## Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.York_Sunline_ZR060

York Sunline ZR060

### Information

Performance data for DX single speed cooling coil model. This data corresponds to the following EnergyPlus model:

    Coil:Cooling:DX:SingleSpeed,
        York Sunline ZR060,              !- Name
        CoolingCoilAvailSched,           !- Availability Schedule Name
        18687,                           !- Rated Total Cooling Capacity {W}
        0.685,                           !- Rated Sensible Heat Ratio
        3.98,                            !- Rated COP
        0.944,                           !- Rated Air Flow Rate {m3/s}
        ,                                !- Rated Evaporator Fan Power Per Volume Flow Rate {W/(m3/s)}
        DXCoilAirInletNode,              !- Air Inlet Node Name
        DXCoilAirOutletNode,             !- Air Outlet Node Name
        York Sunline ZR060 CapFT,        !- Total Cooling Capacity Function of Temperature Curve Name
        York Sunline ZR060 CapFFF,       !- Total Cooling Capacity Function of Flow Fraction Curve Name
        York Sunline ZR060 EIRFT,        !- Energy Input Ratio Function of Temperature Curve Name
        York Sunline ZR060 EIRFFF,       !- Energy Input Ratio Function of Flow Fraction Curve Name
        York Sunline ZR060 PLFFPLR;      !- Part Load Fraction Correlation Curve Name

Extends from Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic (Generic data record for SingleSpeed DXCoils).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | minSpeRat | 0.2 | Minimum speed ratio
Stage | sta[nSta] | {Buildings.Fluid.HeatExchang... | Data record for coil performance at each stage
Minimum conditions
MassFlowRate | m_flow_small | 0.0001*sta[1].nomVal.m_flow_... | Small mass flow rate for regularization near zero flow [kg/s]

### Modelica definition

record York_Sunline_ZR060 = Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic(sta = { Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.Stage(spe=1800, nomVal= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.NominalValues( Q_flow_nominal= -18687, COP_nominal= 3.98, SHR_nominal= 0.685, m_flow_nominal= 1.2*0.944), perCur= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.PerformanceCurve( capFunT= {1.1491510,-0.0161007,0.0015936,-0.0027657,-0.0000236,-0.0004692}, capFunFF= {0.3148231,1.0463502,-0.3708016}, EIRFunT= {0.1210878,0.0560928,-0.0012307,0.0092825,0.0005999,-0.0010492}, EIRFunFF= {1.9711221,-1.6315991,0.6688369}, TConInMin= 273.15 + 23.89, TConInMax= 273.15 + 51.67, TEvaInMin= 273.15 + 13.89, TEvaInMax= 273.15 + 25, ffMin= 0.625, ffMax= 1.25))}) "York Sunline ZR060";

## Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.York_Sunline_DR060

York Sunline DR060

### Information

Performance data for DX single speed cooling coil model. This data corresponds to the following EnergyPlus model:

    Coil:Cooling:DX:SingleSpeed,
        York Sunline DR060,               !- Name
        CoolingCoilAvailSched,            !- Availability Schedule Name
        17398.26,                         !- Rated Total Cooling Capacity {W}
        0.69,                             !- Rated Sensible Heat Ratio
        4.05,                             !- Rated COP
        0.944,                            !- Rated Air Flow Rate {m3/s}
        ,                                 !- Rated Evaporator Fan Power Per Volume Flow Rate {W/(m3/s)}
        DXCoilAirInletNode,               !- Air Inlet Node Name
        DXCoilAirOutletNode,              !- Air Outlet Node Name
        York Sunline DR060 CapFT,         !- Total Cooling Capacity Function of Temperature Curve Name
        York Sunline DR060 CapFFF,        !- Total Cooling Capacity Function of Flow Fraction Curve Name
        York Sunline DR060 EIRFT,         !- Energy Input Ratio Function of Temperature Curve Name
        York Sunline DR060 EIRFFF,        !- Energy Input Ratio Function of Flow Fraction Curve Name
        York Sunline DR060 PLFFPLR;       !- Part Load Fraction Correlation Curve Name

Extends from Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic (Generic data record for SingleSpeed DXCoils).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | minSpeRat | 0.2 | Minimum speed ratio
Stage | sta[nSta] | {Buildings.Fluid.HeatExchang... | Data record for coil performance at each stage
Minimum conditions
MassFlowRate | m_flow_small | 0.0001*sta[1].nomVal.m_flow_... | Small mass flow rate for regularization near zero flow [kg/s]

### Modelica definition

record York_Sunline_DR060 = Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic(sta = { Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.Stage(spe=1800, nomVal= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.NominalValues( Q_flow_nominal= -17398.26, COP_nominal= 4.05, SHR_nominal= 0.69, m_flow_nominal= 1.2*0.944), perCur= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.PerformanceCurve( capFunT= {1.4767927,-0.0614116,0.0027182,-0.0010838,-0.0000353,-0.0003531}, capFunFF= {0.9156325,0.0076960,0.0769601}, EIRFunT= {-0.2918107,0.0950527,-0.0026508,0.0070978,0.0005090,-0.0006143}, EIRFunFF= {0.9336732,0.2228647,-0.1628839}, TConInMin= 273.15 + 23.89, TConInMax= 273.15 + 51.67, TEvaInMin= 273.15 + 13.89, TEvaInMax= 273.15 + 22.22, ffMin= 0.75, ffMax= 1.25))}) "York Sunline DR060";

## Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.York_Sunline_ZF240

York Sunline ZF240

### Information

Performance data for DX single speed cooling coil model. This data corresponds to the following EnergyPlus model:

    Coil:Cooling:DX:SingleSpeed,
        York Sunline ZF240,               !- Name
        CoolingCoilAvailSched,            !- Availability Schedule Name
        81807,                            !- Rated Total Cooling Capacity {W}
        0.70,                             !- Rated Sensible Heat Ratio
        3.59,                             !- Rated COP
        3.776,                            !- Rated Air Flow Rate {m3/s}
        ,                                 !- Rated Evaporator Fan Power Per Volume Flow Rate {W/(m3/s)}
        DXCoilAirInletNode,               !- Air Inlet Node Name
        DXCoilAirOutletNode,              !- Air Outlet Node Name
        York Sunline ZF240 CapFT,         !- Total Cooling Capacity Function of Temperature Curve Name
        York Sunline ZF240 CapFFF,        !- Total Cooling Capacity Function of Flow Fraction Curve Name
        York Sunline ZF240 EIRFT,         !- Energy Input Ratio Function of Temperature Curve Name
        York Sunline ZF240 EIRFFF,        !- Energy Input Ratio Function of Flow Fraction Curve Name
        York Sunline ZF240 PLFFPLR;       !- Part Load Fraction Correlation Curve Name

Extends from Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic (Generic data record for SingleSpeed DXCoils).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | minSpeRat | 0.2 | Minimum speed ratio
Stage | sta[nSta] | {Buildings.Fluid.HeatExchang... | Data record for coil performance at each stage
Minimum conditions
MassFlowRate | m_flow_small | 0.0001*sta[1].nomVal.m_flow_... | Small mass flow rate for regularization near zero flow [kg/s]

### Modelica definition

record York_Sunline_ZF240 = Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic(sta = { Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.Stage(spe=1800, nomVal= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.NominalValues( Q_flow_nominal= -81807, COP_nominal= 3.59, SHR_nominal= 0.70, m_flow_nominal= 1.2*3.776), perCur= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.PerformanceCurve( capFunT= {1.0477109,-0.0126686,0.0012838,0.0012381,-0.0000551,-0.0003875}, capFunFF= {0.6042146,0.6557209,-0.2667894}, EIRFunT= {0.4544209,0.0213827,-0.0007051,0.0028662,0.0004214,-0.0003177}, EIRFunFF= {1.4410769,-0.7566253,0.3239453}, TConInMin= 273.15 + 23.89, TConInMax= 273.15 + 51.67, TEvaInMin= 273.15 + 13.89, TEvaInMax= 273.15 + 25, ffMin= 0.625, ffMax= 1.25))}) "York Sunline ZF240";

## Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.York_Sunline_DJ240

York Sunline DJ240

### Information

Performance data for DX single speed cooling coil model. This data corresponds to the following EnergyPlus model:

    Coil:Cooling:DX:SingleSpeed,
        York Sunline DJ240,               !- Name
        CoolingCoilAvailSched,            !- Availability Schedule Name
        73518,                            !- Rated Total Cooling Capacity {W}
        0.75,                             !- Rated Sensible Heat Ratio
        4.096,                            !- Rated COP
        3.776,                            !- Rated Air Flow Rate {m3/s}
        ,                                 !- Rated Evaporator Fan Power Per Volume Flow Rate {W/(m3/s)}
        DXCoilAirInletNode,               !- Air Inlet Node Name
        DXCoilAirOutletNode,              !- Air Outlet Node Name
        York Sunline DJ240 CapFT,         !- Total Cooling Capacity Function of Temperature Curve Name
        York Sunline DJ240 CapFFF,        !- Total Cooling Capacity Function of Flow Fraction Curve Name
        York Sunline DJ240 EIRFT,         !- Energy Input Ratio Function of Temperature Curve Name
        York Sunline DJ240 EIRFFF,        !- Energy Input Ratio Function of Flow Fraction Curve Name
        York Sunline DJ240 PLFFPLR;       !- Part Load Fraction Correlation Curve Name

Extends from Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic (Generic data record for SingleSpeed DXCoils).

### Parameters

Type | Name | Default | Description
--- | --- | --- | ---
Real | minSpeRat | 0.2 | Minimum speed ratio
Stage | sta[nSta] | {Buildings.Fluid.HeatExchang... | Data record for coil performance at each stage
Minimum conditions
MassFlowRate | m_flow_small | 0.0001*sta[1].nomVal.m_flow_... | Small mass flow rate for regularization near zero flow [kg/s]

### Modelica definition

record York_Sunline_DJ240 = Buildings.Fluid.HeatExchangers.DXCoils.Data.SingleSpeed.Generic(sta = { Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.Stage(spe=1800, nomVal= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.NominalValues( Q_flow_nominal= -73518, COP_nominal= 4.096, SHR_nominal= 0.75, m_flow_nominal= 1.2*3.776), perCur= Buildings.Fluid.HeatExchangers.DXCoils.Data.Generic.BaseClasses.PerformanceCurve( capFunT= {1.3804089,-0.0801861,0.0033588,0.0118882,-0.0001339,-0.0005357}, capFunFF= {0.7894654,0.1996615,0.0111454}, EIRFunT= {-0.1635113,0.1222397,-0.0037107,-0.0070372,0.0005052,-0.0002069}, EIRFunFF= {1.5272381,-0.9652850,0.4418485}, TConInMin= 273.15 + 23.89, TConInMax= 273.15 + 51.67, TEvaInMin= 273.15 + 13.89, TEvaInMax= 273.15 + 22.22, ffMin= 0.75, ffMax= 1.175))}) "York Sunline DJ240";